7 
KN 
SS 
Q 
— 
. 
SS 
& 


cand 
Steel Cabinets 
for Light and Power 


0 
oe 
S 
- 
~ 
< 
S 


a4 


RAL, f 

AN 
\ nt » 
AANA fin Con 


a s 
Ae 
ni 


BENJAMIN-STARRET] 


Lighting Panelboards 
and Cabinets 


Metering Panelboards 
and Cabinets 


Power Panelboards 
and Cabinets 


Switchboards 


Catalog S-5 


Copyright, 1928 
BENJAMIN ELECTRIC MFG. CO., CHICAGO 


BENJAMIN ELECTRIC MFG. CO. 


247 W. 17th Street 120-128 So. Sangamon Street 448 Bryant Street 
NEW YORK CHICAGO SAN FRANCISCO 


Benjamin-Starrett Panelboards and Cabinets are Fully Protected 
by United States and Foreign Patents. Other Patents Pending. 


a a a 
Printed in U.S. A. 


nee _ BENJAMIN -STARRETT 


Foreword 


HE Benjamin-Starrett Organization, long recognized as a pioneer 
in the use of moulded composition base sectional unit construc- 
tion, continues its leadership with this new and improved design. 


Listed and illustrated in this catalog are types of panelboards suited 
to meet all the diversified requirements of electric lighting distribution. 


Special power and lighting distribution panelboards, cabinets and 
switchboards are also shown. The Benjamin-Starrett organization 
stands ready with its capable and experienced engineering staff to aid 
in the solution of your special requirements. 


All the panelboard material listed in this catalog is constructed in 
accordance with the rules and specifications of the National Board of 
Fire Underwriters’ and each device bears the Inspection Label of the 
Underwriters’ Laboratories. 


For convenient reference, this catalog has been divided into the 
eight sections enumerated below. 


Index 


Section Il —Type “G’? and Little Sentry Lighting Panelboards. 


Section II —One Fuse Lighting Panelboards: Safety, Protective, 
and Open Front Types. 


Section III —Two Fuse Lighting Panelboards: Safety, Protective, 
and Open Front Types. 


Section IV —TIncreased Capacity and Added Equipment. 
Section V  —Metering Panels with Cabinets. 


Section VI —Cabinets and Boxes for Telephone Cabinets, Junction 
and Pull Boxes only. 


Section VII —Special Power and Lighting Panelboards with Cabinets, 
and Switchboards. 


Section VIII—Numerical Index. 


bo 


—_—___—_—_ BAN Sey ——________.. 


Dominant Features of 
Benjamin-Starrett Lighting Panelboards 


Heavy Gauge — One Piece Steel Panels are provided with Adjustable Mount- 


Panel Back on which are mounted ing Studs so that Panel Adjustment may be 
Standardized Unit Bases. made both in and out laterally in box. 


All Fuse Receptacles are individual 
and are easily removed from front. 


Switches removable individually from 
front without removing trim. 


Underwriters Approved 30 Ampere 250 
volt Heavy Duty Tumbler Switches 
in both single pole and double pole. 


Fuse Receptacles have slot at side 
which permits testing of fuses without 
removing fuse. 


All Metal Panel Parts are Rust- 
proofed. 


Full Four Inch Gutter Space on all 
Four Sides of Panel. 


Harmonious design combined with 
careful engineering and _ skill in 


Switch Cover Plates 
Removable Individu- 
ally from the front. 


Unit Composition Base for all 
types of Branch Switches assure 
interchangeability of parts. 


manufacturing, make an unusually 
fine appearing panel. 


TENAMIN SERRE —————______.. 


Features of Standard Lighting Panelboards 


Exceed Underwriters’ Requirements 
Benjamin-Starrett Standard Lighting Panelboards are constructed and designed to meet 
safety requirements. They not only bear the label and have the approval of the Underwriters’ 
Laboratories, Inc., but actually exceed their requirements. 


Capacities 
The main and branch circuit connections are in accordance with the requirements of Under- 
writers’ Laboratories, Inc. All copper parts are of 98% conductivity and of a maximum current 
density of 1000 amperes per square inch cross section. 


Sectional Construction 


Benjamin-Starrett Standard Lighting Panels are 
built up of standardized composition bases which are 
attached to a steel back by means of screws. All bases 
carrying fusible branch circuit equipment are of same 
size, so changes in branch circuit equipment may be 
made after the panelboard is installed, without the 
necessity of removing panel from box. 


Standard Composition Base 


Standard Composition Bases 


Bases are of approved moulded composition having perfect insulating qualities, and are 
standardized as to design. They are individual for one two-fuse circuit or two one-fuse circuits. 


One-Piece Steel Panel Back 


The method of mounting individual parts on a steel panel back or base, makes a durable rigid 
assembly which is easily handled as a unit and which gives the individual parts that make up the 
panelboard the greatest possible protection against breakage during shipment and installation. 


Accessibility 

All parts of the Benjamin-Starrett Standard Lighting 
Panelboards are accessible from the front of the panel. 
Every part of the panel equipment may be removed and new 
or even equipment of an entirely different kind may be 
substituted without removing the panel mounting base 
from the box. This feature alone is of the greatest import- 
ance as it means—LOWEST POSSIBLE COST OF 
MAINTENANCE. 


sai 
J 
© Pil 


Steel for Strength and Service 


Benjamin-Starrett Standard Lighting Panelboards are 
strong and practically indestructable and under ordinary 
conditions will last a life time. Steel is used throughout:. 


for the barrier, for the box, for the trim, for the protective Method of Assembling Individual 
shield and for the panel back. Standard Sections on Steel Panel Back 


a pe 


BENJAMIN:STARRETT 


Features of Standard Lighting Panelboards 


Individual Circuit Marking 


Tumbler switch branch circuits are equipped with 
individual ecard holders. Other types of branch 
circuits are plainly marked by numbered metal discs. 


Card HolderMarking 
Metal Protective Shield 


Metal protective shield, thoroughly grounded, covers the entire face of Waieraliariing 


the panel on all Protective Types and some Safety Front Types. This 
shield eliminates any danger of contact with live parts when operating switches or renewing 
fuses, and gives the board an unusually fine appearance. 


Moulded Composition Receptacle 


Edison Screw Base Receptacle is of cold moulded composition with 
heavy copper screw shell. Extra large contact surface, assures perfect 
connections. Receptacle can be removed from panel as a unit by removing 
one screw. A slot in the side of the receptacle eliminates the necessity of 
removing fuses for testing. 


Phosphor Bronze Fuse Clips 


Cartridge Fuse Chlps are of spring phosphor bronze mounted on 
standardized composition bases and will accommodate fuses from 1 to 30 
ampere capacity. 


Heavy Duty Tumbler Switch 


Cartridge Fuse Clips Both Single and Double Pole Branch Circuit 

Tumbler Switches are 30ampere, 250 volt Heavy 
Duty type, ruggedly constructed to stand up under severe service 
conditions. Switch has an insulating composition top with indicating 
handle to show “off”? and ‘‘on” positions. Mechanism is of the ‘quick 
make” and ‘‘quick break” type. Switches are placed between the main 
bus bar and branch fuse receptacles, so that fuses are dead when the switch 
is in the “off” position. Entire switch can be removed from panel as a 
unit by loosening mounting screws. 


30 Ampere Single Pole 
Tumbler Switch 


Branch Circuit Knife Switch 


Knife switch is 30ampere, 125 volt capacity and is substantially 
constructed with blades of heavy copper and handle of moulded com- 
position. Contact clips are rolled in at each end for perfect alignment 
of the contact surfaces, and hinges are formed of one-piece of copper. 
Spring washers are used in riveting blade to hinge jaw, thus insuring 
perfect contact. 


Branch Circuit ; 
Knife Switch 


Steel Tumbler Switch Plate 
Steel tumbler switch cover plate is individual for each 


(—seo= 
pair of double fuse branch circuits or for each four single sae Sn ald 


fuse branch circuit. Switch plate can be readily removed. Tumbler Switch Plate 


pa 


Features of Standard Lighting Panelboards 


Positive Acting Brush Type Switch 


Brush type switch for safety panel is constructed 
of very best materials assuring sturdiness and dura- 
bility. Switch has laminated brush contacts, and is 
“quick-break”’, ‘‘double-break’”’, and non-retardable. 
A protective shield covers all parts except operating 
handle. 


Main Brush Type Switch 
Main Knife Switch 


Main knife switch is of standard design and of milled, 
pinned, and sweated construction. Blades and jaws are made 
of heavy copper and handle is large and strong. 


Easily Detachable Barrier 


Barriers are made of steel in four separate sections and are 
mounted independently of the trim by means of special hinges : 
(A) at ends of barrier sections which slip over four steel posts . 

(B) screwed to panel back. In this way a strong rigid Main Knifeswitch 
assembly requiring neither bolts nor screws is made and a 
simple straightforward pull (as shown in illustration) is all that is necessary to conveniently re- 
move barrier for wiring. Barriers are cut out on bottom edges to allow passage of wires. 


How Steel 
Barrier 
Attaches to 
Steel Panel 
Back 


A Straight 
Pull is all that 
is Necessary 
to Remove 
Barrier 
Sections. 


Finisu: All steel panel parts are finished dead black and rust proofed. 


Features of Standard Lighting 
Panel Boxes 


Durable Construction 
_ Boxes are of Code gauge galvanized steel, overlapped at corners and 
riveted, with a 34” inward flange (see illustration) all around outside 
edges. | This flange serves as an anchorage for the adjustable clamps 
(see Fig. C on opposite page) that attach trim to box. 

Four Inch Gutter Space 


All standard lighting panelboard boxes have a four inch gutter space 
which allows ample room for wiring. 


Standart : : : ng Standard Box with 

andard boxes are furnished with knockouts as shown on page 9. Barrier and Panel 

eEeEeEeEeEeEeEeEeEeEeEeEeEeESESESEE—E 
6 


s.—________ BENJAMIN) SFARREW)] ————_________» 


Features of Standard Lighting Panel Boxes and Trims 


Boxes Carried in Stock 


Code Gauge Galvanized Steel Boxes are standardized 
for all Benjamin-Starrett Standard Lighting Panelboards 
listed on pages 20 to 45, inclusive, and are carried in stock 
ready for immediate shipment. Boxes can be ordered 
and installed long before panels are required on the job. 
Same boxes can be used for flush or surface mounting. 


Accurate Location of Mounting Holes 


Holes drilled and tapped in the back of steel box to take 
the Adjustable Panel Support Studs are made by means of 
special drilling fixtures, thus assuring correct fit of panel 
in box. 


Fig. A Standard Box with Panel 
and Barrier 


Panel Adjustment 


Every standard lighting panel box has a device which 
allows outward panel adjustments up to 34” (see Fig. A). 
Panels are attached by means of four or more studs (see 
Fig. B), and can be positioned forward or backward on 
these studs by simply adjusting the locking nuts provided. 
This adjustment is necessary where edge of box is recessed 
from the plaster line. Extra large panel mounting holes 
are provided in steel panel back to permit plumbing of panel when box is out of alignment. 


Figure B 


One Piece Trim 


Trims are made of one piece of Code Gauge Steel. A mould- 
ing is welded around the outside edge of the door overlapping the 
mat, thereby forming a rabbet. 


Three Styles of Doors 
Single door, double door and door-in-a-door. 
Flush and Surface Trims 
Flush trims for Benjamin-Starrett Standard Lighting Panel Boxes have a 1” overlap all around 
outside edge. Surface trims are flush with outside edge of box. 
Trim Adjustment 


Trims are fastened to box by means of adjustable clamps (see Fig. C). These clamps permit 
flush mounting of trim where outer edge of box is recessed from plaster ee and also the correct 
aligning of trim where box is out of plumb. 


Figure C 


Hardware 


Doors on all standard lighting panelboard 
cabinets are equipped with a Yale combination 
spring latch and lock, with the exception of the 
small door on the safety type which is equipped 
with latch only. All hinges are flush. 


Directory Frames 
Metal directory frame with circuit diagram 
card is furnished as standard equipment. Glass 
covered directory frames can be furnished at prices 
shown on page 50. 
Finish 
Trims are finished dead black. 
Single Door Trim Boxes are galvanized unpainted. Door In-A-Door Trim 
od 


Box Drilling 
Of Little Sentry and Type G Panelboards 


Types NAS and hG Complete Units In Stock 


Ready for Immediate Shipment 


The various types of Little Sentry and 
Type G Panelboards listed in this cata- 
log are carried in stock as complete units 
which are ready for immediate shipment. 
Each unit consists of a panel, trim and a 
box which is provided with knockouts, 
according to type, as shown by the dia- 
grams on this page. 


1 AAA A | 
y, SSC c] 
<3 ()\ (DY ID) 
W QW YY 


10 - ¥a'K.0. 
OR 


10-72'K.0. 


is 


Little Sentry Panel Box 
Types NCG and CG Types NP, P, NEP and EP 


9" 


e* 1% 1 46" 
' 


A A AAA A_| 
eRe 
MN (DUD MO) GAL) 
N/A CASES AAD), 


DY 


1-144"K.0. 
OR 
1-2""K.0. 


12-2'K.0. 
OR 
12-¥4"K.0. 


D\w/AD\w/ABN 
DD 


@ 


e pe 


‘<< BENJAMIN STARRETT - 


Box Drilling 
For Standard Lighting Panelboards 


Boxes for the STANDARD types of lighting panels listed in this catalog are provided with 
standard knockouts as shown by the diagram below. Boxes provided with this knockout arrange- 


ment ARE IN STOCK ready for immediate shipment. Save delay by ordering boxes with 
STANDARD knockouts from stock. 


eater 
S5606006 


Boxes with standard knockouts will | | ese a a 
: ; A134) 2 l234| 3 334| 4 | Mint | f oot 
always be shipped unless otherwise Conduit, | *| 24 heal mum | Hole | Bushing 


specified, as standard knockouts will meet 
practically every wiring requirement. If 
special drilling should be required, we are 
prepared to furnish same without additional 
charge, on condition that full information 
accompanies order. 


23% AREA 314 35% iy wy 

91 VAD} VADEY, 31% 33% 334 : 1% 

34/2343 |3343564 | 1% 

eA waa LY 134 

g3344 \43¢ 3% 2 

Sm 434 3y 2 
3143343344 Si45615 ‘ | 3 

B34 354 334 414 434 aa 53% 3% 3% 

4\3iK4 |43% eps 5 5% 5 


AN] BON 


el \e 
~ 


i} 


me] co] oo] bo} bo] et] et 


4 414.434.4345 54 45% 


Nore—Special Drilling Templates, Form AD 1156, will be furnished on request. Specify 
number desired when ordering. 


OO ee ese 


9 


bo BENJAMIN-S 


General Information 


Quotations—Will be gladly furnished on 
any special lighting panelboards, power panel- 
boards, switchboards, metering panels, or any 
other special type of distribution centers. In 
requesting quotations on special apparatus 
please send complete information including 
either drawings or blue prints in order to 
avoid possibility of error. 


Drawings—Specifications sometimes require 
shop drawing of panelboards and cabinets or 
switchboards. Drawings of typical panel- 
boards and cabinets or general layout sketches 
of special panelboards and cabinets or switch- 
boards will be furnished without charge. When 
DETAIL drawings are required on_ either 
standard or special equipment they will be 
furnished on the payment of a service charge. 
This service charge is based on the amount of 
time required in making up the drawings so 
always specify amount of detail necessary. 


Delivery—Delivery will be made from our 
factory, f. o. b. Chicago, or at our option from 
New York Warehouse, f. 0. b. New York, or 
San Francisco Warehouse, f.o. b. San Francisco. 


Goods are shipped at the purchaser’s risk. 
Our responsibility ceases when they have been 
received in good condition by the transportation 
company. In no case are they to be returned 
without our consent. 


No shipments will be made from New York 
stock to Buffalo, Pittsburgh, or points West 
thereof. 

For information regarding Freight Allowance 
and Express Shipments refer to Discount Sheet. 


State definitely whether material is to be 
shipped express or freight. If no instructions 
are given shipment will be made in the most 
direct and economical manner. 


On C. O. D. or Sight Draft Shipments, for 
distributors’ account direct to their customers, 
25% of the amount of the order shall be de- 
posited with the distributor, or with this 
Company, to insure that shipment will be 
lifted promptly when presented. 


Unusual care and attention is given to 
packing and every piece of equipment leaving 
the Factory is adequately protected, see 
illustration to right. Our responsibility ends 
when the shipment is turned over to the Trans- 
portation Company in good condition, so in 
signing carrier’s receipt make sure that material 
has not been damaged in transit. 


Price—Prices and discounts are subject 
to change without notice. Description and 
listing of material in this catalog supercede 


3d 


description of materials as published in former 
catalog bulletin and circulars. 


A minimum charge of $1.00 net will be made 
on all orders. No credit memorandum will be 
issued when the net amount is less than $1.00. 


Claims for making changes or repairs on 
panelboards and cabinets will not be allowed 
unless they are previously authorized by the 
main office of the Benjamin Electric Mfg. Co. 


Claims of errors in filling orders for panel 
boards and cabinets or for defective material, 
if found to be justified will be adjusted entirely 
at the expense of the Benjamin Electric Mfg. 
Co., but it cannot be responsible for errors 
made by customers and adjustments in such 
cases will be at customers’ expense. 


Changes or Cancellations— Wher changes 
are made on an order after work has once been 
started the cost of such changes must be made 
at the customer’s expense. Where cancellations 
are issued on orders which are already in prog- 
ress a charge will be made that will prevent 
a loss to the Benjamin Electric Mfg. Co. 


A typical Benjamin-Starrett shipping crate. Sturdy reinforced 
construction of thick shock-resisting pine, securely 
cross-lapped and braced. 


Returned Material—No returned material 
will be accepted unless accompanied by a Re- 
turned Material Permission Slip, which can be 
obtained only from the main office of the 
Company at Chicago. The date and number 
of original order must accompany request to 
return material. 


Special Material cannot be returned for 
credit. Should the customer desire to dispose 
of the special material and will furnish the 
main office of the Benjamin Electric Mfg. Co. 
with the order number on whichit was shipped, 
a record will be made of it. When an order 
covering the same material is received, per- 
mission will be granted for its return and 
when received in good order; credit will be 
issued less any transportation charges and a 
service charge for handling. 


uTucC_—————————— a’ © i 


BENTAMIN:STARRETT — 


How to Order 


Benjamin-Starrett Standard Lighting Panelboards and Cabinets 


Give Catalog Number 


Catalog number may be easily found by referring to indexed illustrations on listing 
pages and selecting type, style and size of panel required. 


Give following description: 


Capacity of Mains 
*1923 Code (see page 4). 


Increased (give Capacity in Amperes 
See pages 48 and 49). 


Arrangement of Mains 


*2 Wire, 125 Volt. 

*3 Wire, 125-250 Volt. 

2 Wire, 250 Volt. 

3 Wire, 3 Phase, 125 or 250 Volt. 
4 Wire, 3 Phase, 125 or 250 Volt. 


Equipment of Mains 


*(a) Lugs only. 

*(b) Fusible only. 

*(c) Fuseless Main Knife Switch. 
*(d) Fusible Main Knife Switch. 
*(e) Fusible Main Brush Switch. 


Location of Mains 


Top of Panel or Bottom of Panel. 
(See indexed illustrations for standards. ) 


Number of Circuits 


*2 fuse panels catalogued in 4 to 32 circuits. 
*1 fuse panels catalogued in 4 to 64 circuits. 


Number of Fuses per Branch 


*2 or *1 (polarity type.) 


Type of Fuses in Branches 
*Plug, or *Cartridge. 


8. 


10. 


ta 


12. 


14. 


Type of Switches in Branches 


*30 Ampere, 250 Volt Tumbler, *30 Ampere 
Knife. 


Sub-Feed and Through Feed 


See pages 48 and 49, and give Capacity in 
Amperes. 


Style of Front 


*Safety Front—door-in-a-door, *Protected 

Front—single door or double door and 
a metal shield covering live parts, or 
*Open Front—single door with live parts 
exposed. 


Type of Trim 
*Surface mounting or *Flush mounting. 


Wiring Gutter 

*4 inches in boxes for standard lighting 
panel. 

Prices for 5” 
on page 50. 


and 6” gutter panels shown 


Cabinet Drilling 


*Regularly furnished withStandard Knock- 
outs, as shown on page 9. 

If special drilling should be required, we 
are prepared to furnish same without 
additional charge, on condition that full 
information accompanies each _ order. 
Special drilling templates (Form AD1156). 
will be furnished on request. Specify 
number desired when ordering. 


Gauge of Steel in Cabinet 


*According to National Electrical Code. 
Other thicknesses may be specified. 


*Nore—All items marked with asterisk (*) are standard equipment and are specified under 


catalog numbers. 


All other items must be specified separately. 


SECTION I 


A Line of Standardized Panelboards which meet all the requirements of the average 
Residence, Store, Small Factory or Warehouse. 


Little Sentry Panels 


COS 


114" 


Wiring Space 


yy 


See 


y 


a 
O© 


Switches 
Not 
Furnished 


4 to 12 Branch Circuits 4 to 12 Branch Circuits 

Type NP—1 Fuse Panels Type NEP—1 Fuse Panels 

Type P—2 Fuse Panels Type EP—2 Fuse Panels 
Page 14 Page 15 


Type G Panels 


i 


Ds: 


i) 


@Q) 
Oo 


@ 


Au 
Wiring Gutter 


° 


S 
© 
O¢ 
Ot 


a 
oy 
62 
o 
oz 
O= 
oy 
le 
bs 
= 

pod 
=a 


4 to 20 Branch Circuits 4 to 20 Branch Circuits 
Type NCG—1 Fuse Panels Type NPG—1 Fuse Panels 
Type CG—2 Fuse Panels Type PG—2 Fuse Panels 
Cartridge Fuses Plug Fuses 
Page 17 Page 17 
— = pS 


—<—<——$—_—__$__—____— BENJAMIN STARRETT 


=< 


SECTION I 
Little Sentry Panelboards With Cabinets 


For Residences, Apartment Buildings, Small Stores, Schools, and similar 
places having from 4 to 12 branch circuits. 


ve 


fe 
) 


OF Lerat 


1Om 


a= 


FEATURES 


1. One piece code gauge steel trim makes a 
neat appearing job. ‘Trim, barrier, shield and 
door are all in one piece, thereby reducing the 
number of parts to be handled when installing. 


2. Metal protective shield covers all live 
parts and assures absolute safety when renew- 
ing fuses. 


3. Cabinet trim is removed by removing 
four screws. 

4. Box ends, flanged and welded, provide 
threaded holes for the support of cabinet trim. 


5. <A quarter turn of four screws allows 
removal of panel as a unit to facilitate the 
pulling in of wires. 

6. Panel fuse strips can be removed to give 
easy access to neutral bar connections by 
removing two screws. 

7. Each neutral branch connection is 
stamped with circuit number and is opposite 
the fuse for that circuit, simplifying the tracing 
of circuits. This feature eliminates bunching 
of wires at one end of the panel. 


ie] 


13 


8. Fuse receptacles removed as a unit from 
the panel by removing one screw Note the 
fuse testing slot feature which makes it unneces- 
sary to remove fuse for testing. 


9. Wiring space, 11% inches. 


10. Knockouts at each end of box arranged 
to meet any conditions required in conduit or 
open wiring. See layouts on page 8. 


11. Each circuit is clearly and legibly 
numbered. 
12. A card, numbered on one side for a 


directory of circuits and showing diagram of 
wiring connections on the other side, is pro- 
vided with each panelboard. 


13. A strong, serviceable vault handle latch 
holds door tightly closed. 


14. Trim overlaps box 4% inch on all sides 
making it suitable for either flush or surface 
mounting. Trim and shield are aluminum 
bronze finish. 


joi 


Fae 


ONE FUSE PANELS 
Type NP Little Sentry Panels with Cabinets 


For 3 Wire Service 
Mains: 125-250 Volt 
Branches: 125 Volt Arranged for Plug Fuses Only 


Frniso: Trim and Shield are finished aluminum bronze. 


299989 ke 
898008 | 


No. | re | List | _ Box pinenone in Inches = | Shipping 
Cir No. Price Outside | Outside | insige paints 
4 66104 $ 6.30 9% 9% 3% 15 
6 66106 9.00 91% iil 3% iL¢/ 
8 66108 10.80 9% 12% 3% 19 
10 66110 12.60 9% 14 3% 21 
12 66112 14.40 91% 15% 3% 23 


TWO FUSE PANELS 


Type P Little Sentry Panels with Cabinets 


For 2 Wire and 3 Wire Service 
Mains: 125-250 Volt 3 Wire, 125 Volt 2 Wire 
Branches: 125 Volt Arranged for Plug Fuses Only 


Fintsu: Trim and Shield are finished aluminum bronze. 


SaaS — 
Cir No. Price Outside | Outside | Inside Pounds 
4 66204 $ 9.00 91% 121% 3% 19 
6 66206 13.50 91% 15% 3% 23 
8 66208 16.20 9% 18% 3% 26 
10 66210 18.90 91% 21% 3% 29 
12 66212 22.50 9% 241% 3% 34 
Wiring Diagrams 
| 9.9 
! 
Lt 4 
3 Wire 125-250 Volt 3 Wire 125-250 Volt 2 Wire 125 Volt 
Type NP 1 Fuse Type P 2 Fuse Type P 2 Fuse 


1 TTT EEE 
14 


pa, 


ONE FUSE PANELS 


Type NEP Little Sentry Panels with Cabinets 


Arranged with Switch Plates 


For 3-Wire Service 
Mains: 125-250 Volt 
Branches: 125 Volt Arranged for Plug Fuses 


Fintso: Trim and Shield are finished aluminum bronze. 


No No Cat. List Box Dimensions in Inches Shipping 
ct [sti] fe | Bis [SRST otitis | pee | 
4 4 66304 §$ 8.60 9% 15% 3% 16 
6 8 66306 12.50 91% 20 3% 18 
8 8 66308 15.50 91% 21% 3% 20 
10 12 66310 20.00 91% 27% 3% 23 
Lome Ome 663120 23.00 9% 29 31% 24 
Switches not included in above prices. Tumbler Switches 


Not Furnished 


TWO FUSE PANELS 


Type EP Little Sentry Panels with Cabinets 


Arranged with Switch Plates 
For 2 Wire and 3 Wire Service 
Mains: 125-250 Volt 3 Wire, 125 Volt 2 Wire 


Branches: 125 Volt Arranged for Plug Fuses 


Frnisu: Trim and Shield are finished aluminum bronze. 


No. No Cat List Box Dimensions in Inches Shipping 
of Switch ree Price | Wide Hiyh Deep Weight 
Cir Mtgs. ; Outside | Outside | Inside Pounds 
a 4 66404 $12.50 9% 18% 3% 20 
6 8 66406 18.50 9% 241% 3% 24 
8 8 66408 23.20 9% 27% 3% 27 
10 12 66410 26.40 9% 35 3% 31 
12 We 66412 30.50 9% 38 3% 36 
: ’ 5 2 Tumbler Switches 
Switches not included in above prices. Not Furnished 
ce oF 


F BENJAMIN-STARRETT 


Type G Panelboards with Cabinets 


For Residences, Store Buildings, Apartment Buildings, Churches, Factories, 
Hospitals and Sanitariums. 


> 


v 


\/ 


© 


36 


A 


— 4 


v 


©) 


v 


Om@ 


FEATURES 


1. Surface or flush mounting trim of one- 
piece code gauge steel. 


2. Combination steel barrier and shield. 


3. Adjustable trim clamps secure fronts 
to boxes and permit plumbing of trim when 
box is out of alignment. These clamps are 
self-adjusting when box is recessed from 
plaster surface. 


4. Adjustable panelboard supports, which 
allow an outward adjustment when box is 
recessed from plaster surface, are standard 
equipment on all boxes. They also permit 
adjustment to center, and plumb the panel- 
board when box is out of alignment. 


we 


5. Wiring gutter of 3 inches all around. 


6. Fuse receptacles removable as a unit 
from the panel by removing one screw. Note 
the fuse testing slot feature which makes it 
unnecessary to remove fuse for testing. 


7. Door is provided with a Yale com- 
bination spring latch and lock and circuit 
directory holder and ecard. 


8. Composition bases mounted on one- 
piece steel back. 


9. Extra large mounting holes for plumbing 
panel in box. 


10. Each circuit individually marked. 


8 Sanh 


Re eee ye 4 


Type G Panels with Cabinets 
Type NPG Panels with Cabinets 3 Wire Mains 


1 Fuse Branches 
For 3 Wire Service 


Mains: 125-250 Volt—1 Fuse Branches 
Branches: 125 Volt Arranged for Plug Fuses Only 


Panel with Cabinet : Gutter Box Dimensions in Inches Shipping lo ©) 
Surrace Flush | ce | Space Wide High Deep Weight °) & 
Cat. No. Cat. No. Ae Inches Outside | “Outside Inside Pounds 0) 

60104 60154 ~—- $21.00 3 11% 13% 3.34 92 ‘ss 
60106 60156 23.00 3 11% 15 33, 27 2 
60108 60158 25.00 3 11% 16% 334 32 e® 
60110 60160 27.50 3 11% 18 33, 37 e® 
60112 60162 30.00 3 11% 19% 33, 42 r® 
60114 60164 32.50 3 111% rail 33, 47 @ 
60116 60166 35.00 3 11% 22% 3%, 52 © 
60118 60168 37.50 3 11% 24 33, 57 

60120 60170 40.00 3 11s 25% 33, 62 


Type PG Panels with Cabinets Ea met eae |e 


For 2 Wireand 3 Wire Service 2 Fuse Branches 
Mains: 125-250 Volt 3 Wire, 125 Volt 2 Wire 
2 Fuse Branches 


Branches: 125 Volt Arranged for Plug Fuses Only -_ 
Panel with Cabinet ; Gutter Box Dimensions in Inches Shipping OO 
Surface Flush | ae | Space Wide High Deep Weight ESS 
Cat. No. Cat. No. Ws Inches Outside | Outside Inside Pounds 5) 
60204 60254 $20.00 3 {isso eles 3%), 17 oo 
60206 60256 25.00 3 11% 191% 334 20 6.0 
60208 60258 30.00 3 11% 22% 334 22 = 
60210 60260 35.00 3 11 ioe memo is 3%, 24 oo 
60212 60262 40.00 3 11% 28% 354 27 Ov 
60214 60264 45.00 3 11% 31% 3% 3 Ou.@ 
60216 60266 50.00 3 11% 3414 33, 39 OvO 
60218 60268 55.00 3 11144 387% 3% 3 
60220 60270 60.00 a 11% 401% 3% 3 


Type NCG Panels with Cabinets 3 Wire Mains 


For 3 Wire Service i Fuse Branches 


Mains: 125-250 Volt—1 Fuse Branches 
Branches: 125 Volt Arranged for Cartridge Fuses Only 


ee a ) 
CODANOCWODSA |: 


Panel with Cabinet tier Gutter ; Box Dimensions in Inches Shipping - ~ ” i 
Surface Flush Pita Space Wide | High Deep Weight oa miller ee] 
Cat. No. Cat. No. Inches Outside Outside Inside Pounds = | Be] 
60304 60354 $23.00 3 13% 15% 334 24 = =! 
60306 60356 25.50 3 13% 17 354 30 et sa! 
60308 60358 27.50 3 13% 18% 334 35 om wlbe 36 
60310 60360 30.50 3 13% 20 3% 41 | Ble Bs 
60312 60362 33.00 3 13% 21% 3% 46 pe ped 
60314 60364 36.00 3 13% 23 334 52 $2 &l/a 56 
60316 60366 38.50 3 13% 24% 3% 57 s= rE) 
60318 60368 41.00 3 13% 26 3% 63 
60320 60370 44.00 3 13% 27% 3%4 68 
Type CG Panels with Cabinets 2 or 3 Wire Mains 
For 2 Wire and 3 Wire Service 22 AOD EER 
Mains: 125-250 Volt 3 Wire, 125 Volt 2 Wire 
2 Fuse Branches rem f 
Branches: 125 Volt Arranged for Cartridge Fuses Only i fee 
Panel with Cabinet ] Gutter Box Dimensions in Inches Shipping S molbe 6 
Surface Flush ae Space Wide High Deep Weight = os a on : 
Cat. No. Cat. No. pice Inches Outside | Outside Inside Pounds = Belle Be 
60404 60454 $22.00 3 13% 18% o 34 ig baie fon 
60406 60456 27.50 3 1334 21% 3% 22 baat | alice’ 
60408 60458 33.00 3 13% 24¥, 354 24 be fine 
60410 60460 38.50 3 13% 271% 334 26 = Bllee Ze 
60412 60462 44.00 3 3% 30% 334 30 ss Be) 
60414 60464 49.50 3 13% 33% 334 30 npr, 
60416 60466 55.00 3 13% 36% 3% 35 
60418 60468 60.50 3 13% 39% 3% af 
60420 60470 66.00 3 13% 42% 3% 41 


ily 


ta BENAMIN-STARRERT 


SECTION II 
One-Fuse Panelboards With Cabinets 


Each one fuse panel is equipped with Edison plug fuse receptacles or cartridge fuse clips in the 
ungrounded side of the branch circuit. Grounded wires are fed direct from copper neutral bar 
and are not fused. Where switches are shown they are single pole. For general specifications, see 


pages 4, 5, 6, and 7. 


Safety Front Type 


Door-in-a-Door Cabinet 


This safety type panel is of double-door 
construction—one smaller door within a 
larger one. Opening of the small door gives 
access to the switches of the branch circuits 
only, while opening of the large door exposes 
the full face of the panel. 


This safety panel is intended for installa- 
tions where branch switches are operated by 
inexperienced persons and fuses renewed by a 
maintenance man. The large door is pro- 
vided with a Yale combination spring latch 
and lock, which effectively prevents over 
fusing by an inexperienced person, tampering 


with the main or branch connections, and 
theft of fuses. All cabinets are regularly 


supplied with circuit directory card 
mounted in a metal directory frame— 
SAFETY FRONT TYPE see illustration. 


Open Front Type 
Single Door Cabinet 


The open front panel has a single door 
which gives access to all switches, fuses 
and connections on the face of the panel. 
Because of its open front construction 
this type is suitable for use only where 
operation of switches and replacement of 
fuses is made by some experienced person. 
The door is equipped with a Yale com- 
bination spring latch and lock which pre- 
vents unauthorized tampering. All cabi- 
nets are regularly supplied with circuit 
directory card mounted in a metal 
directory frame—see illustration. 


aad 


ane 
7 
xd 
—_ 
= 
ae 


Da ee eae ee 


GRRRRI 


OPEN FRONT TYPE 


18 


a 


ENJAMIN:STARRETT — 


SECTION II 


One Fuse Panelboards With Cabinets 


Protective Front Type 
Single Door Cabinet 


This panel differs from the standard 
safety panel only in that it is furnished 
with a single door trim. 


The cabinets for panels with Fusible 
Main Knife Switches have two individual 
doors, one exposing the knife switch, the 
other giving access to branch circuit 
switches and fuses. Both doors are 
equipped with a Yale combination spring 


latch and lock. 


Panels with Fusible Mains, have a small 
door in the protective shield, giving access 
to the main fuses. 


All cabinets are equipped with a 
Circuit Directory Card mounted in a 


nnin ale sie RIB SIA BIB 8 


ies | 
Cm 
cms 
Tt 
Co 
Cm 
Ci 
fs | 
om 
tm 
cm 
pesca 
ict | 


metal directory frame—see illustra- 


tion. 


Type NSPT 
Type NSCT 


Type NLP 
Type NEPT 


Type NOC 

Type NOCT 
Type NOPK 
Type NOCK 


a 


PROTECTIVE FRONT TYPE 


Index to Section II 


One-Fuse—Safety Front Type 


Hie ULETE UL LGRESSOTTO NOC, 1 OTA PLUG. [USES vga ae a ae en eee Page 20 
DDC DiLGhes AIT Ongedss OV, CATITIOde JUSES: .... 0.22 ee ee Page 21 
One-Fuse—Protective Front Type 
PALIT CURLED ULUMILLSCSEONUY mime, Marae. oh ek, ae tee Page 22 
COL aro LeNeSEOLTONOCUE Ole DIAL | USCS a.m” ee nae eee Page 23 
One-Fuse—Open Front Type 

PALI Cm OTACOT UT LOT CAI ULSCS. OLLI Me. cutee Se la gee Page 24 
LDL eta OUNCE Se TERONUC, | OTACOTUTLOGE [ULSCS.ian ater ere ene Page 25 
IME PSIPOTO ES CHE OP TOUE NOT TOUIOISOS SAE Brot Berscis On oe Ba ee Page 26 
TG eso UWILChes QTLANg cue 1 Of CATITIOGE |] USCS tan a Page 27 

of 


— 


ENJAMIN STARRETT 
3Wire Mains Type NSPT Safety Panels with Cabinets 


1 Fuse Branches Branches: 2 Wire, 30 Amp. 250 V. HEAVY DUTY Tumbler Switches, 
Plug Fuses. Mains: 125-250 Volt. 


ie 


No. Panel with Cabinet A Capacity | Gutter Box Dimensions in Inches Shipping 
DOOR IN A DOOR of Surface Flush taut of Mains | Space fa Wide High Deep | Weight 
CABINETS i Cat.No. | Cat.No. Amps. _| Inches Outside | Outside | _Inside_| Pounds 


PANELS WITH MAIN LUGS ONLY 


4 52004 52104 $50.00 30 
8 52008 52108 60.00 60 
1 5201 2eeoc le 70.00 60 
16 52016 52116 86.00 100 


20 52020 52120 96.00 100 
24 52024 52124 106.00 100 
28 52028 52128 116.00 100 
32 52032 52132 126.00 100 


36 52036 52136 146.00 200 
40 52040 52140 156.00 200 
44 52044 52144 172.00 200 
48 52048 52148 182.00 200 


52 52052 52152 192.00 200 
56 52056 52156 206.00 200 
60 52060 52160 222.00 200 


= 
on 
os 
as 
i) 
on 
eo) 

ae 
a” 
a 
am 
on 
cr) 
jen 


ane ele cls eis cjes 


PEP PEEP PEPE PP PP 
0] 
w 
o 
bo 
te 
Ss 
ive) 
oo 
awe 
w 
SS 
ra 
Ne} 
Oo 


With Main Lugs Only. 
PANELS WITH FUSIBLE MAINS 


4 52204 52304 $62.00 30 R21 241, 21 4% 105 
8 52208 52308 74.00 60 R24 241% 24 4% 120 
12 52212 5232 86.00 60 R27) 241%! 27 4% 135 
16 52216 52316 102.00 100 R36 24% 36 44% 180 


4 
4 
4 
4 
20 52220 52320 114.00 100 4 R39 24% 39 4% 195 
24 52224 52324 126.00 109 4 R42 24%! 42 4, 210 
28 52228 52328 138.00 100 4 R45 24% 45 4% 225 
32 52232 52332 150.00 100 4 R48 2416! 48 4%, 240 
4 
4 
4 
4 
4 
4 
t 


36 52236 52336 172.00 200 R54 2414) 54 4%, 270 
40 52240 52340 184.00 200 R57 924% 57 4%, 285 
44 52244 52344 204.00 200 R60 24% 60 4% 305 
48 52248 52348 216.00 200 R63 24% 63 4Y%, 325 


52 52252 52352 228.00 200 R66 2416) 66 4% 345 
56 52256 52356 240.00 200 R69 24% 69 4% 365 
60 52260 52360 252.00 200 R72 24% 72 4% 385 


With Fusible Mains. 


PANELS WITH FUSIBLE MAIN BRUSH TYPE SWITCH 


4 52404 52504 $80.00 30 
8 52408 52508 96.00 60 
12 52412 52512 108.00 60 
16 52416 52516 132.00 100 


20 52420 52520 144.00 100 
24 52424 52524 156.00 100 
28 52428 52528 168.00 100 
32 52432 52532 188.00 100 


36 52436 52536 222.00 200 
40 52440 52540 236.00 200 
44 52444 52544 248.00 200 
48 52448 52548 260.00 200 


52 52452 52552 272.00 200 

56 52456 52556 286.00 200 
With Fusible Main Brush 60 52460 52560 302.00 200 
Type Switch. 


Ree PEPER PPE PPP 
a 
oO 
p 
bo 
~ 
es 
ol 
rs 
nS 
Be 
bo 
ol 
Ol 


PANELS WITH FUSIBLE MAIN KNIFE SWITCH 


4 52604 52704 $76.00 30 t R27 24% 27 4% 135 
8 52608 52708. 93.00 60 4 R33 24% 33 4% 150 
12 526i CeO (al Cee os) 60 4 R36 241% 36 4145 165 
16 52616 52716 130.00 100 4 R42 24% 42 4% 195 
20 52620 52720 142.00 100 4 R45 24% 45 44% 210 
24 52624 52724 154.00 100 t R48 24% 48 4%, 225 
28 52628 52728 166.00 100 4 R51 24% 51 4% 240 
32 52632 52732 186.00 100 1 R54 24% 54 4V, 255 
36 52636 52736 219.00 200 4 V60 24% 60 5% 290 
40 52640 52740 233.00 200 4 V63 241% 63 5% 310 
t+ 52644 52744 245.00 200 4 V66 24% 66 5% 330 
48 52648 52748 257.00 200 4 V69 24% 69 5% 350 
52 52652552752) 269.00 200 4 V72 «24% 72 54% 370 
56 52656 52756 283.00 200 t V75 24% 75 5 390 
60 52660 52760 299.00 200 4 V78 241% 78 5% ©6410 


With Fusible Main Knife 
Switch. Panels with Unfused Main Switches can be furnished at same prices as Panels with 


Fusible Main Switches. 


20 


—<$___________— BENJAMIN STARRELT aa 


Type NSCT Safety Panels with Cabinets 3 wire Mains 


Branches: 2 Wire, 30 Amp. 250 V. HEAVY DUTY Tumbler Switches, 1 Fuse Branches 
Cartridge Fuses. Mains: 125-250 Volt. 


| Panel with Cabinet | with Cabinet List Capacity Gutter Box Dimensions in Inches 
Cat.No. Cat. No. Amps. | Inches Outside | Outside | Inside 


PANELS WITH MAIN LUGS ONLY 


Shipping DOOR IN A DOOR 
Weight 


Pounds CABINETS 


4 52804 52904 $50.00 S0int ety, AR1G@ ode 188 dee | 90 
8 52808 52908 60.00 600) 940 ROtee 24m 1 ed iee wal 05 | 
12 52812 52912 70.00 60-624. “RDA 924%, 994" 9434 9120 ot 
ioeem525160 629160". 86.00 100° +4) R279 24325 7 Puig. 135 er 
eh 
20 52820 52920 96.00 100 4 R80 24% 30 4% 4150 er 
24 52824 52924 106.00 100 4 R33 24% 33 4% 165 rede 
pameeh280S.) 59998 116.00. 100 . 4) R36 02445) 36. 64165 180 - 
32) 62832 «452082 412600 100 4 R39 24% 3 4% 195 - 
36 52836 52936 146.00 200 4 R42 24% 42 4% 210 ~ 
40 52840 52940 156.00 200 4 R45 24% 45 414 225 = ; 
44 52844 52944 172.00 200 4 R48 24% 48 4% 240 ps) 
48 52848 52948 182.00 200 4 R51 24% 51 4% 255 a eS 
52 52852 52952 192.00 200 4 R54 24% 54 4% 270 
56 52856 52956 206.00 200 4 R57 24% 57 41% 285 
60 52860 52960 222.00 200 4 R60 24% 60 4% 305 WitMR Leas Only 
PANELS WITH FUSIBLE MAINS 
4 53004 53104 $62.00 30 meee 2 (eon? 1 gee ed teed 
8 53008 53108 74.00 CO p ede RO4GNO4 ee 4120 
d2mee 580125 531126) = 86.00 GONE mpd Se RO7 maou oT 4 tee TSE 
BGmmeeS 50168 63116001 02.00nur 1000 ede eo RSGame 241455 36 die 180 
20 53020 53120 11400 100 4 R389 24% 39 4% 195 
Bi 53024053124 9 196,00) 100 eae R4208 2416, rao, FA, 7910 
285) 58028 53128 138.00 100 4. R45 24% 45 43% . 295 
32 53032 53132 150.00 100 4 R48 24% 48 4% 240 
36 53036 53136 172.00 200 4 R54 24% 54 4% 270 
Amer 53040098 53140588 184.00 2008 94) 9 R579 84445 57 44 285 
44 53044 53144 20400 200 4 R60 24% 60 4% 305 
48 53048 53148 21600 200 4 R63 24% Bendy 825 
52 538052 53152 22800 200 4 R66 24% 66 4% 345 
56 53056 53156 240.00 200 4 R69 24% 69 4% 365 
60 53060 53160 252.00 200 4 R72 24% 72 4% 385 With Fusible Mains. 


PANELS WITH FUSIBLE MAIN BRUSH TYPE SWITCH 


4 53204 53304 $80.00 30 4 R30 24% 
8 53208 53308 96.00 60 R33 24% 33 AY, 


4 Ze A150 
12 53212 53312 108.00 COMMER EER 3 GNERO4 in eee oe Wace 465 
16 53216 53316 132.00 100 4 R42 24% 42 414 195 
20 53220 53320 144.00 100 4 R45 24% 45 4% 210 
94 53224 53324 156.00 100 4 R48 2414 48 414 225 
990 53299 53328 168.00 100 °° 4° R51 24% 651 414 240 
32 53232 53332 188.00 100 4 R54 24% 54 41% 255 
36 53236 53336 222.00 200 4 V60 24% 60 5% 290 
AO 53240 53340 236.00'° 200 4° 63 241% 63 5% 310 
44 53944 53344 24800 200 4 4V66 24% 66 5% 330 
48 53248 53348 260.00 200 4 V69 24% #69 51%, 350 
52 69252 53352 272.00 200 4 ##V72 24% +72 %|5% 370 
BE 53066 | 53356). 286.00 200 4 «°° -V75«244%8 75 | 51% - 390 
60 53260 53360 302.00 200 4 478 24% 78 5% 410 Wid Fisibia MAL Bred, 


Type Switch. 


4 53404 53504 $76.00 30 4 R27 24% 27 4% 135 

8 53408 53508 93.00 60 4 R33 24% 3 4% 150 
12 53412 53512 105.00 60 4 R36 24% 36 41% 165 
16 53416 53516 130.00 100 4 R42 24% 42 4% 195 
20 53420 53520 142.00 100 4 R45 24% 45 41% 210 
24 53424 53524 154.00 100 4 R48 24% 48 4% 225 
28 53428 53528 166.00 100 4 R51 241% 51 4% 240 
32 53432 53532 186.00 100 4 R54 24% 54 4% 255 
36 53436 53536 219.00 200 4 v60 24% 60 5 290 
40 53440 53540 233.00 200 4 V63 241% 63 514 310 
44 53444 53544 245.00 200 4 V66 241% 66 514 330 
48 53448 53548 257.00 200 4 Vv69 244 69 514 350 
52 53452 53552 269.00 200 t V72 =24% 72 5 370 
56 53456 53556 283.00 200 4 V75 24% 75 514 390 
60 53460 53560 299.00 200 4 V78 24% 78 5Y 410 


With Fusible Main Knife 
Panels with Unfused Main Switches can be furnished at same prices as Panels with Switch. 


Fusible Main Switches. 21 


te BENJAMIN:STARRETT am 
3Wire Mains ‘Type NLP Protective Panels with Cabinets 
1 Fuse Branches Branches: 2 Wire, Plug Fuses Only. 
Mains: 125-250 Volt. 
SINGLE DOOR | Panel with Cabinet _| with Cabinet Capacity | Gutter saenee 
CABINDTS ren [tim (ote [SRE ES) i [a ota | io | Bae 


PANELS WITH MAIN LUGS ONLY 


8 53608 53708 $46.00 60 4 R18 24% 18 4% 90 
16 53616 53716 56.00 100 4 R21 24% 21 4% 105 
24 53624 53724 66.00 100 4 R24 24% 24 4% 120 
32 53632 53732 76.00 100 t R27 24% 27 4% 135 
40 53640 53740 100.00 200 4 R30 24% 30 4%, 150 
48 53648 53748, 115.00 200 4 R33 24% 33 4%, 165 
56 53656 53756 130.00 200 4 R36 24% 36 4% 180 
64 53664 53764 150.00 200 4 R39 24% 39 4% 195 


With Main Lugs Only 


PANELS WITH FUSIBLE MAINS 


8 53808 53908 $60.00 60 4 R21 24% 21 4% 105 
16 53816 53916 80.00 100 4 R30 24% 30 4% 150 
24 53824 53924 90.00 100 4 R33 241% 33 4% 165 
32 53832 53932 105.00 100 4 R36 24% 36 4% 180 
40 53840 53940 130.00 200 4 R42 24% 42 4% 210 
48 53848 53948 145.00 200 4 R45 24% 45 4% 225 
56 53856 53956 160.00 200 4 R48 24% 48 4y, 240 
64 53864 53964 175.00 200 4 R51 24% 51 44%, 255 


8 54008 54108 $74.00 60 4 R30 24% 30 4% 135 
16 54016 54116 95.00 100 4 R36 24% 36 4% 165 
24 54024 54124 108.00 100 4 R39 9.241% 39 4% 180 
32 54032 54132 120.00 100 4 R42 241% 42 4u% 195, 
40 54040 54140 160.00 200 4 V48 =24% 48 54 225 
48 54048 54148 180.00 200 4 vol 24% 51 buy 245 
56 54056 54156 200.00 200 4 V54 24% 54 5 260 
64 54064 54164 220.00 200 1 WAY 24% DT 514 275 


With Fusible Main Brush 
Type Switch. 


PANELS WITH FUSIBLE MAIN KNIFE SWITCH 


8 54208 54308 $71.00 60 4 R30 24% 30 4% 135 
16 54216 54316 93.00 100 { R36 24% 36 41% 165 
24 54224 54324 =6106.00 100 1 R39 2414 39 4% 180 
32 54232 54332 118.00 100 4 R42 24% 42 4% 195 
40 54240 54340 157.00 200 4 V48 24% 48 54 225 
48 54248 54348 177.00 200 4 v51 2414 51 5Y% 245 
56 54256 54356 197.00 200 1 V54 24% 54 5% 260 
64 54264 54364 217.00 200 4 V57 2414 57 54 275 


With Fusible Main Knife 
Switch. 


Panels with Unfused Main Switches can be furnished at same prices as Panels with 
Fusible Main Switches. 29 


EEE 


i 


BENJAMIN-STARRETT 
Type NLPT Protective Panels withCabinets 3 Wire Mains 


Branches: 2 Wire, 30 Amp. 250 V. HEAVY DUTY Tumbler Switches, 1 Fuse Branches 
Plug Fuses. Mains: 125-250 Volt. 


|__Panel with Cabinet | List | Capacity | Gutter a prac Hobe | Wee SINGLE DOOR 
panel wih Cabinet _] Flush of Mains | Space Wide High eight S 
Price | amos. | trons eH ea Bead hot CABINETS 


PANELS WITH MAIN LUGS ONLY 


4 54404 54504 $34.00 30 4 R18 241% 18 4% 90 
8 54408 54508 40.00 60 4 R21 241% 21 4% 105 
12 54412 54512 50.00 60 4 R24 241% 24 41% 120 = 
16 54416 54516 74.00 100 4 R27 24% 27 4% 135 = 
20 54420 54520 84.00 100 4 R30 2416 30 41% 150 = 
24 54424 54524 94.00 100 4 R33 24% 3 4% 165 rm 
28 54428 54528 104.00 100 4 R36 241% 36 4% 180 es 
32 54432 54532 114.00 100 4 R39 24% 39 4% 195 an 
36 54436 54536 134.00 200 4 R42 241% 42 4% 210 = 
40 54440 54540 144.00 200 4 R45 24% 45 4% 225 = 
44 54444 54544 160.00 200 4 R48 24% 48 4% 240 ia 
48 54448 54548 170.00 200 4 R51 24% Ou 4% 255 
52 54452 54552 180.00 200 4 R54 241% 54 4% 270 
56 54456 54556 194.00 200 4 R57 241% 57 4% 285 
60 54460 54560 210.00 200 t R60 24% 60 4% 305 
PANELS WITH FUSIBLE MAINS 
4 54604 54704 $46.00 30 4 R21 241% 21 4% 105 
8 54608 54708 58.00 60 4 R24 241% 24 4% 120 
12 54612 54712 70.00 60 4 R27 24% 27 4% 135 
16 54616 54716 90.00 100 4 R36 24% 36 4% 180 
20 54620 54720 102.00 100 4 R39 2416 39 4% OD 
24 54624 54724 114.00 100 4 R42 24% 42 4% 210 
28 54628 54728 126.00 100 + R45 24% 45 4% 225 
32 54632 54732 138.00 100 4 R48 241% 48 4% 240 | 
36 54636 54736 160.00 200 4 R54 241% 54 414 270 
40 54640 54740 172.00 200 4 R57 241% ort 4% 285 i 
44 54644 54744 192.00 200 4 R60 241% 60 4% 305 
48 54648 54748 204.00 200 4 R63 24% 3 41% 325 
52 54652 54752 216.00 200 4 R66 241% 66 41% 345 
56 54656 54756 228.00 200 4 R69 24% 69 4% 365 
60 54660 54760 240.00 200 4 R72 241% 42 4% 385 With Fusible Mains 
PANELS WITH FUSIBLE MAIN BRUSH TYPE SWITCH 
4 54804 54904 $68.00 30 4 R30 24% 30 4% 135 
8 54808 54908 84.00 60 4 R33 24% 33 4% 150 
12 54812 54912 96.00 60 4 R36 ue 36 4% 165 
16 54816 54916 120.00 100 4 R42 24% 42 4, 195 
20 54820 54920 132.00 100 + R45 2444 45 4% 210 
24 54824 54924 144.00 100 4 R48 24% 48 4% 225 
28 54828 54928 156.00 100 4 R51 241% 51 4% 240 
32 54832 54932 176.00 100 + R54 24% 54 4% 255 
36 54836 54936 210.00 200 4 V60 241% 60 54 290 
40 54840 54940 224.00 200 4 V63 24% 63 54, 310 
44 54844 54944 236.00 200 a V66 24% 66 54 330 
48 54848 54948 248.00 200 4 V69 24% 69 5 350 
52 54852 54952 260.00 200 4 V72 24% 72 54 370 
56 54856 54956 274.00 200 4 V75 24% 75 54 390) 
60 54860 54960 290.00 200 4 £4.V78 241% 78 5% 410 with Pusible Main Brush 
ype Switch. 


PANELS WITH FUSIBLE MAIN KNIFE SWITCH 


4 55004 55104 $64.00 30m ede RO7g od ee 7 ee 4 3G 
8 55008 55108 81.00 604 ee RSG mmeed eee s S emedgeme 5() 
4 55012 55112 93.00 60). 4 R369 241 86a dts 165 
760m 5501600855116) 9 118.00) 100 400 R42 5e 24420) 42 4k 195 
20 55020 55120 130.00 100 4 R45 24% 45 4% 210 
24 55024 55124 14200 100 4 R48 24% 48 4% 295 
28 55028 55128 154.00 100 4 R51 24% 51 4% 240 
829m) 5503250 55182) 9174.00 100 «4 «R545 2496" 1548 sag (O55 
36 55036 55136 207.00 200 4 V60 24% 60 5% 290 
40 55040 55140 22100 200 4 63 24% 68 54% 310 
44 55044 55144 233.00 200 4 66 24% 66 5% 330 
48 55048 55148 245.00 200 4 V69 24% 69 5% 350 
52 55052 55152 257.00 200 4 V72 24% #72 5% 370 
R6 55056 55156 271.00 200 4 V75 24% 75 5% 390 
GO ge 55060955 1600 8287.00.89 200 ged 1 V78™ notte OTe Sd, 410m wat erp a neaTn nite 


Panels with Unfused Main Switches can be furnished at same prices as Panels with Switch 
Fusible Main Switches. 23 


if BENJAMIN STARRETT ba 
3Wire Mains Type NOC Open Front Panels with Cabinets 


1 Fuse Branches Branches: 2 Wire, Cartridge Fuses Only. 
Mains: 125-250 Volt. 


| Panel with Cabinet | List Capacity | Gutter 
a ee Flush Price | °F Mains | Space 
Cat.No. | Cat.No. Amps._| Inches 


Box Dimensions in Inches 


Wide High 
Outside | Outside | Inside 


Shipping 
Weight 
Pounds 


SINGLE DOOR 
CABINETS 


PANELS WITH MAIN LUGS ONLY 


<> = 

> ne 8 55208 55308 $46.00 60 4 R18 24% 18 4% 90 

ia oe 16 55216 55316 56.00 100 4 R21 24% 21 4% 105 

Po 2% 24 65224 55324 «66.00 «1004 AA 24_Ci‘i kd (120 

as oa 32, 55282 9956332 9 76.005) 100) m4g) Rov) 244, une] ee 

am ez Be 

am et BS 

«> == 40 55240 55340 100.00 200 4 R30 24% 30 4% 1650 

Es Be 48 55248 55348 115.00 200 4 R83 24% 38 4% 165 
56 55256 55356 130.00 200 4 R36 24% 36 4% 180 
64 55264 55364 150.00 200 4 R39 24% 39 4% 195 


PANELS WITH FUSIBLE MAINS 


8 55408 55508 $60.00 60 “4 Rel 24165 oi Raye 
16° 55416 55516 $0.00 ©100 4 R30 24% 30 “44 mi50 
Of 55424 55524 1 90.00 ~ 100 [4 | R330 24%, 938° edagmence 
32 55432 55532 ° 105.00 100 4 R86 24% 36 4% 180 
40 | 55440 55540 130.00 200 4 R42 94% 42 | “Aap Not 
48 55448 55548 145.00 200 4 R45 24% 45 4% 225 
56 55456 55556 160.00 200 4 R48 24% 48 4% 240 
64 55464 55564 175.00 200 4 R51 24% 51 4% 255 


PANELS WITH FUSELESS MAIN KNIFE SWITCH 


30 4% 135 


8 55608 55708 $71.00 COE e420 ume4 
16 55616 55716 93.00 100 .4 <R36 244% 86 41, uetes 
24 55624 55724 106.00 100 4 R39 24% 39 4% 180 
82 155632. 55732. 118.00 100 48) R42. 994128 4 ea 
40 55640 55740 157.00 200 4 R48 24% 48 4% 225 
48.’ 55648 55748 177.00 200 9 4. R51) 2434 hee 
56 55656 55756 197.00 200 4 R54 24% 54 4% 260 
64 55664 9 55764. 7217.00 200° 9948 R57) 24260 57 or 
With F eee Main Knife 
Switch. 
PANELS WITH FUSIBLE MAIN KNIFE SWITCH 
8 55808 55908 $71.00 60 "347 R309 924120 30 
a 46 55816 55916 93.00 100° 4 R36 24% 36 41,0 ies 
—— 24 55824 55924 106.00 100 4 R39 24% 39 4% 180 
ie 32 55832 55932 118.00 100 4 R42 24% 42 41% 495 
‘| 
=m 
pod 40 55840 55940 157.00 200 4 V48 24% 48  5y 225 
"| fers 48 55848 55948 177.00 200 4 V51 24% 51 5% 245 
56 55856 55956 197.00 200 4 V54 24% 54 5y% 260 
. 64 55864 55964 217.00 200 4 V57 24% 57 #£=+5y% 275 
With Fusibie Main Knife 
Switch. 
ee oy 


24 


—$___—_——___________ BENJAMIN STARRETT Pa 
Type NOCT Open Front Panels with Cabinets — 3 Wire mains 


Branches: 2 Wire, 30 Amp. 250 V. HEAVY DUTY Tumbler Switches, 1 Fuse Branches 
Cartridge Fuses. Mains: 125-250 Volt. 


Panel with Cabinet 


Box Dimensions in Inches 


Shipping SINGLE DOOR 


? List vay elt ay Box sepia 
0 Surface Flush : of Mains | Space Deep eight ; 
: Cat.No. Cat. No. i) Amps. | Inches No. Outside | Outside | Inside | Pounds CABINETS 


PANELS WITH MAIN LUGS ONLY 


4 56004 56104 $34.00 30 Ae RiGee 4 ees AY, 90 

8 56008 56108 40.00 60 A Rote 4 ee 44; 105 

12 56012 56112 50.00 60 4 R24 24% 24 41 > 120 = ae - 
16 56016 56116 74.00 100 4 R27 2414 27 die 135 tc >it OS Sle» 

¥ 2 

20 56020 56120 84.00 100 4 RSOe 24165 30 4% 150 > <3 
24 «56024 56124 94.00 100 4 RSS an 24 ieee 4% 165 v< >a le 
28 56028 56128 104.00 100 4 -R36." 2414 86 4% 180 < eee ele = 
32 56032 56132 114.00 100 4 R39 24% 39 4%, 195 econ els a 
36 56036 56136 134.00 200 4 R42 24% 42 4% 210 ts > eeeres< = 
40 56040 56140 144.00 200 de R45 2456 ee 4 4% 295 2 lon, oe) 

44 56044 56144 160.00 200 4 R48 241%, 48 4% 240 <2 ee 
48 56048 56148 170.00 200 4 R51 24% £51 4% 255 Re 
52 56052 56152 180.00 200 di R542 od ied 2% 270 

56 56056 56156 194.00 200 4 R57 24% 57 44% 985 

60 56060 56160 210.00 200 45)-R60 2414 1.60 414 305 With MaGiENEs Ons 

PANELS WITH FUSIBLE MAINS 

4 56204 56304 $46.00 30 A RO famed tor es Sie 105 

8 56208 56308 58.00 60 AUS RO4e S341 89d £7, 10 

12 56212 56312 70.00 60 Awe ROT 41 Bee oy 116 9135 

16 56216 56316 90.00 100 A WE) Gee BY 4% 180 
20 56220 56320 102.00 100 ARS oes ce 39 44% 195 

24 56224 56324 114.00 100 4 R42 24% 42 4% 210 

28 = 56228 «= 456328) = s«126.00 ~—« 100 4 R45 241% 45 44%, 225 

32 56232 56332 138.00 100 4 R48 2414 48 44%, 240 

36 56236 56336 160.00 200 4d R54 9414 5A 414%, 270 
40 56240 56340 172.00 200 Am RO7e Ate 57 4d 285 
44 56244 56344 192.00 200 4 R60 2414 60 4% 305 
48 56248 56348 204.00 200 ABO ROS eee 4tce6S 44%, 325 
52 56252 56352 216.00 200 A R66 2414 66 44% 345 
56 56256 56356 228.00 200 4 R69 241%, 69 4%, 365 
60 56260 56360 240.00 200 AU ER7Z2aN 24iG2 72 Le SIs 

PANELS WITH FUSELESS MAIN KNIFE SWITCH 

4 56404 56504 $64.00 30 ROT eT 41 35 

8 56408 56508 81.00 60 Th (eRe SGI BES 4% 150 

12 56412 56512 93.00 60 A R266 24°, eS 4B 165 

16 56416 56516 118.00 100 Ae RAD 943208 aD 4% 195 
20 56420 56520 130.00 100 Ae R45 41 AS Ate 1 0) 
24 56424 56524 142.00 100 4 R48 241%, 48 AZ 095 
28 56428 56528 154.00 100 A= R51. 24% 51 41%, . 240 de 
32 56432 56532 174.00 100 4 R54 241% 54 416 2955 te 
36 56436 56536 207.00 200 Ae oEROOUeED4e G0 4% 290 > 
40 56440 56540 221.00 200 Ae R63 er 2417 wee} 416° 310 = 
44 56444 56544 233.00 200 Aw ©R6G 10414 6G An 330) = 
48 56448 56548 245.00 200 4 R69 241, 69 4% 350 

52 56452 «56552 257.00 =. 200 AeR 7nd ee 72 41 370 

56 56456 56556 271.00 200 He fewisll ee lls 41%, 390 ila 
60 56460 56560 287.00 200 4 R78 241% 78 4% 410 With Fuseless Main Knife 

PANELS WITH FUSIBLE MAIN KNIFE SWITCH 

4 56604 56704 $64.00 30 4 R27 2436 27 Aeros 

8 56608 56708 81.00 60 4 R33. 24% 88 41% 150 

12 56612 56712 93.00 60 4 R86" 2414 36 4% 165 

16 56616 56716 118.00 100 4 R42 24% 49 4144 195 

20 56620 56720 130.00 100 7 rn - 7. y ©) 1 44, 210 

24 56624 56724 142.00 100 4 R48 24% £48 44%, 225 

28 56628 56728 154.00 100 Ty GT OE, A 41%, 240 |. 

32 56632 56732 174.00 100 4 R54 24% 54 41%, 255 cm 

36 56636 56736 207.00 200 4  V60 24% °&60 5% 290 “o> 

40 56640 56740 221.00 200 4 V63 2414 3 5Y% 310 pe 

44 56644 56744 233.00 200 4  V66 2414 66 Ba 330 ob 

48 56648 56748 245.00 200 4  V69 24144 69 5Y 350 

52 56652 56752 257.00 200 See 72) od eT 51% 370 

56 56656 56756 271.00 200 AEN 75 a 41g 5144, 390 ave 
60 56660 56760 987.00 900) 4 V78 2414 78 5Y, 410 With Fusible Main Knife 


Switch. 


iw) 
On 


DENTAMIN:ECTARRE 
“ —— BENJAMIN-STARRETT Ds 
3 Wire Mains Type NOPK OpenFront Panels with Cabinets 
1 Fuse Branches Branches: 2 Wire, 30 Amp. 125 V. Knife Switches, Plug Fuses. 
Mains: 125-250 Volt. 
SINGLE DOOR No. List | Capacity [Gutter ] 4, |_Box Dimensions in Inches | Shipping 
f f Mains | S ; Weigh 


PANELS WITH MAIN LUGS ONLY 


4 56804 56904 $40.00 30 R18 24% 18 4% 85 
8 56808 56908 50.00 60 R21 24% 21 4%, 100 
12 56812 56912 60.00 60 R24 24% 24 4M 115 
16 56816 56916 72.00 100 R27 24% 27 4% 130 


20 56820 56920 84.00 100 R30 24% 30 4% 145 
24 56824 56924 94.00 100 R33 24% 33 4% 160 
28 56828 56928 104.00 100 R36 24% 36 4% 175 
32 56832 56932 114.00 100 24% 39 4% 185 


36 56836 56936 134.00 200 R42 24% 42 4% 200 
40 56840 56940 148.00 200 R45 24% 45 4% 215 
44 56844 56944 162.00 200 R48 24% 48 4% 225 
48 56848 56948 176.00 200 R51 24% 51 4% 240 


52 56852 56952 190.00 200 R54 24% 54 4% 255 
56 56856 56956 204.00 200 R57 24% 57 4% 270 
With Main Lugs Only. 60 56860 56960 218.00 200 R60 24% 60 4% 285 


ALL PLAL PLE PPP 
a 
oo 
© 


PANELS WITH FUSIBLE MAINS 


4 57004 57104 $46.00 30 R21 24% 21 44% 100 
8 57008 57108 58.00 60 R24 24% 24 4% 115 
42 DAVIE DIAN 68.00 60 R27 24% 27 4%, 130 
16 57016 57116 82.00 100 R36 24% 36 4% 175 


20 57020 857120 94.00 100 R39 2414 39 44%, 190 
24 57024 57124 114.00 100 R42 24% 42 4%, 200 
28 57028 57128 126.00 100 R45 24% 45 4% 215 
32 57032 57132 138.00 100 24% 48 4% 225 


36 57036 57136 158.00 200 
40 57040 57140 172.00 200 
44 57044 57144 186.00 200 
48 57048 57148 200.00 200 


52 57052 57152 214.00 200 
56 57056 57156 228.00 200 
60 57060 57160 242.00 200 


PEL LALA PALE PREP 
8) 
mS 
jee) 


PANELS WITH FUSELESS MAIN KNIFE SWITCH 


4 57204 57304 $55.00 309 4 R27 24 eet 4% 115 

8 57208 57308 65.00 Aimee Week Re Be 4% 145 

12 57212 «457312 «75.00 601 Ae 3608 24 tee 41% 160 

16 57216 57316 90.00 100 4 R42 24% 42 4% 190 

20 57220 57320 102.00 100 4 R45 24% 45 4% 205 

24 57224 57324 126.00 100 Aes RAS ed tee 8 4% 995 

28 57228 57328 138.00 100 Loe RSs eT 4% 240 

82 57232) 957332" 150.00. 100 4) R54 924i2ge 4 et 

36 57236 57336 188.00 200 4 R60 24% 60 41% 285 

40 57240 57340 202.00 200 4 R63 24% °& £63 4% 305 

44 57244 57344 216.00 200 4 R66 241% 66 4% 320 

48 57248 57348 230.00 200 4 R69 24% 69 41%, 340 

52 57252 57352 244.00 200 Aa R72 od ee TD 4144 360 

“ a 56 57256 57356 258.00 200 Sa 75s TS 4% 380 
With pes Mai nie 60 57260 57360 272.00 200 dee R724 34 ee TS 41%, 400 


PANELS WITH FUSIBLE MAIN KNIFE SWITCH 


4 57404 57504 $55.00 30 4 R27 241% PAT 4% 115 
8 57408 57508 65.00 60 4 R33 24% 33 41% 145 
12 57412 57512 75.00 60 4 R36 241% 36 4% 160 
16 57416 57516 90.00 100 4 R42 24% 42 4% 190 
20 57420 57520 102.00 100 4 R45 241% 45 4% 205 
24 57424 57524 126.00 100 4 R48 24% 48 4% 225 
28 57428 57528 138.00 100 4 R51 241% 51 4% 240 
32 57432 57532 150.00 100 4 R54 241% 54 4% 255 
36 57436 57536 188.00 200 4 v60 241% 60 5, 285 
40 57440 57540 202.00 200 4 V63 241% 63 54 305 
44 57444 57544 216.00 200 4 V66 241% 66 5% 320 
48 57448 57548 230.00 200 4 V69 24% 69 54% 340 
52 57452 57552 244.00 200 4 V72 24% 72 54 360 
56 57456 57556 258.00 200 4 V75 2414 75 ERA 380 
With Fusible Main Knife 60 57460 57560 272.00 200 4 V78 241% 78 5% 400 
Switch. 
ime) py 


26 


BENJAMIN-STARRETT 
Type NOCK OpenFront Panels with Cabinets — 3 wire mains 


Branches: 2 Wire, 30 Amp. 125 V. Knife Switches, Cartridge Fuses. 1 Fuse Branches 


Mains: 125-250 Volt. 
| Panel with Cabinet | with Cabinet List Capacity | Gutter Box Dimensions in Inches 
Cat.No. Cat. No. Amps. | Inches Outside | Outside | Inside 


PANELS WITH MAIN LUGS ONLY 


c) 


Shipping SINGLE DOOR 
ae : 
Birds CABINETS 


4 57604 57704 $40.00 30 4 RIS odie 218 44 85 

8 57608 57708 50.00 60 4 R21 24% 21 4% 100 

12 57612 57712 60.00 60) seed RO4men O11 eed Aes 1115 

16 57616 57716 72.00 100 4. R27 24% 27 4% 130 

20 57620 57720 8400 100 4 R30 24% 30 4% 145 

24 57624 57724 94.00 100 4. R33) 2446 38 4% 160 as 
28 57628 57728 104.00 100 4) R386) 244, 9 36 4% 175 = 
32 57632 57732 114.00 100 4 R39 24% #239 £41% 185 = 
36 57636 57736 134.00 200 4 R42 24% 42 4% 200 . 
40 57640 57740 148.00 200 4 R459 0241609 45 odie 15 5 
44 57644 57744 162.00 200 4 R48 241% 48 41%, 99 ‘<> 
48 57648 57748 176.00 200 4 #=RS51 24% 51 4% 240 | 
52 57652 57752 190.00 200 4 R54 94% 54 4% 255 

56 57656 57756 204.00 200 AR 5 74 eT 4%, 270 . ' 
60 57660 57760 218.00 200 Awe R6O eo 4 4c 41%, 285 With Main Lugs Only. 

PANELS WITH FUSIBLE MAINS 

4 57804 57904 $46.00 30 dee R21 ed 4% 100 

8 57808 57908 58.00 60 4 RO4e 243; eee od Teva Gilt 

12 57812 57912 68.00 60 AUR OT, eds 7 41%, 130 

16 57816 57916 82.00 100 AL R360 0425 8G 4466 2175 
20 57820 57920 94.00 ~=100 Ae R394 129 4% 190 
24 57824 57924 114.00 100 mo qevby “Sy Wy, 4%, 200 
28 57828 57928 126.00 100 4 R45 241% 45 4% 215 
32 57832 57932 138.00 100 4 R48 2414 48 4% 295 
36 57836 57936 158.00 200 4 R54 24% 54 4% 255 

40 57840 57940 172.00 200 YAN, OTR ie 4% 270 

44 57844 57944 186.00 200 AMER GON) 2422 ar C0 ede O85 

48 57848 57948 200.00 200 45 R630) 2414 63 Air 305 

52 57852 57952 214.00 200 4 R66 24% £66 vie EER s 

56 57856 57956 228.00 200 4 R69 24% 69 4% 345 

60 57860 57960 242.00 200 4 R72 4 72 4% 360 


PANELS WITH FUSELESS MAIN KNIFE SWITCH 


4 58004 58104 $55.00 30 4 R27 24% 27 4% 115 

8 58008 58108 65.00 60 4 R33 24% 33 4% 145 

12 58012 58112 75.00 60 4 R36 24% 36 4% 160 

16 58016 58116 90.00 100 4 R42 24% 42 4% 190 

20 58020 58120 10200 100 4 R45 24% 45 4% 205 

24 58024 58124 126.00 100 4 R48 24% 48 4% 225 

28 58028 58128 138.00 100 4 R51 24% 51 4% 240 

32 58032 58132 150.00 100 4 R54 24% 54 4% 255 

36 58036 58136 188.00 200 4 R60 24% 60 4% 285 

40 58040 58140 202.00 200 4 R63 24% 63 4% 305 

44 58044 58144 216.00 200 4 R66 24% 66 4% 320 

48 58048 58148 230.00 200 4 R69 24% 69 4% 340 

52 58052 58152 24400 200 4 R72 24% 72 4% 360 

56 58056 58156 25800 200 4 R75 24% 175 4% 380 : My 
COMED S000NN 5316090272 00. 200 45 0 R78 24%, 78. 841, 400%, With Buseless Main Knife 


PANELS WITH FUSIBLE MAIN KNIFE SWITCH 


4 58204 58304 $55.00 30 4 R27 24% 27 4% 115 

8 58208 58308 65.00 60 4 R33 24% 33 4% 145 
12 58212 58312 75.00 60 4 R36 24% 36 4% 160 
16 58216 58316 90.00 100 4 R42 24% 42 4% 190 
20 58220 58320 102.00 100 4 R45 24% 45 4% 205 
24 58224 58324 12600 100 4 R48 241% 48 4% 225 
28 58228 58328 13800 100 4 R51 24% 51 4% 240 
32 58232 58332 150.00 100 4 R54 24% 54 4% 255 
36 58236 58336 188.00 200 4 V60 24% 60 5% 285 
40 58240 58340 202.00 200 4 V63 24% 63 5% 305 
44 58244 58344 216.00 200 4 V66 24% 66 5% 320 
48 58248 58348 230.00 200 4 V69 24% 69 5% 340 
52 58252 58352 24400 200 4 Vv72 24% 72 5% 360 
56 58256 «58356 25800 200 4 V75 24% 75 5% 380 
60 58260 58360 27200 200 4 V78 24% 78 5% 400 With Fusible Main Knife 


Sr 


BENJA 


SECTION III 
Two-Fuse Panelboards With Cabinets 


Each two fuse panel is equipped with Edison plug fuse receptacles or cartridge fuse clips in both 


sides of the branch circuit. Where switches are shown they are double pole. 


cations, see pages 4, 5, 6 and 7. 


|® 
eo 
@) 
(D>. 
(>) 
@i 
|® 
(> 
©, 
(> 
(o> 
(| 


SAFETY FRONT TYPE 


Open Front Type 


Single Door Cabinet 


The open front panel has a single door 
which gives access to all switches, fuses 
and connections on the face of the panel. 
Because of the open front construction this 
type is suitable for use only where operation 
of switches and replacement of fuses is 
made by some experienced person. The 
door is equipped with a combination Yale 
spring latch and lock which prevents 
unauthorized tampering. 

All cabinets are furnished with a 


circuit directory card mounted in a 
metal frame—see illustration. 


TeaReeeeeegee 


For general specifi- 


Safety Front Type 
Door-In-A-Door Cabinet 


This safety type panel is of double-door 
construction—one smaller door within a 
larger one. Opening of the small door 
gives access to the switches of the branch 
circuits only, while opening of the large 
door exposes the full face of the panel. 


This safety panel is intended for installa- 
tions where branch switches are operated 
by inexperienced persons and fuses renewed 
by a maintenance man. ‘The large door 
is provided with a Yale combination 
spring latch and lock, which effectively 
prevents over fusing by an inexperienced 
person, tampering with the main or branch 
connections, and theft of fuses. 


All cabinets are equipped with a 
circuit directory card mounted in a 
metal frame—see illustration. 


": 


BAPE Ee 


o 


OPEN FRONT TYPE 


28 


SECTION III 


Two-Fuse Panelboards With Cabinets 


Protective Front Type 


Single Door Cabinet 


This panel differs from the standard 
safety panel only in that it is furnished 
with a single door trim. 


The cabinets for panels with Fusible 
Main Knife Switches have two doors, one 
exposing the knife switch, the other giv- 
ing access to branch circuit switches and 
fuses. Both doors are equipped with a 
Yale combination spring latch and lock. 


Panels with Fusible Mains have a small 
door in the protective shield, giving access 
to the main fuses. 


All cabinets are equipped with a cir- 
cuit directory card mounted in a metal 
directory frame—see illustration. 


PROTECTIVE FRONT TYPE 


Index to Section III 


2-Fuse—Safety Front Type 


Ce mat TULeT aS OI LCRES: OTTONGED 1.01 DULG J USES. 6... ae». eee Pages 50-31 
hipe sC L  Tumbler Switches arranged for cartridge fuses............-. Pages 32-33 


2-Fuse—Protective Front Type 


i npaxe Iba ee PAVE IL COR) Ole DULG MALS CSL OU ae ee Sach 6 es, Fee Pages 34-35 
Ti Deelnie mee, UMOLETMSLUULChes: QTTANGeG {OL DLULG FUSES 4. tea. es ee Pages 56-37 


2-Fuse—Open Front Type 


Type OC PATERCLIIG COM ONEGO LUTE Cul ULSCSLOTLL) Sane Stee te re ee Pages 88-39 
Tipe OC Ts] umblerisuniches arranged for cartridge fuses... ...... 7... Pages 40-41 
ETCH Lemme CP UPL CILESECLET ONGCOS LOT APUG USCS. tana. taake ae nee Pages 42-43 
Ta G Koma Coo BUC es Orr angeo. [ON COTW Ge Juss... anaes er Pages 44-45 
a De 


29 


2Wire Mains ‘Type SPT Safety Panels with Cabinets 


2 Fuse Branches Branches: 2 Wire, 30 Amp. 250 V. HEAVY DUTY Tumbler Switches, 
Plug Fuses. Mains: 125 Volt. 


Panel with | Panel with Cabinet _| List Capacity Gutter Box Dimensions in Inches 
Cat.No. Cat. No. Amps. | Inches Outside | Outside | Inside 


PANELS WITH MAIN LUGS ONLY 


Shipping 
Weight 
Pounds 


DOOR IN A DOOR 
CABINETS 


4 90004 90054 $62.00 60 R21 241% 21 % 105 
6 90006 90056 68.00 100 R24 24% 24 % 120 
8 90008 90058 78.00 100 R27 24% 27 Y% 135 
10 90010 90060 88.00 100 R30 24% 30 Y% 150 


12 90012 90062 98.00 200 


14 90014 90064 110.00 200 R36 24% 36 


Le ee ool 
tte be 
i 
ee) 
i) 


4 
4 
4 
4 
R33 24% 33 4 
4 
4 
4 
4 
4 


16 90016 90066 120.00 200 R39 24% 39 6 195 
18 90018 90068 130.00 200 R42 24% 42 Y% 210 
20 90020 90070 = 140.00 200 R45 24% 45 Ye 225 
22 90022 § 90072) 150.00 200 R48 24% 48 


24 90024 90074 160.00 200 
26 90026 90076 176.00 200 


28 90028 90078 186.00 200 
30 90030 90080 200.00 200 
32 90032 90082 216.00 200 


LPP PPE LP PPE PPP 


PANELS WITH FUSIBLE MAINS 


4 90104 90154 $74.00 60 R24 24% 24 4%, 120 
6 90106 90156 86.00 100 R33 24% 33 4% 165 
8 90108 90158 96.00 100 R36 24% 36 4% 180 
10 90110 90160 106.00 100 R39 24% 39 4% 195 


12 90112 90162 126.00 200 R45 24% 45 4% 225 
14 90114 90164 136.00 200 R48 24% 48 4%, 240 
16 90116 90166 146.00 200 R51 24% 51 4145 255 
18 90118 90168 156.00 200 24% b4 4% 270 


20 90120 90170 166.00 200 R57. 24% 57 4% 285 
22 90122 90172 186.00 200 R60 24% 60 44% 305 
24 90124 90174 196.00 200 R63 24% 63 4% 325 
26 90126 90176 206.00 200 R66 24% 66 4% 345 


28 90128 90178 216.00 200 R69 24% 69 4% 365 
30 90130 90180 226.00 200 R72. 24% 72 41%6 385 
32 90132 90182 236.00 200 R75 24% 75 4%, 405 


PPL PALL PELL PPPH 
Bs) 
o 
TS 


With Fusible Mains. 


PANELS WITH FUSIBLE MAIN BRUSH TYPE SWITCH 


4 90204 90254 $88.00 60 R33 24% 33 4%, 150 
6 90206 90256 108.00 100 R39 24% 39 4% 180 
8 90208 90258 118.00 100 R42 241% 42 4%, 195 
10 90210 90260 128.00 100 R45 24% 45 4% 210 


12 90212 90262 160.00 200 
14 90214 90264 170.00 200 
16 90216 90266 190.00 200 
18 90218 90268 200.00 200 


20 90220 90270 210.00 200 
22 90222 90272 220.00 200 
24 90224 90274 230.00 200 
26 90226 90276 246.00 200 


28 90228 90278 260.00 200 

30 90230 90280 276.00 200 

With Fusible Main Brush 32 90232 90282 290.00 200 
Type Switch. 


LAL PPP AREPL PPPS 
< 
fon) 
°o 
bo 
es 
i 
for) 
= 
on 
Nd 
pS 
bo 
ra) 
On 


PANELS WITH FUSIBLE MAIN KNIFE SWITCH 


4 90304 90354 $85.00 60 R33 24% 33 4%, 150 
6 90306 90356 106.00 100 R39 241% 39 4% 180 
8 90308 90358 116.00 100 R42 24% 42 416 195 
10 90310 90360 126.00 100 R45 24% 45 4% 210 


12 90312 90362 157.00 200 v51 241% 51 5% 245 
14 90314 90364 167.00 200 V54 24% 54 5% 260 
16 90316 90366 187.00 200 V57 24% 57 5% 275 
18 90318 90368 197.00 200 24% 60 5% 86295 


20 90320 90370 207.00 200 V63 24% 63 5% 315 
22 90322 90372 217.00 200 V66 24% 66 54 335 
24 90324 90374 227.00 200 V69 24% 69 54 355 
26 90326 90376 243.00 200 V72 24% 72 5% 8603875 


28 90328 90378 257.00 200 V75 24% 75 514 395 
30 90330 90380 273.00 200 V78 24% 78 54 415 
32 90332 90382 287.00 200 Vv81 24% 81 5% 435 


Lp ALLL PREP PRR 
< 
a 
oO 


With Fusible Main Knife See ee EE 
Switch. Panels with Unfused Main Switches can be furnished at same prices as Panels with 
Fusible Main Switches. 


& 


Type SPT Safety Panels with Cabinets 3 Wire Mains 


Branches: 2 Wire, 30 Amp. 250 V. HEAVY DUTY Tumbler Switches, 2 Fuse Branches 
Plug Fuses. Mains: 125-250 Volt. 


Panel with |__ Panel with Cabinet _ | List Capacity Gutter Box Dimensions in Inches 
Cat.No. | Cat. No. Amps. _| Inches Outside | Outside | Inside 


PANELS WITH MAIN LUGS ONLY 


No. 


Shipping 
Weight 
Pounds 


DOOR IN A DOOR 
CABINETS 


4 90404 90454 $58.00 30 1 R21 24% 21 4% 105 
6 90406 90456 68.00 60 4 R24 24% 24 4% 120 
8 90408 90458 78.00 60 4 R27 24% 27 4, 135 
10 90410 90460 88.00 60 4 R30 24% 30 4% 150 
12 90412 90462 98.00 60 4 R33 24% 33 4% 165 
14 90414 90464 106.00 100 4 R36 24% 36 4% 180 
16 90416 90466 116.00 100 4 R39 241% 39 4% 195 
18 90418 90468 126.00 100 4 R42 24% 42 4%, 210 
20 90420 90470 = 140.00 100 4 R45 241% 45 4% 225 
22 90422 90472 8150.00 100 1 R48 24% 48 41% 240 
24 90424 90474 160.00 100 4 R51 24% 51 414 255 
26 90426 90476 170.00 100 4 R54 24% 54 44%, 270 
28 90428 90478 180.00 100 4 R57 2416 57 4% 285 
30 90430 90480 190.00 100 d R60 24% 60 4% 305 
32 90432 90482 206.00 100 4 R63 24% 63 4% 325 
PANELS WITH FUSIBLE MAINS 

4 90804 90854 $68.00 30 4 R24 24% 24 4%, 120 
6 90806 90856 78.00 60 4 R27 24% 27 4% 135 
8 90808 90858 88.00 60 + R30 24% 30 4%, 150 
10 90810 90860 98.00 60 4 R33 24% 33 4% 165 
12 90812 90862 108.00 60 4 R36 24% 36 41%, 180 
14 90814 90864 128.00 100 4 R45 24% 45 44%, 225 
16 90816 90866 138.00 100 4 R48 24% 48 4% 240 
18 90818 90868 148.00 100 4 R51 241% 51 4% 255 
20 90820 90870 158.00 100 4 R54 24% 54 AY 270 
ae 90822 90872 8 168.00 100 4 R57 24% 57 416 285 
24 90824 90874 178.00 100 4 R60 24% 60 4% 305 
26 90826 90876 192.00 100 4 R63 24% 63 4% 325 
28 90828 90878 202.00 100 4 R66 241% 66 4% 345 
30 90830 90880 212.00 100 4 R69 2414 69 4% 365 
32 90832 90882 222.00 100 4 R72 24% 72 4% 385 


PANELS WITH FUSIBLE MAIN BRUSH TYPE SWITCH 


4 90904 90954 $86.00 30 4 R33 24% 33 4% 150 
6 90906 90956 96.00 60 4 R36 24% 36 4% 165 
8 90908 90958 106.00 60 4 R39 24% 39 4% 180 
10 90910 90960 116.00 60 4 R42 24% 42 4% 195 
12 90912 90962 126.00 60 4 R45 241% 45 4% 210 
14 90914 90964 150.00 100 4 R51 24% 51 4% 240 
16 90916 90966 160.00 100 4 R54 24% 54 4% 255 
18 90918 90968 180.00 100 4 R57 24% 57 4% 270 
20 90920 90970 190.00 100 4 R60 24% 60 4% 290 
22 90922 90972 200.00 100 4 R63 24% 63 4% 310 
24 90924 90974 210.00 100 4 R66 24% 66 4% 330 
26 90926 90976 220.00 100 4 R69 24% 69 4% 350 
28 90928 90978 230.00 100 4 R72 241% 2 4% 370 
30 90930 90980 240.00 100 4 R75 24% 75 4% 390 
32 90932 90982 250.00 100 4 R78 24% 78 4% 410 With Fusible Main Brush 


Type Switch. 
PANELS WITH FUSIBLE MAIN KNIFE SWITCH 


4 91004 91054 $82.00 30 4 R30 24% 30 4% 150 

6 91006 91056 93.00 60 4 R36 24% 36 4% 165 

8 91008 91058 103.00 60 4 R39 241% 39 4% 180 
10 91010 91060 113.00 60 4 R42 24% 42 4% 195 
12 91012 91062 123.00 60 4 R45 24% 45 4% 210 
14 91014 91064 148.00 100 4 R51 24% 51 4% 240 
16 91016 91066 158.00 100 4 R54 241% 54 4% 255 
18 91018 91068 178.00 100 4 R57 24% 57 AY 270 
20 91020 91070 188.00 100 4 R60 24% 60 4%, 290 
22 91022 91072 198.00 100 4 R63 24% 63 4% 310 
24 91024 91074 208.00 100 1 R66 24% 66 4% 330 
26 91026 91076 218.00 100 4 R69 24% 69 4% 350 
28 91028 91078 228.00 100 4 R72 24% 72 4% 370 
30 91030 91080 238.00 100 4 R75 24% 75 4% 390 
32 91032 91082 248.00 100 4 R78 24% 78 4% 410 


- - With Fusible Main Knife 
Panels with Unfused Main Switches can be furnished at same prices as Panels with Switch. 


Fusible Main Switches. 


31 


2Wire Mains Type SCT Safety Panels with Cabinets 


2 Fuse Branches Branches: 2 Wire, 30 Amp. 250 V. HEAVY DUTY Tumbler Switches, 
Cartridge Fuses. Mains: 125 Volt. 


DOOR IN A DOOR No. Panel with Cabinet List Capacity | Gutter Box Box Dimensions in Inches Shipping 
INETS of Surface Flush Price of Mains | Space No Wide High Deep | Weight 
CAB : Cat.No. Cat. No. Amps. | Inches * | Outside | Outside | Inside | Pounds 


PANELS WITH MAIN LUGS ONLY 


4 91104 91154 $62.00 60 4 R21 24% 21 4% 105 
6 91106 91156 68.00 100 4 R24 24% 24 4% 120 
8 91108 91158 78.00 100 R27. 24% 27 4% 135 
10 91110 91160 88.00 100 R30 24% 30 4% 150 


12 91112 91162 98.00 200 R33 24% 33 4% 165 
14 91114 91164 110.00 200 R36 24% 36 4%, 180 
16 91116 91166 120.00 200 R39 24% 39 4% 195 
18 91118 91168 130.00 200 R42 24% 42 4% 210 


20 91120 91170 140.00 200 24% 45 41h 225 
ee 91122 91172 150.00 200 R48 24% 48 44% 240 
24 91124 91174 160.00 200 R51 24% 51 4% 255 
26 Oi 2 CeO 7 Ommmelario nO) 200 R54 24% 54 4%, 270 


28 91128) 91178) 186.00 200 R57 2416 57 4% 285 
30 91130 91180 200.00 200 R60 24% 60 4% 305 
32 91132 91182 216.00 200 R63 24% 63 4% 325 


LAL PALL APAR BR 
Bs) 
as 
oa 


PANELS WITH FUSIBLE MAINS 


4 91204 91254 $74.00 60 
6 91206 91256 86.00 100 
8 91208 91258 96.00 100 
10 91210 91260 106.00 100 


12 91212 91262 126.00 200 
14 91214 91264 136.00 200 
16 91216 91266 146.00 200 
18 91218 91268 156.00 200 


20 91220 pei 27.0 6.6.00) 200 
22 C1222 Cm OL U0) 200 
24 91224 91274 196.00 200 
26 91226 91276 206.00 200 


28 91228 127 Se 26.00 200 
30 91230 91280 226.00 200 
32 912382 91282 236.00 200 


TELELLELLLLLL 
PTEeee tiie tT 


eee 


PPE PEEL SEE PPE 
2) 
o1o 
os 
bo 
ine 
BS 
oO 
rs 
Ne 
= 
BS 
bo 
J 
(==) 


With Fusible Mains. 
PANELS WITH FUSIBLE MAIN BRUSH TYPE SWITCH 


4 91304 91354 $88.00 60 R33 24% 33 4%, 150 
6 91306 91356 108.00 100 R39 241% 39 4%, 180 
8 91308 91358 118.00 100 R42 24% 42 4% 195 
10 91310 91360 128.00 100 R45 24% 45 4% 210 


12 91312 91362 160.00 200 v51 241% 51 5% 8245 
14 91314 91364 170.00 200 V54 24% 54 54% 260 
16 91316 91366 190.00 200 V57 2414 57 5% ©6275 
18 91318 91368 200.00 200 


20 91320 91370 210.00 200 
22 91322 91372 220.00 200 
24 91324 91374 230.00 200 
26 91326 91376 246.00 200 


28 91328 91378 260.00 200 

30 91330 91380 276.00 200 

With Fusible Main Brush 32 91332 91382 290.00 200 
Type Switch. 


mee PPE PEEP PRE 
< 
fo>) 
[o) 
bo 
rg 
= 
by 
[op) 
Oo 
oO 
nS 
bo 
oo 
oO 


PANELS WITH FUSIBLE MAIN KNIFE SWITCH 


4 91404 91454 $85.00 60 4 R33 24% 33 414%, 150 

6 91406 91456 106.00 100 4 R39 24% 39 4% 180 

8 91408 91458 116.00 100 4 R42 24% 42 4% 195 

10 91410 91460 126.00 100 4 R45 24% 45 4% 210 

12 91412 91462 157.00 200 4 V51 241% 51 54% 86245 

14 91414 91464 167.00 200 4 V54 824% 54 54 260 

16 91416 91466 187.00 200 4 V57 24% 57 5% «275 

18 91418 91468 197.00 200° 4 V60 24% 60 5% 86295 
a2 & 

ia & 20 91420 91470 207.00 200 4 V63 24% 63 54% 315 

pd 22 91422 91472 217.00 200 4 V66 24% 66 5%4 335 

pas 24 91424 91474 227.00 200 4 V69 24% 69 5% 355 

$2 > 26 91426 91476 243.00 200 4 V72 «24% 72 5% 375 

28 91428 91478 257.00 200 4 V75 24% 75 54% 395 

30 91430 91480 273.00 200 4 V78 24% 78 51%, 415 

32 91432 91482 287.00 200 4 V81 24% 81 5% 435 


With Fusible Main Knife EE RE SSE RE Sean ES RTT EY SRN NERS SOE HEEB PAWS cr, 5g 
Switch. Panels with Unfused Main Switches can be furnished at same prices as Panels with 
Fusible Main Switches. 


Type SCT Safety Panels with Cabinets 3 Wire Mains 


Branches: 2 Wire, 30 Amp. 250 V. HEAVY DUTY Tumbler Switches, 2 Fuse Branches 
Cartridge Fuses. Mains: 125-250 Volt. 


Panel with Cabinet - Capacity | Gutter Box Dimensions in Inches 
List € Mai S$ Box 
Price of Mains | Space No 
Amps. | Inches s 


Surface Flush Wide High 
Cat.No. Cat. No. Inside 


Outside | Outside 
PANELS WITH MAIN LUGS ONLY 


Shipping DOOR IN A DOOR 
Weight 


Pounds CABINETS 


4 91804 91854 $58.00 SOM R210 od ife O19 Aken 108 
6 91806 91856 68.00 60 4 R24 24% 24 4% 120 
8 91808 91858 78.00 GU. RO 7am od 18 7 nt ee a pape 
10 91810 91860 88.00 60 4 R30 24% 30 4% 150 = > 
12 91812 91862 98.00 GUimee4 ee RSS | 24125 | 381) dices G5 t= >L 
14 91814 91864 106.00 100 4 R386 24% 36 4% 180 -* 
16 91816 91866 116.00 100 4 R39 24% 39 4% 195 Joa 2 
18 91818 91868 126.00 100 4 R42 24% 42 4% 210 <> 
20 91820 91870 140.00 100 4 R45 24% 45 4% 295 = 
22 91822 91872 150.00 100 4 R48 24% 48 41% 240 are =| 
24 91894 91874 160.00 100 4 R51 24% 51 4% 255 Toe 
26 91826 91876 170.00 100 4 R54 24% 54 4% 270 - : 
28 91828 91878 180.00 100 4 R57 24% 57 44% 285 
30 91830 91880 190.00 100 4 R60 24% 60 4% 305 
6201022) 891899 a 1c OOM LU0MEEE4 RESUS 2434" = 63") 416" 0395 
PANELS WITH FUSIBLE MAINS 
4 91904 91954 $68.00 BOMMETEER 4M 249, 2 24) 044g 100 
6 91906 91956 78.00 COME ANI R27, 24358 OT. 416) 195 
8 91908 91958 88.00 COME eer R 20 er 24 16m 30) 9 6416 150 
10 91910 91960 98.00 607) 4.9 R33 2416 «83846165 
12 91912 91962 108.00 60m er4eme R36. 24325 36) 9 4125 180 
34g 191400 919640 128.008 100) 408 R455 2941409 45 ta, 005 
16 91916 91966 13800 100 4 R48 24% 48 41% 240 
fnme9 1919991068. 14800 1 00MmNE4ueE R51IN 241600 Fle . 4167 255 
20 91920 91970 158.00 100 4 R54 24% 54 4% 270 
22°).91922 91972 168.00 100 4 R57 24% 57 4% 285 
949101924 91974 178.00 100. 4 R60 241% 60 © 4% 305 
26 91926 91976 192.00 100 4 R63 24% 63 4% 325 
28 91928 91978 202.00 100 4 R66 24% 66 4% 345 
800 -91980 — 91980 212.00. 100 4 R69 24%. 69 4% 365 
50m 0108200 1919092819 222,00e 100) aad emeR72 682444. 72 «8446 «8385 


PANELS WITH FUSIBLE MAIN BRUSH TYPE SWITCH 


4 92004 92054 $86.00 30 4 R33 241% 3 4% 150 

6 92006 92056 96.00 60 4 R36 24% 36 4% 165 

8 92008 92058 106.00 60 4 R39 24% a) 4% 180 
10 92010 92060 116.00 60 + R42 24% 42 4% 195 
12 92012 92062 126.00 60 4 R45 241% 45 41%, 210 
14 92014 92064 150.00 100 4 R51 241% 51 4% 240 
16 92016 92066 160.00 100 a R54 241% 54 4% 255 
18 92018 92068 180.00 100 4 R57 241% yf 4% 270 
20 92020 92070 190.00 100 4 R60 24% 60 4% 290 
22 92022 92072 200.00 100 4 R63 24% 63 4% 310 
24 92024 92074 210.00 100 4 R66 24% 66 4% 330 
26 92026 92076 220.00 100 4 R69 24% 69 4% 350 
28 92028 92078 230.00 100 4 R72 241% 7 4% 370 p 
30 92030 92080 240.00 100 4 R75 241% u 4%, 390 
32 92032 92082 250.00 100 4 R78 24% 78 4% 410 With Fusible Main Brush 

Type Switch. 
PANELS WITH FUSIBLE MAIN KNIFE SWITCH 

4 92104 92154 $82.00 30 4 R30 241% 30 4% 150 

6 92106 92156 93.00 60 4 R36 241% 36 4% 165 

8 92108 92158 103.00 60 + R39 241% 39 4% 180 
10 92110 92160 113.00 60 4 R42 24% 42 4% 195 
12 92112 92162 123.00 60 4 R45 241% 45 4% 210 
14 92114 92164 148.00 100 4 R51 24% 51 4% 240 
16 92116 92166 158.00 100 4 R54 24% 54 4% Zoo 
18 92118 92168 178.00 100 a R57 2416 57 4% 270 
20 92120 92170 188.00 100 4 R60 2414 60 4%, 290 
22 92122 92172 198.00 100 4 R63 241% 63 4% 310 
24 92124 92174 208.00 100 4 R66 24% 66 4% 330 
26 92126 92176 218.00 100 + R69 24% 69 4% 350 
28 92128 92178 228.00 100 4 R72 24% 72 4 370 
30 92130 92180 238.00 100 4 R75 24% OS 4% 390 
32 92132 92182 248.00 100 4 R78 24% 78 4% 410 


ne eennta: apennee erwin ewe cen NT en a ee eee With Pusible Main Knife 
Panels with Unfused Main Switches can be furnished at same prices as Panels with Switch. 


Fusible Main Switches, 


33 


Pa 


& = BENJAMIN STARRETT 
2Wire Mains Type LP Protective Panels with Cabinets 


2 Fuse Branches Branches: 2 Wire, Plug Fuses Only. 


Mains: 125 Volt. 
Box Dimensions in Inches 


Panel with | Panel with Cabinet _| List Capacity | Gutter 
Surface Panel wi Cabinet _] lush Price | fist Space Deep 
Cat.No. Cat. No. Amps. | Inches Outside | Outside | Inside 


PANELS WITH MAIN LUGS ONLY 


Shipping 
Weight 
Pounds 


SINGLE DOOR 
CABINETS 


: 4 92204 92254 $38.00 60 4 R21 24% 21 414 105 
° 8 92208 92258 45.00 100 4 R24 24% 24 4% 120 
: 12 9221 Zum zeod 52.00 200 4 R27 24% 27 4% 135 
: 16 92216 92266 60.00 200 4 R30 24% 30 4% 150 
2 20 92220 92270 70.00 200 t R33 24% 33 41% 165 
° 24 92224 92274 80.00 200 4 R36 241% 36 4% 180 

28 92228 92278 90.00 200 4 R39 24% 39 4s 195 

32 92232 92282 100.00 200 4 R42 24% 42 4% 210 


With Main Lugs Only. 


PANELS WITH FUSIBLE MAINS 


ce : 4 92304 92354 $54.00 60 4 R24 24% 24 4% 120 
8: ; 8 92308 92358 68.00 100 2 R33 24% 33 4% 165 
. 8 12 92312 92362 85.00 200 4 R39 24% 39 4% 195 
: ° 16 92316 92366 95.00 200 4 R42 24 42 4% 210 
Be : 20 92320 92370 105.00. 200 4° R45 24% 945: e4agmumogn 
24 92324 92374 115.00 200 4 R48 24% 48 4% 240 
28 92328 92378 125.00 200 4 R51 24% 51 41% 255 

32 92332 92382 135.00 200 4 R54 24% 54 4% 270 

With Fusible Mains. 
PANELS WITH FUSIBLE MAIN BRUSH TYPE SWITCH 

4 92404 92454 $70.00 60 4 R33 24% 33 4% 1650 

8 92408 92458 80.00 100 4 R39 24% 39 4% 180 

12 92412 92462 120.00 200 4 45 24% 45 5% 210 

16 92416 92466 130.00 200 4 V48 24% 48 5% 225 

20 92420 92470 140.00 200 4 51 24% 51 54% 245 

24 92424 92474 150.00 200 4 54 24% 54 5% 260 

28 92428 92478 160.00 200 4 57 24% 57 5% 275 

32 92432 92482 180.00 200 4 60 24% 60 5% 290 


With Fusible Main Brush 
Type Switch. 


PANELS WITH FUSIBLE MAIN KNIFE SWITCH 


4 92504 92554 $67.00 60 4 R33 24% 33 4% 150 
8 92508 92558 78.00 100 4 R39 24% 39 4% 180 
12 92512 92562 ‘117.00 200 4 Vv45 24% 45 5% 210 
16 92516 92566 127.00 200 + V48 824% 48 51%) =225 
20 9252055) 92570 a 3s7.00 200 4 v51 241% 51 5% 8=6245 
24 92524 92574 147.00 200 4 V54 24% 54 5% 260 
28 92528 92578 157.00 200 4 V57 2414 57 5% 86275 
32 92532 92582 177.00 200 + V60 24% 60 5% 290 


With Fusible Main Knife ee ee 
Switch. Panels with Unfused Main Switches can be furnished at same prices as Panels with 


Fusible Main Switches. 
34 


Type LP Protective Panels withCabinets — 3 Wire Mains 


2 Fuse Branches 


Branches: 2 Wire, Plug Fuses Only. 
Mains: 125-250 Volt. 


No. Panel with Cabinet Te Capacity | Gutter | po, Box Dimensions in Inches Serpette SINGLE DOOR 
0 Surface Flush 5 of Mains | Space Wide High eight 
Price | Amps. | Inches | N° | Outside| Outside | Inside | Pounds CABINETS 


PANELS WITH MAIN LUGS ONLY 


4 92604 92704 $38.00 30 4 R18 24% 18 4% 90 

8 92608 92708 45.00 60 4 R21 24% 21 4% 105 

12 92612 92712 52.00 60 4 R24 24% 24 4% 120 

16 92616 92716 60.00 100 4 R27 24% 27 4% 135 

20 92620 92720 70.00 100 4 R30 24% 30 4% 150 

24 92624 92724 80.00 100 4 R33 24% 33 4% 165 

28 92628 92728 90.00 100 4 R36 24% 36 4% 180 

32 92632 92732 100.00 100 4 R39 24% 39 4% 195 

36 92636 92736 115.00 200 4 R42 24% 42 4% 210 
40 92640 92740 125.00 200 4 R45 24% 45 4% 295 

44 92644 92744 135.00 200 4 R48 24% 48 4% 240 

48 92648 92748 145.00 200 4 RS1 24% 51 41% 255 

52 92652 92752 160.00 200 4 R54 24% 54 4% 270 

56 92656 92756 170.00 200 4 R57 24% 57 416 285 

60 92660 92760 180.00 200 4 R60 24% 60 4% 300 

PANELS WITH FUSIBLE MAINS 

4 92804 92904 $5400 30 4 R21 24% 21 41% 105 

8 92808 92908 62.00 60 4 R24 24% 24 4% 120 = 

12 92812 92912 70.00 60 4 R27 24% 27 4% 135 °@ 
16 92816 92916 85.00 100 4 R36 24% 36 4% 180 °@ 
20 92820 92920 95.00 100 4 R39 24% 39 4% 195 < O@ 
24 92824 92924 105.00 100 4 R42 24% 42 4% 210 oe 
28 92828 92928 115.00 100 4 R45 24% 45 4% 295 3 | 
32 92832 92932 125.00 100 4 R48 24% 48 4% 240 3 i 
36 92836 92936 145.00 200 4 R54 24% 54 4% 270 : 
40 92840 92940 160.00 200 4 R57 24% 57 416 285 8-8 | 
44 92844 92944 170.00 200 4 R60 241% 60 41% 300 
48 92848 92948 180.00 200 4 R63 24% 63 4% 315 
52 92852 92952 190.00 200 4 R66 24% 66 4% 330 

56 92856 92956 200.00 200 4 R69 24% 69 416 345 
60 92860 92960 210.00 200 4 R72 24% 72 4% 360 
PANELS WITH FUSIBLE MAIN BRUSH TYPE SWITCH 

4 93004 93104 $70.00 30 4 R30 24% 30 4% 18 

8 93008 93108 78.00 60 4 R33 24% 33 4% 150 

12 93012 93112 86.00 60 4 R36 24% 36 4% 165 

16 93016 93116 100.00 100 4 R42 24% 42 4% 195 
20 93020 93120 110.00 100 4 R45 24% 45 4% 210 
24 93024 93124 120.00 100. 4 R48 24% 48 41% 295 
28 93028 93128 136.00 100 4 R51 24% 51 416 245 
32 93032 93132 146.00 100 4 R54 24% 54 41% 260 
36 93036 93136 184.00 200 4 V60 24% 60 5% 290 
40 93040 93140 19400 200 4 V63 24% 63 5% 305 
44 93044 93144 204.00 200 4 V66 24% 66 5% 320 
48 93048 93148 21400 200 4 V69 24% 69 5% 335 
52 93052 93152 224.00 200 4 V72 24% 72 5% 350 

56 93056 93156 234.00 200 4 V75 24% 75 5% 365 
0mmmno3060 51192316008 244.008 200g n4 8 V78 82412 578°" 51, 880 eierenmenenasiAlnecah 


Type Switch. 
PANELS WITH FUSIBLE MAIN KNIFE SWITCH 


4 93204 93304 $66.00 30 4 R27 241% 27 4% 120 

8 93208 93308 75.00 60 4 R33 24% 33 4% 150 
12 93212 93312 83.00 60 4 R36 24% 36 4%, 165 
16 93216 93316 98.00 100 4 R42 24% 42 4% 195 
20 93220 93320 108.00 100 4 R45 24% 45 4% 210 
24 93224 93324 118.00 100 4 R48 24% 48 4% 225 
28 93228 93328 134.00 100 4 R51 241% 51 4% 245 
32 93232 93332 144.00 100 4 R54 24% 54 4% 260 
36 93236 93336 181.00 200 4 V60 24% 60 54 290 
40 93240 93340 191.00 200 4 V63 24% 63 5% #305 
44 93244 93344 201.00 200 + V66 24% 66 5% 320 
48 93248 93348 211.00 200 4 V69 24% 69 5% 335 
52 93252 93352 221.00 200 4 V72 241% 72 5% 350 
56 93256 93356 231.00 200 4 V75 241% 75 5 365 
60 93260 93360 241.00 200 4 Vv78 241% 78 5y 380 


With Fusible Main Knife 
Panels with Unfused Main Switches can be furnished at same prices as Panels with Switch. 


Fusible Main Switches. 2 
35 


A 3ENJAMIN STARRETT 
2Wire Mains Type LPT Protective Panels with Cabinets 


2 Fuse Branches Branches: 2 Wire, 30 Amp. 250 V. HEAVY DUTY Tumbler Switches, 
Plug Fuses. Mains: 125 Volt. 


Box Dimensions in Inches 


u n No. Panel with Cabinet Capacity | Gutter Shipping 
SINGLE pas oF Sinface P eush | Lee of Mains peste Wide High Deep | Weight 
CABINETS ir. Cat.No. oe No. Amps. | Inches Outside | Outside | Inside | Pounds 


PANELS WITH MAIN LUGS ONLY 


| 4 93404 93454 $42.00 60 4 R21 24% 21 4% 105 

‘ae ely 6 93406 93456 52.00 100 4 R24 24% 24 4% 120 
Serra 8 93408 93458 62.00 100 4 R27 24% 27 4% 185 
aude 10 93410 93460 72.00 100 4 R30 24% 30 4% 150 

12 98412 93462 82.00 200 4 R33 24% 33 4% 165 

14 93414 93464 94.00 200 4 R36 24% 36 4% 180 

16 93416 93466 104.00 200 4 R39 24% 39 4% 195 

18 93418 93468 114.00 200 4 R42 24% 42 4% 210 

fo 20 93420 93470 124.00 200 4 R45 24% 45 41% 225 
| ee 22 93422 93472 13400 200 4 R48 24% 48 4% 240 
tte estan 24 93424 93474 14400 200 4 R51 24% 51 4% 255 
26 93426 93476 160.00 200 4 R54 24% 54 4% 270 

28 93428 93478 170.00 200 4 RST 24% 57 4% 285 

30 93430 93480 184.00 200 4 R60 24% 60 4% 305 

32 93432 93482 200.00 200 4 R63 24% 63 4% 325 


With Main Lugs Only. 


PANELS WITH FUSIBLE MAINS 


4 93804 93854 $58.00 60 R24 24% 24 4% 120 
6 93806 93856 70.00 100 R33 24% 33 4% 165 
8 93808 93858 80.00 100 R36 24% 36 44% 180 
10 93810 93860 90.00 100 R39 24% 39 4% 195 


12 93812 93862 110.00 200 R45 24% 45 44% 225 
14 93814 93864 120.00 200 R48 24% 48 4% 240 
16 93816 93866 130.00 200 6 
18 93818 93868 140.00 200 


20 93820 93870 150.00 200 
22 93822 93872 170.00 200 
24 93824 93874 180.00 200 
26 93826 93876 190.00 200 


28 93828 93878 200.00 200 
30 93830 93880 210.00 200 
32 93832 93882 220.00 200 


Pee PEPE PPP PPP 
av 
ol 
TS 
bo 
wae 
= 
oO 
re 
He 
bo 
+] 
So 


4 93904 93954 $72.00 60 4 R33 24% 33 4% 150 
6 93906 93956 92.00 100 4 R39 241% 39 4%, 180 
8 93908 93958 102.00 100 

0) 93910 93960 112.00 100 
2 


93912 93962 144.00 200 
14 93914 93964 154.00 200 
16 93916 93966 174.00 200 
18 93918 93968 184.00 200 


20 93920 93970 194.00 200 
22 93922 93972 204.00 200 
24 93924 93974 214.00 200 
26 93926 93976 230.00 200 


28 93928 93978 244.00 200 
30 93930 93980 260.00 200 


With Fusible Main Brush 32 93932 93982 274.00 200 
Type Switch. 


Ree PEPE PEER PP 
< 
fo?) 
(oe) 
bo 
rs 
ol 
> 
or) 
oo 
ol 
H 
ry 
(se) 
es 
oO 


PANELS WITH FUSIBLE MAIN KNIFE SWITCH 


+ 94004 94054 $69.00 60 4 R33 24% 33 41%, 150 

6 94006 94056 90.00 100 + R39 24% 39 41% 180 

8 94008 94058 100.00 100 4 R42 241% 42 41% 195 

10 94010 94060 110.00 100 4 R45 241% 45 4% 210 

12 94012 94062 141.00 200 4 V51 2414 Sil 5 245 

14 94014 94064 151.00 200 4 V54 241% 54 5 260 

16 94016 94066 171.00 200 t V57 241% 57 514 275 

18 94018 94068 181.00 200 + Vv60 24% 60 54 295 

20 94020 94070 191.00 200 4 V63 241 63 5 SLD 

22 94022 94072 201.00 200 4 V66 24% 66 54 335 

24 94024 94074 211.00 200 4 V69 24% 69 54 355 

26 94026 94076 227.00 200 4 V72 241% 72 by 375 

28 94028 94078 241.00 200 4 V75 24% 7 54 395 

30 94030 94080 257.00 200 4 V78 241% 78 5uy 415 

With Fusible Main Knife 32 94032 94082 271.00 200 + Vv81 24% 81 54 435 

Switch. 


Panels with Unfused Main Switches can be furnished at same prices as Panels with 
Fusible Main Switches. 


36 


x 


BENJAMIN 


N:STARREIT m 


Type LPT Protective Panels with Cabinets — 3 Wire Mains 


Branches: 2 Wire, 30 Amp. 250 V. HEAVY DUTY Tumbler Switches, 
Plug Fuses. 


List Capacity | Gutter 
Prica of Mains | Space 
Amps. | Inches 


PANELS WITH MAIN LUGS ONLY 


No. 


Panel with | Panel with Cabinet | 


Cat.No. Cat. No. 


2 Fuse Branches 


Mains: 125-250 Volt. 


Box Dimensions in Inches | Shipping SINGLE DOOR 
Wide High Deep | Weight ; 
Pounds CABINETS 


4 94104 94154 $38.00 80 4 R21 24% 21 4% 105 

6 94106 94156 48.00 GO 00 ds OR2ANre 249d edt ee 3 

8 94108 94158 58.00 60M) 045 ROT smolts ie 85 

10 94110 94160 68.00 60 4 R30 24% 30 4% 150 

12 94112 94162 78.00 60 4 R33 24% 33 4% 165 

14 94114 94164 90.00 100 4 R386 24% 36 4% 180 

16 94116 94166 100.00 100 4 R39 24% 39 41% 195 

18 94118 94168 110.00 100 4 R42 24% 42 4% 210 

20 94120 94170 12400 100 4 R45 24% 45 4% 225 

Boma 9212294172 134,000 100) 48 R48 2418 48 43g 940 

24 94124 94174 144.00 100 4 R51 24% 51 4% 255 
26 94126 94176 154.00 100 4 R54 24% 54 414 270 

28 94128 94178 164.00 100 4 R57 24% 57 4% 285 

30 94130 94180 174.00 100 4 R60 241% 60 4% 305 

9 2 99 
32) 94132, 94182 190.00 100 4 REZ 24% 68 4825 ta nadin Tugs ONY, 
PANELS WITH FUSIBLE MAINS 

4 94204 94254 $52.00 300) poe eRO4SBEO4Ie 94 412) 130 = 

6 94206 94256 62.00 GO 4a R27eee At, ee 87 edd 13h eae 
8 94208 94258 72.00 60 ete R30 m4 160 S04 0 Tr = oe) x 
10 94210 94260 82.00 60. 4 R33) 624% 880 41GB PI = oan 
12 94212 94262 92.00 bE eeRS Gm 41 60) a 4de8 180 (co emeen ac! 
gn 94214094264 112.00.) 1000) 4 R456 2414 45° 4g 295 pa eee | 
16 94216 94266 122.00 100 4 R48 24% 48 41% 240 (oo a 
18 94218 94268 132.00 100 4 R51 24% 51 4% 255 | (co ee ms 
20 94220 94270 142.00 100 4 R54 24% 54 4% 270 om 
poem 42226 042795 152.00) 1004) R57) 2432 57 414-285 re 
24 94224 94274 162.00 100 4 R60 24% 60 4% 305 
26 94226 94276 176.00 100 4 R63 24% 68 4% 325 
28 94228 94278 186.00 100 4 R66 24% 66 4% 345 
30 94230 94280 196.00 100 4 R69 24% 69 4% 365 . 
62m 942320 04202 9 206.00) 1000 4 (R725 8 24%40 72° 41% 885 NRERT IR) CEN Gs 


PANELS WITH FUSIBLE MAIN BRUSH 


4 94304 
6 94306 
8 94308 
10 94310 
12 94312 
14 94314 
16 94316 
18 94318 
20 94320 
22 94322 
24 94324 
26 © 9.4326 
28 94328 
30 94330 
32 94332 


4 94404 
6 94406 
8 94408 

10 94410 

12 94412 

14 94414 

16 94416 

18 94418 

20 94420 

22 94422 

24 94424 

26 94426 

28 94428 

30 94430 

32 94432 


94354 
94356 
94358 
94360 


94362 
94364 
94366 
94368 


94370 
94372 
94374 
94376 


94378 
94380 
94382 


94454 
94456 
94458 
94460 


94462 
94464 
94466 
94468 


94470 
94472 
94474 
94476 


94478 
94480 
94482 


$70.00 
80.00 
90.00 
100.00 


110.00 
134.00 
144.00 
164.00 


174.00 
184.00 
194.00 
204.00 


214.00 
224.00 
234.00 


ALL PLALL PEDP PPPS 


APP LLLP PALE PP BP 


R33 
R36 
R39 
R42 


R45 
R51 
R54 
R57 


R60 
R63 
R66 
R69 


R72 
R75 
R78 


R30 
R36 


-ESWS PSPSPS 


B Ye 195 
24% 45 41 210 
24% 51 41 240 
24% 54 4% 255 
24% Bye 4% 270 
241% 60 4% 290 
241% 63 4%, 310 
241% 66 A330) 
24% 69 4% 350 
241% 72 4%, 37 
24% 75 41655 390 - : = 
241, 78 41, 410 With iterate Ret 
241% 30 4% 150 
2416 36 Al%e 165 
24% 39 4% 180 
241% 42 4% 195 
241 45 4% 210 
24% 51 4% 240 
24% 54 414 255 
241% 57 416 270 a Gash a Baos= 3) 
241% 60 4% 290 a | 
24% 63 41%, 310 
24% 66 4% 330 | timated 
24% 69 41% 350 
241% 2, AG BYTi(i) 
24% 15 4% 390 
241% a 4% 410 With Fusible Main Knife 


Switch. 


Panels with Unfused Main Switches can be furnished at same prices as Panels with 
Fusible Main Switches. 


37 


bp 


ia BENJAMIN STARRETT 
2 Wire Mains ‘Type OC Open Front Panels with Cabinets 


2 Fuse Branches Branches: 2 Wire, Cartridge Fuses Only. 
Mains: 125 Volt. 


Panel with | Panel with Cabinet | List Capacity | Gutter Box Dimensions in Inches 
Surface Panel with Cabinet _] lush Price | f Mains | Space Deep 
Cat.No. Cat. No. Amps. | Inches Outside | Outside | Inside 


PANELS WITH MAIN LUGS ONLY 


Shipping 
Weight 
Pounds 


SINGLE DOOR 
CABINETS 


= sf 4 94804 94854 $38.00 60 4). R18 24120 18 ee 
pepe 3 8 94808 94858 45.00 100 4 R21 24% «21 4% 4105 
t= == | 12 94812 94862 52.00 200 4 R24 24% 24 4% 120 
i= i || 16 94816 94866 60.00 200 4 R27 24% 27 4% 185 
= Be a SS 
beet mil 20 94820 94870 70.00 200 AMT R30 We 24305 30 4% 150 
‘> mand 24 948948 194874 80,00 200. «4° R383. 2426. 83 eee 
28 94828 94878 90.00 200 4 R36 24% 36 4% #180 
32 94832 94882 100.00 200 4 #4R39 24% 39 44% 4195 


PANELS WITH FUSIBLE MAINS 
= “ Sa sti 4 94904 94954 $54.00 60 4 R21 24% 21 4% 4105 
4 ==) 
<> cm 8 94908 94958 68.00 100 4 R30 2416 30. u4iumaaD 
4 a. 
«> | 42 94912 94962 ' 85.00 200 - 4 R86 24%) 36” 432umieO 
‘= . 16° 94916 94966. 95.00 200 °4 R89 24169 9939) ipemos 
o= B= oa. 
20 94920 94970 105.00 200 4 R42 24% 42 4% 210 
®4- 94924. 94974 115.00 300 4 4945. 241400 45) eeu 
28 94928 94978 125.00 200 4 R48 24% 48 4% 240 
| 32 94932 94982 185.00. 200 4 R51 2414, 995i eee 
With Fusible Tee 
PANELS WITH FUSELESS MAIN KNIFE SWITCH 
4 95004 95054 $67.00 60) 4 R30 84169 930. Paige 
8 95008 95058 78.00 100 94 R36 2444 36 4350 ules 
12 95012 95062 117.00 200 4 R42 24% 42 4% 195 
16. 95016 95066 127,00 200 4 R45 adie 4h ee 
20 95020 95070 137.00 200 4 R48 24% 48 4% 295 
24 95024 95074 147.00 .200 4 RS1 24% 51 4% 245 
28 95028 95078 157.00 200 4 R54 2414 54 " 4agniieaeg 
32 95032 95082 177.00" 200 4 R57 2414 57° 4a megs 


With Fuses Main Knife 
Switch 


PANELS WITH FUSIBLE MAIN KNIFE SWITCH 


4 95104 95154 $67.00 60) © 40 R300" 24%, 130 eae 

8 95108 95158 78.00 100 4 R86 24% 36 4% 165 
12 95112 95162 117.00 200 4 °V42 243, 42> 5 eetas 
16 95116 95166 127.00 200 4 V45 24% 45 5% 210 
20 95120 95170 137.00 200 4 48 24% 48 5% 225 
94 95124 95174. 147,00 9200) 40 V1 24 ot ee 
28 95128 95178 157.00 200 4 V54 24% 54 5% 260 
32 95139-95182 7700 200) 4 V57. 6 24i¢ue 5 ee a 


With Fusible Main Knife 
Switch. 


Se 
38 


£m EN AMIN'SEARRELT 
Type OC Open Front Panels withCabinets 3 Wire Mains 


Branches: 2 Wire, Cartridge Fuses Only. 2 Fuse Branches 
Mains: 125-250 Volt. 


Panel with Cabinet Capacity Shipping SINGLE DOOR 
Surface Flush P of Mains | Space Weight 
de) Amps. | Inches No. | outside | Outside Inside_| Pounds CABINETS 


PANELS WITH MAIN LUGS ONLY 


4 95204 95304 $38.00 30 4 R18 24% 18 414 90 
8 95208 95308 45.00 60 49 ROT) 12446 21 4%, 105 
12 95212 95312 52.00 60 4 R24 24% 24 4% 120 mses ht 
16 95216 95316 60.00 100 4 R27 24% 27 4% 135 => 2 
zm = BO} i: 
20 95220 95320 70.00 100 4 R30 24% 30 4% 150 i Be = 54|/) 
24 95224 95324 80.00 106 Ame RSS eed te aee 33 4% 165 a aml 
28 95228 95328 90.00 100 A R365 24568 7 36 4% 180 ‘= ie = =|) 
32 95232 95332 100.00 100 499 R397) 24159 8539 4% 195 eee <1) 
36 95236 95336 115.00 200 4 R42 241% 49 4% 210 ao Al 
40 95240 95340 125.00 200 4 R45 24% 45 4% 225 <i <= 
44 95244 95344 135.00 200 die RIB 24458 48 4%, 240 ‘2 [= 5 
48 95248 95348 145.00 200 4 R51 24% 51 4% 255 pie tle 
52 95252 95352 160.00 200 4 R54 24% 54 4% 270 
56 95256 95356 170.00 200 Maye VOLES Ty 4% 285 
9 fj 9A L i i 
60 95260 95360 180.00 200 4 R60 24% & 60 4% 300 WARES One 
PANELS WITH FUSIBLE MAINS 
4 95404 95504 $54.00 30 AP ROTG 24-21 41%, 105 
8 95408 95508 62.00 60 4 R24 24% 24 41% 120 “ 
12 95412 95512 70.00 60 4 “R27 . 24346 27 4% 185 = 
16 95416 95516 85.00 100 4 R36 24% 36 4% 180 rp} 
20 95420 95520 95.00 100 4 R39 24% 39 4% 195 4 
24 95424 95524 105.00 100 Bee R4 eee os ee 22 4%, 210 = 3 
28 95428 95528 115.00 100 4 R45 24% 45 41%° 295 <s 
32 95432 95532 125.00 100 4 R48 24% 48 4% 240 bee 
36 95436 95536 145.00 200 4 R54 24% 54 4% 27 at 
40 95440 95540 160.00 200 4 R57 24% 57 41, 285 
44 95444 95544 170.00 200 4 ROOM 241" S60 4% 300 
48 95448 95548 180.00 200 4 R63 24% 33 4% 315 
52 95452 95552 190.00 200 4 R66 241% 66 41% 330 
56 95456 95556 200.00 200 4 R69 24% °& 69 41%, 345 
60 95460 95560 210.00 200 eR (ese eT 2 4% 360 


PANELS WITH FUSELESS MAIN KNIFE SWITCH 


A 95604 95804 $66.00 30 4 R27 24% 27 4% 120 

8 95608 95808 75.00 60 4 R33 241% 33 4% 150 
ie 95612 95812 83.00 60 4 R36 24% 36 41% 165 
16 95616 95816 98.00 100 4 R42 24% 42 4% 195 
20 95620 95820 108.00 100 4 R45 24% 45 41% 210 
24 95624 95824 118.00 100 4 R48 24% 48 4% 225 
28 95628 95828 134.00 100 4 R51 241% 51 414 245 
32 95632 95832 144.00 100 4 R54 24% 54 414 260 
36 95636 95836 181.00 200 4 R60 24% 60 4% 290 
40 95640 95840 191.00 200 4 R63 24% 63 4% 305 
44 95644 95844 201.00 200 4 R66 24% 66 4i% 320 
48 95648 95848 211.00 200 4 R69 24% 69 41% 335 
52 95652 95852 221.00 200 4 R72 241% 12 4i% 350 é 
56 95656 95856 231.00 200 4 R75 241% 75 4% 365 - “ 
60 95660 95860 241.00 200 4 R78 24% 78 415 380 With Fuseless Main Knife 

Switch. 
PANELS WITH FUSIBLE MAIN KNIFE SWITCH 

4 95904 96004 $66.00 30 4 R27 24% PA 414 120 

8 95908 96008 EO TH 4 R33 241% 33 4% 150 
12 95912 96012 83.00 60 4 R36 24% 3 4% 165 
16 95916 96016 98.00 100 4 R42 24% 42 41% 195 
20 95920 96020 108.00 100 4 R45 241% 45 AV, 210 oC 
24 95924 96024 118.00 100 4 R48 24% 48 4% 225 a 
28 95928 96028 134.00 100 4 R51 241% 51 4% 245 e 
32 95932 96032 144.00 100 4 R54 24% 54 4M 260 fe 

i 

36 95936 96036 181.00 200 4 V60 241% 60 pA 290 et 
40 95940 96040 191.00 200 4 V63 24% 3 5% 305 i 
44 95944 96044 201.00 200 4 V66 241% 66 514 320 3 
48 95948 96048 211.00 200 4 V69 241% 69 54 SEIS) 
52 95952 96052 221.00 200 4 V72 24% 2 5% 350 
56 95956 96056 231.00 200 4 V75 241% (3 D4 365 
60 95960 96060 241.00 200 4 V78 24% 78 54 380 With Fusible Main Knife 


Switch. 


SS ess EEE 


39 


ta BENAMIN-STARREY ———______________» 
2 Wire Mains ‘l'ype OCT Open Front Panels with Cabinets 


2 Fuse Branches Branches: 2 Wire, 30 Amp. 250 V. HEAVY DUTY Tumbler Switches, 
Cartridge Fuses. Mains: 125 Volt. 


Panel with Cabinet List Capacity | Gutter Boe Box Dimensions in Inches 
Price of Mains | Space No 
Amps. | Inches 3 


Surface Flush Wide High 
Cat. No. Cat. No. Outside | Outside | Inside 


PANELS WITH MAIN LUGS ONLY 


Shipping 
Weight 
Pounds 


SINGLE DOOR No. 


CABINETS 


4 96104 96154 $4200 60 4 R21 24% 21 4% 105 

6 96106 96156 52.00 100 4 R24 24% 24 4% 120 

om | 8 96108 96158 62.00 100 4 R27 24% 27 4% 135 

zi 10 96110 96160 72.00 100 4 R30 24% 30 4% 1650 

=| 12 96112 96162  82.00> 200 4 R33 24% 38 439° 91Gb 

a m|| 14 96114 96164 94.00 200 4 R36 24% 36 4% 180 

all 16 96116 96166 104.00 200 4 R39 24% 39 4% 195 

| 18 96118 96168 11400 200 4 R42 24% 42 4% 210 

r4| 20 96120 96170 124.00 200 4 R45 24% 45 4% 225 

=|) 99 96122 96172. H134,00e" 200) 4) | R48) 2414 oe eg etic mmm 

= 3 24 96124 96174 14400 200 4 R51 24% 51 4% 255 

26 96126 96176 160.00 200 4 R54 24% 54 4% 270 

28 96128 96178 170.00 200 4 R57 24% 57 4% 285 

30 96130 96180 184.00 200 4 R60 24% 60 4% 305 

32 96132 96182 200.00 200 4 R63 24% 68 4% 325 

PANELS WITH FUSIBLE MAINS 

4 96204 96254 $58.00 60 4 R24 24% 24 4% 120 

2 6 96206 96256 70.00 100 4 R33 24% 33 4% 165 

a | 8 96208 96258 80.00 100 4 R36 24% 36 4% 180 

aml 10 96210 96260 90.00 100 4> R39 241% 39 4% 195 
edd 

a =| 12 96212 96262 110.00 200 4 R45 24% 45 4% 295 

fs 2 /| 14 96214 96264 «120.00 200 «2S 4 Ss R48. 24% 44D 

fe =| 16 96216 96266 130.00 200 4 R51 24% 51 4% 255 

fc 18 96218 96268 140.00 200 4 R54 24% 54 4% 270 

fs =| 20 96220 96270 150.00 200 4 R57 24% 57 4% 285 

: 33) 22 96222 96272 170.00 200 4 R60 24% 60 4% 305 

24 96224 96274 180.00 200 4 R63 24% 63 4% 325 

26 96226 96276 190.00 200 4 R66 24% 66 4% 345 

28 96228 96278 200.00 200 4 R69 24% 69 4% 365 

30 96230 96280 210.00 200 4 R72 24% 72 4% 385 

32 96232 96282 220.00 200 4 R75 24% 75 4% 405 


PANELS WITH FUSELESS MAIN KNIFE SWITCH 


4 96304 96354 $69.00 60 Aer 3 Samed ss 33 4% 150 

6 96306 96356 90.00 100 4 R39 24% 39 Ai ASO 

8 96308 96358 100.00 100 4 R42 9024 ee 4% 195 

10 96310 96360 110.00 100 4 R45 9412 45 41Z eo 

12 96312 96362 141.00 200 4 R51, e434 51 4%, 245 

14 96314 96364 151.00 200 4 R54 24% 54 4% 260 

16 96316 96366 171.00 200 4 R57. 24% 57 4% 275 

“ 18 96318 96368 181.00 200 4 R60 24% 60 dig 4295 

ve 20 96320 96370 191.00 200 4 R63 24% 63 4% 315 

« 22 96322 96372 201.00 200 4 R66 24% 66 Ev BCT. 
bed 24 96324 96374 211.00 200 4 R69 24% 69 4%, 355 
26 96326 96376 227.00 200 4 R72 ose een 2 4% 375 

28 96328 96378 241.00 200 4. R75 24% 75 4% 395 

. — 30 96330 96380 257.00 200 4 R78 24% 78 4% 415 
With Fuseless Main Knife 32 96332 96382 271.00 200 4 R81 24% 81 4% 435 


Switch. 


PANELS WITH FUSIBLE MAIN KNIFE SWITCH 


4 96404 96454 $69.00 60 4 R33 24% 33 41% 150 
6 96406 96456 90.00 100 4 R39 24% 39 41% 180 
8 96408 96458 100.00 100 4 R42 241% 42 414 IES) 55 
10 96410 96460 110.00 100 4 R45 24% 45 4% 210 
12 96412 96462 141.00 200 f v51 241% 51 buy 245 
14 96414 96464 151.00 200 4 V54 244% 54 5 260 
16 96416 96466 171.00 200 4 V57 241% 57 5 275 
i & 18 96418 96468 181.00 200 4 V60 241% 60 buy 295 
hz Be 
> 20 96420 96470 191.00 200 4 V63 24% 63 5 315 
a 22 96422 96472 201.00 200 4 V66 241% 66 514 335 
Sm 24 96424 96474 211.00 200 4 V69 24% 69 buy 355 
26 96426 96476 227.00 200 4 V72 24% 72 bY 375 
28 96428 96478 241.00 200 4 V75 24% 75 5A 395 
—— ananenian 30 96430 96480 257.00 200 4 V78 2416 78 54 415 
With Fuaiblei Main) Kxite 32*" 964324 96482. F271 009 F200) pe 4 ee VS ed 54 = 435 
va = a 


40) 


— IN Ne 


Type OCT Open Front Panels with Cabinets — 3 wire mains 


Branches: 2 Wire, 30 Amp. 250 V. HEAVY DUTY Tumbler Switches, 2 Fuse Branches 
Cartridge Fuses. Mains: 125-250 Volt. 


seumalicapsaiy; | autier | bo 
Cat.No. | Cat. No. Amps. _| Inches *__| Outside| Outside | Inside 
PANELS WITH MAIN LUGS ONLY 


4 96504 96554 $38.00 30 4 R21 241% 
6 96506 96556 48.00 60 4 R24 24% 24 4 
8 


Shipping SINGLE DOOR 
ight 
‘ihe CABINETS 


b 
i) 
iat 
~) 
So 
iL. 
—t 


96508 96558 58.00 60 4 R27 24% 27 4% 135 | : 
10 96510 96560 68.00 60 4 R30 24% 30 4% 150 pa a 
12 96512 96562 78.00 GOERS 41 358 4% 165 cc eee. || 
14 96514 96564 90.00 109 4 R36 2414, 36 4%, 180 te > ls ee ef | 
16 96516 96566 100.0 R39 241%, 39 4% 195 | ae ig 
18 96518 96568 110.00 100 4 R42 24% 42 41% 210 res Se =: ||) 
cn (= o|"* ad 
20 96520 96570 124.00 100 4 R45 24% 45 4% 995 ‘21 ee=:> 
22 =6©96522 «96572 «134.00 ~—-:100 4 R48 241% 48 4% 240 eet dl 
24 96524 96574 144.00 100 APRS DAU 5] 41g 966 = oe ots 
26 96526 96576 154.00 100 4 R54 24% 54 4% 270 ans i < ry 
28 96528 96578 164.00 100 ASR 747 44% 285 
30 96530 96580 174.00 100 4 R60 241%, 60 41% 305 
32 96532 96582 190.00 100 4 R63 24% £63 444, 325 
With Main Lugs Only. 
PANELS WITH FUSIBLE MAINS 
4 96604 96654 $52.00 30 4 R24 24% 24 4% 120 
6 96606 96656 62.00 60 AERO, OAs) 87 4146 135 
8 96608 96658 72.00 60 4 R30 24% 30 41% 150 
10 96610 96660 82.00 60 A AER ee 4% 165 
12 96612 96662 92.00 60 dee R364 ie 36 4% 180 
14 96614 96664 112.00 100 4 R45 241% 45 414%, 2295 
16 96616 96666 122.00 100 4 R48 24% 48 4%, 240 
18 96618 96668 132.00 100 4 R51 24% 51 444 255 
20 96620 96670 142.00 100 4 R54 24% 54 4% 270 
22 «96622 =96672 =—«-152.00 + ~=—:100 4 R5ie 24s) + 57 41, 9285 
24 96624 96674 162.00 100 4 R60 24% °&60 44, 305 
26 96626 96676 176.00 100 45) R63) 2414. «63 4%, 325 
28 96628 96678 186.00 100 Zee R664 ce 66 4% 345 
30 96630 96680 196.00 100 Awe 6OMED 1 cone 69 4% 365 
32 96632 96682 206.00 100 fe’ Weve evs Eb) 4i, 385 
PANELS WITH FUSELESS MAIN KNIFE SWITCH 
4 96804 96854 $66.00 30 4 R304) 30 44% 150 
6 96806 96856 77.00 60 tee R36 241 86 4% 165 
8 96808 96858 87.00 60 aeRO 4 eee 39 4% 180 
10 96810 96860 97.00 60 4 R42 941% 42 4% 195 
12 96812 96862 107.00 60 4 R45 241% 45 4% 210 
14 96814 96864 132.00 100 4 R51 241% 51 4% 240 
16 96816 96866 142.00 100 AR 540 416 54 44, 255 
18 96818 96868 162.00 100 fe Waeye yy | aay fave yi) yee 
= Bel 
20 96820 96870 172.00 100 4A R60” 2476 ~~ 60 4144 290 i 
22 =©96822 «96872 «182.00 100 Cee RG6SUn od ae G3 Gi Ei) pos 
24 96824 96874 192.00 100 Awe R66 e466 Ee SEG) =e 
26 96826 96876 202.00 100 4 R69 241% £69 4%, 350 
28 96828 96878 212.00 100 A> R72 $2414 72 4% 370 
30 96830 96880 222.00 100 me Wega © OEE Ns 4%, 390 . midi 
32 96832 96882 232.00 100 4 R78 241%, 78 4% 410 With Fuseless Main Knife 
PANELS WITH FUSIBLE MAIN KNIFE SWITCH 
4 96904 96954 $66.00 30 4 R30 24% 30 414 150 
6 96906 96956 77.00 60 Ape R364 26 4% 165 
8 96908 96958 87.00 60 4 R39 92416 «989 4% 180 
10 96910 96960 97.00 60 ARADO 4 160d? 4% 195 
12 96912 96962 107.00 60 4 R45 2414 45 Ze 210 
14 96914 96964 132.00 100 Agee R524 Ge! 414 240 
16 96916 96966 142.00 100 4 R54 241% 54 41, 255 
18 96918 96968 162.00 100 eee R57 41 OT 4 270 
20 96920 96970 172.00 100 4 R60 24% °&60 4% 290 
22 96922 96972 182.00 100 4 R63 24% 68 44% 310 
24 96924 96974 192.00 100 4 R66 24% 66 4% 330 
26 96926 96976 202.00 100 4 R69 241% 69 4% 350 
28 96928 96978 212.00 100 fy fey ph OE RVR 70) 4 370 
30 96930 96980 222.00 100 hoe R754 TG 4% 390 ; ; . 
32 96932 96982 232.00 100 4 R78 241% 78 41%, 410 With Fusihle Main Knife 


Switch. 


SSSsSsSSSSSSSSS9909080 SST 


aN 
bak 


“ ___— BENJAMIN:STARRETT “ ; 
2 Wire Mains ‘Type OPK Open Front Panels with Cabinets 


2 Fuse Branches Branches: 2 Wire, 30 Amp. 125 V. Knife Switches, Plug Fuses. | 
; 
| 


Mains: 125 Volt. 


Panel with | Panel with Cabinet _ | List Capacity | Gutter Box Dimensions in Inches 
Cat.No. Cat. No. Amps. | Inches Outside | Outside | Inside 


PANELS WITH MAIN LUGS ONLY 


SINGLE DOOR 
CABINETS 


Shipping 
Weight 
Pounds 


4 97004 97054 $44.00 60 4 R21 24% 21 4%, 100 
6 97006 97056 52.00 100 4 R24 24% 24 At 115 
8 97008 97058 62.00 100 4 R27 241% 27 4% 130 
10 97010 97060 72.00 100 4 R30 24% 30 4p 145 
12 97012 97062 82.00 200 4 R33 24% 33 41% 160 
14 97014 97064 94.00 200 4 R36 24% 36 4% 175 
16 97016 97066 104.00 200 4 R39 24% 39 4% 185 
18 97018 97068 114.00 200 4 R42 24% 42 4% 200 
20 97020 97070 124.00 200 4 R45 24% 45 4% 215 
22 97022 97072) 134.00 200 4 R48 24% 48 4% 225 
24 97024 97074 144.00 200 4 R51 24% 51 4% 240 
26 97026 97076 154.00 200 4 R54 24% 54 4% 255 
28 97028 97078 164.00 200 1 R57 24% 57 4% 270 
30 97030 97080 184.00 200 4 R60 241% 60 4% 285 
32 97032 97082 200.00 200 4 R63 24% 63 4% 305 


PANELS WITH FUSIBLE MAINS 


4 97104 97154 $58.00 60 4 R24 241% 24 

6 97106 97156 70.00 100 

8 97108 97158 80.00 100 
10 97110 97160 90.00 100 


4 
4 
4 
12 NW STAN LDC 200 4 
14 97114 97164 120.00 200 4 
16 NIG SA) TROL 200 4 
18 2 Ws Cs cy Ad Uo > We? OO) 200 4 R54 24% 54 4u% 255 
4 
4 
4 
4 
4 
4 
4 


20 O74 20 Me ali, Ommaney) 80,0) 200 
22 ee ATER WON) 200 
24 97124 97174 180.00 200 
26 ONS ANAS = OO ONG 200 


28 97128 97178 200.00 200 
30 IASON 97 1S ON 20200 200 
32 SNS 2m Some 800) 200 


He HR He HEE 


PANELS WITH FUSELESS MAIN KNIFE SWITCH 


4 97204 97254 $65.00 60 4 R33 24% 33 4% 145 

6 97206 97256 78.00 100 4 R39 24% 39 41% 175 

8 O20 SmOZ OS 88.00 100 4 R42 241% 42 4% 190 

10 97210 97260 98.00 100 4 R45 24% 45 4% 205 

12 97212 97262 130.00 200 4 R51 24% Dill AV, 240 

14 97214 97264 140.00 200 4 R54 24% 54 41% 255 

16 97216 97266 156.00 200 4 R57 24% 57 4% 265 

18 97218 97268 166.00 200 4 R60 241% 60 4% 285 

20 97220 97270 176.00 200 4 R63 241 63 4% 305 

22 97222 97272 184.00 200 4 R66 241% 66 415 320 

24 97224 97274 194.00 200 4 R69 241% 69 4% 340 

26 O22 Oe OC Ome 8200) 200 4 R72 24% 72 4% 360 

ee 28 97228 97278 218.00 200 4 R75 24% 19 41% 380 

Fa = 30 97.2300 90280 Re 2 8200 200 t R78 24% 78 4% 400 

With ao ee Knife 32 97232) 97282) 238.00 200 4 R81 241% 81 414 415 
Switch. 


PANELS WITH FUSIBLE MAIN KNIFE SWITCH 


4 97304 97354 $65.00 60 4 R33 24% 33 414 145 

6 97306 97356 78.00 100 4 R39 24% 39 415 175 

8 97308 97358 88.00 100 4 R42 24% 42 416 190 

10 97310 97360 98.00 100 4 R45 241% 45 41, 205 

12 97312 97362 130.00 200 4 V51 241% 51 514 240 

14 97314 97364 140.00 200 4 V54 241% 54 5M 255 

16 97316 97366 156.00 200 4 V57 241% 57 514 265 

18 97318 97368 166.00 200 4 V60 2419 60 54 285 

20 97320 97370 176.00 200 + V63 24% 3 514 305 

22 97322 97372 184.00 200 4 V66 24% 66 54 320 

24 97324 97374 194.00 200 1 V69 24% 69 buy 340 

26 97326 97376 208.00 200 4 V72 241% 72 buy 360 

28 97328 97378 218.00 200 4 V75 24% {G5 514 380 

Saneramae mgt: 30:4 97330 97380 228.00, 200 4 7S 2446 78 Bi = 400 

With a EAE Knife 32 97332 97382 238.00 200 4 v81 24% 81 5%4 415 
Lone loot 


42 


BENJAMIN STARRETT 
Type OPK Open Front Panels with Cabinets 3 wire mains 


Branches: 2 Wire, 30 Amp. 125 V. Knife Switches, Plug Fuses. 2 Fuse Branches 
Mains: 125-250 Volt. 


| 


Panel with Cabinet Box Dimensions in Inches 


Shipping 


SINGLE DOOR 


List agree ell Bax 
of Surface : of Mains | Space High Deep | Weight 
| cat'No. | P#® | amps. [inches |_N°- | ouside Pounds CABINETS 


PANELS WITH MAIN LUGS ONLY 


4 97404 97454 $42.00 B0meee4e R21, 2436 91 ae 100 

6 97406 97456 48.00 GUM tee RO4 en 9412) 04” diceee 116 

8 97408 97458 58.00 HU LE AGE OE Eres 

10 97410 97460 68.00 60eeee FSO NNr2434™ SOS Bisa n i45 

12 97412 97462 78.00 PURE ERSSgeeo432 8) 33 tip at 60 

14 97414 97464 9000 100 4 R36 24% 36 4% 175 

16 97416 97466 100.00 100 4 R39 24% 39 41% 185 

18 97418 97468 110.00 100 4 R42 24% 42 4% 200 

20 97420 97470 12400 100 4 R45 24% 45 4% 215 

Semen 974228 8974727134 00 we 0C ee R489 92472 48° hig | 006 

24 97424 97474 14400 100 4 R51 24% 51 4% 240 

26 97426 97476 15400 100 4 R54 24% 54 4% 255 

28 97428 97478 164.00 100 4 R57 24% T 4% 270 

30 97430 97480 174.00 100 4 R60 24% 60 41% 285 

32 97432 97482 19000 100 4 R63 24% 68 4% 305 

PANELS WITH FUSIBLE MAINS 

4 97504 97554 $52.00 Rly dh ga OR als 

6 97506 97556 62.00 COME Ro fee 24 ere o7 | B4i2, 130 

8 97508 97558 72.00 C0! ELRSO en 2416 5 30) 444) 8145 

10 97510 97560 2.00 AD) SE FER SDR 1 4% 160 

12 97512 97562 92.00 60 4 R386 24% 38 4% 175 

14 97514 97564 112.00 100 4 R45 24% 45 4% 215 

16 97516 97566 122.00 100 4 R48 24% 48 41% 225 

18 - 97518 97568 132.00 100 4 R51 24% 51 4% 240 

20 97520 97570 14200 100 4 R54 24% 54 4% 255 

22 97522 97572 15200 100 4 R57 24% 57 4% 270 

24 97524 97574 162.00 100 4 R60 24% 60 4% 285 

26 . 97526 97576 176.00 100 4 R63 24% 63 4% 305 

28 97528 97578 186.00 100 4 R66 24% 66 4% 325 

30 97530 97580 196.00 100 4 R69 24% 69 4% 345 

Bomb) 2975820 e206, 000e 00) ANU eR720e4y 72-432 860 

PANELS WITH FUSELESS MAIN KNIFE SWITCH 

4 97604 97654 $62.00 300° 4 R30) 9243, ««30 «44h 180 

6 97606 97656 72.00 60 4 R36 241% 36 4% 160 

8 97608 97658 80.00 COmmE OR MER SOU) 4 Zemee SO mn 4i2 © 2175 

10 97610 97660 90.00 GO R42m 24125 42. eedaty 2190 

12 97612 97662 100.00 60 4 R45 24% 45 41% 205 

14 97614 97664 120.00 100 4 R51 24% 51 4% 240 

16 97616 97666 130.00 100 4 R54 24% 54 4% 255 

18 97618 97668 14800 100 4 R57 24% 57 4% 265 

20 97620 97670 158.00 100 4 R60 24% 60 4% 285 
OS 97622 97672 166.001! 100 4. R63 24% 3 Ate we 305 

pam 97624997674) 176.000 9100. 4° R66) 24% 66 4% 3.20 

26 97626 97676 184.00 100 4 R69 24% 69 4% 340 

28 97628 97678 200.00 100 4 R72 24% #72 4% 360 : i 
30 97630 97680 210.00 100 4 R75 24% 75 4% 380 — 
32 97632 97682 220.00 «100 4 7B 24% 784% 400 With Fuseless Main Knife 

ee — witch. 
PANELS WITH FUSIBLE MAIN KNIFE SWITCH 

4 97704 97754 $62.00 SUM RS0ueel 422 mers e415 130 

6 97706 97756 72.00 CU) med EER SOe 24 Gee S6 9 9434" £160 

8 97708 97758 80.00 60) 45 R39) 92412" "939 414175 

10 97710 97760 90.00 60m eR 40mm 41, ed 4s 190 

12 97712 97762 100.00 60 4 R45 241% 45 4% 205 

jam 2977145 9977640120008) 100) 4 R51) 24% 51 94% 240 

Tom 7 0100607766001 30. C0M 100.6 64) R54. 5924165 54-943, 955 

Lowen o7 1S eeorcos 145. 00m 1005 | 4 RE7E 2414 © B7 9496 | 265 
20 97720 977708 5S00)  1000m 64. R60) 994% 60 “41,0 285 
ODM O77 2°MNOT 772166 ODN 1006 gat) We R6StmO4ie0 = 63 = 24225305 
24 97724 97774 176.00 100 4 R66 24% 66 4% 320 
26 97726 97776 184.00 100 4 R69 24% 69 4% 340 
Beuu07728 mr 97778ee200008 100) 4) R72 -) 2414" 72 42, 360 
30 97730 97780 210.00 (‘100 4 R75 24% 75 4% 380 a 
S2mo Cho samo ce ne 0000 Pai 78d 80178 4 84009 With Fusible Main\Knite 

Ww . 
= oy 


Type OCK Open Front Panels with Cabinets 


Branches: 2 Wire, 30 Amp. 125 V. Knife Switches, Cartridge Fuses. 


Mains: 125 Volt. 
|__Panel with Cabinet_ | 4... | Capacity | Gutter 
Surface — Panel sath Capinet_| Price a Mains | Space Deep 
Cat.No. Cat. No. Amps. _| Inches Outside | Outside | Inside 


PANELS WITH MAIN LUGS ONLY 


2 Wire Mains 
2 Fuse Branches 


Shipping 
Weight 
Pounds 


SINGLE DOOR 
CABINETS 


97804 97854 $44.00 G0) 4) (RO18 994150 eo ke 
97806 97856 52.00 100 4 R24 24% 24 4% 4115 
—n | 97808 97858 62.00 100 4 R27 241% 27 444% 130 
poet 97810 97860997200. «100 «4 «=~R30) 2414030) 4am as 
as 97812 97862 982.00 200 4 R83 24% 38 4% 160 
* 97814 97864 94.00 200 4 R36 24% 36 4540-9475 
= =| 97816. 97866. 104.00 200 4 R399 1941440039. 9 4i4gemias 
ar | 97818 97868 11400 200 -4 R42 24%, 42 4% 200 
ajo || 97820 97870 124.00 200 4 R45 24% 45 4% 215 
som Be 97822 97872 13400 200 4 R48 241%, 48 41% 295 
“Bisa 97824 97874 14400 200 4 £4R51 24% 51 444% 240 
97826 97876 154.00 200 4 R54 24% 54 414 255 
97828 97878 164.00 200 94 R57. 2414 57. | 4icumagn 
97830 97880 18400 200 4 R60 2414 60 4% 285 
With Main Lugs Only. 32 97832 97882 200.00 200 4 £4R63 24144 63 414 308 
PANELS WITH FUSIBLE MAINS 
4 97904 97954 $58.00 60) "405 R240 90437 Ode id es 
6) 97906 — 97956 9-70.00 © 100 4 6 R330082414 33 el 
8" 97908! 97958 © 80.005) 100. 4°.) R360 62496 g6 undid 
40. 97910. 97960 9000 100 4." "R39. 99414 939. 4s, eres 
12. 97912 97962 110.00 200 4. R45.) 241445 dies 
14 97914 97964 120.00 200 4 R48 241%, 48 414 225 
16 97916 97966 130.00 200 4 R51 24% 51 418 940 
18 97918 97968 140.00 200 4 R54 24% 54 414.0055 
20 97920 97970 150.00 200 4 £49R57 24% 57 44% 270 
22 97922 97972 170.00 200 4 R60 241% 60 4% 285 
94 97924 97974 180.00 200 4 R63 2414 63 414 305 
26 97926 97976 190.00 200 4 R66 24144 66 41% 325 
989897928. 97978 200.00.) 200 45) | R69 1524146 G9mneet 1 
30 97930 97980 210.00 200 4 R72 241% 72 414 360 
32 97932 97982 220.00 200 4 44R75 241% 75 41% 380 
PANELS WITH FUSELESS MAIN KNIFE SWITCH 
4 98004 98054 $65.00 60 94. R83. 9943200133 aes 
6 98006 98056 78.00 100 4 44R39 241%, 39 4% 175 
8 98008 98058 8800 100 4 R42 241%, 42 41% 190 
y 10 98010 98060 98.00 100 4 R45 2414 45 41% 205 
1 12 98012 98062 130.00 200 4 R51 24% #51 4% 240 
: 14 98014 98064 140.00 200 4 R54 241%, 54. 414 255 
a 16 98016 98066 156.00 200 4 R57 2444 57 414° 9965 
<-- 9 18 98018 98068 166.00 200 4 R60 241%, 60 41% 285 
pera 20 98020 98070 176.00 200 4 R63 24% 68 4% 305 
ease 92 98022 98072 184.00 200 4 R66 24% 66 41%4 320 
aaa 24 98024 98074 194.00 200 4 R69 24% 69 44% 340 
26 98026 98076 208.00 200 4 R72 24% 72 4% 360 
28 98028 98078 218.00 200 4 R75 24% 75 4% 380 
AEE GoRACERN ETERS 30 98030 98080 22800 200 4 £R78 24% 78 414 400 
Miri a Soe na 32 98032 98082 238.00 200 4 R81 24% 81 4% 415 
PANELS WITH FUSIBLE MAIN KNIFE SWITCH 
4 98104 98154 $65.00 60a 4° R33. 2414 9.32 eid a 
6 98106 98156 78.00 100 4 R39 2434 39 414 4175 
8 98108 98158 8800 100 4 R42 24% 42 4% 190 
40° 98110) 98160 = 98.000 (t00  mdee R45 241; etn eu og 
12. 98112 98162 130.009) 200.9 94. | V51" 2414.) 510 eb een 
14 98114 98164 140.00 200 4 V54 24% 54 54% 2655 
16 98116 (98166 4156.00 200 4° V57 944% 57  5i, 265 
18 98118 98168 166.00 200) 4 9 9 V60" 2434.) GO nuebimmeees 
20 98120 98170. 176.00 -200 4  V63 2414 ~ 68 “Sip 305 
92 98122 98172 18400 200 4 V66 24% 66 5% 320 
24 98124 98174 19400 200 4 V69 24% 69 5% 340 
26° 98126 98176 230800 200 4° V72 9434 72 "sbi; 360 
28 98128 98178 21800 200 4 #V75 24% 75 5% 380 
30. 98130 98180 22800 200 4 V78 24% 78 5% 400 
With Fusible Main Knife 32°" 98139 98182 938008 200 4 ~V81 984129 81) abuts 
Switch. 
Boe! of 


44 


Pe BENTAMIN'STARRETT eee 
Type OCK Open Front Panels with Cabinets 3 Wire Mains 


Branches: 2 Wire, 30 Amp. 125 V. Knife Switches, Cartridge Fuses. 2 Fuse Branches 
Mains: 125-250 Volt. 
Box Dimensions in Inches 


Panel with | Panel with Cabinet _| List Capacity | Gutter 
—anel th Gabi Flush Price ap Mains | Space High Deep 
Cat.No. | Cat.No. Amps. | Inches Outside | Outside | Inside 


PANELS WITH MAIN LUGS ONLY 


Shipping SINGLE DOOR 
Weight 


Danie CABINETS 


4 98204 98254 $42.00 eq RE ORR TR ric ayy 
6 98206 98256 48.00 GU eee ROLE di 4 et 
8 98208 98258 58.00 60 Ae ROT) 248 27 4144 130 rome 3 i 
10 98210 98260 68.00 GUmmeE4 SEER SON O45c 80 en 4iae 145 ae mi 
12 98212 98262 78.00 60 4 R83 24% 383° 41% 4160 em 
14 98214 98264 90.00 100 4 R386 24% 36 436 TG om 
16 98216 98266 100.00 100 4 R39 241% 39 4% 185 a” 
18 98218 98268 110.00 100 4 R42 24% 42 41% 200 von 
20 98220 98270 124.00 100 4 R45 24% 45 4% 215 — 
92 98222 98272 13400 100 4 R48 24% 48 41% 295 Tae we 
24 982294 98274 14400 100 4 + #&42X¥R51 24% 51 444% 240 tl) 
26 98226 98276 15400 100 4 R54 24% 54 414 255 we! 
28 98228 98278 164.00 100 4 4R57 24% 57 #444% 270 
30 98230 98280 17400 100 4 R60 24% 60 4% 285 
32 98232 982982 19000 100 4 R63 24% #68 4% 305 


With Main Lugs Only. 


4 98304 98354 $52.00 30 ime Rode D4 ig 94 412) 115 

6 98306 98356 62.00 GO MMEAMENER® 7m 4 4 7 4th 130 
8 98308 98358 72.00 CO mens R30 3) ee 4 145 ts Bem 
10 98310 98360 82.00 60mm ROS MEE (eee 390 edie 160 al 
12 98312 98362 92.00 COmmE AN ERSGmD4 7, e360 84140 9175 

14 98314 98364 112.00 100 4 R45 24% 45. 4% 215 

16 98316 98366 12200 100 4 R48 24% 48 4% 225 

18 98318 98368 132.00 100 4 R51 24% 51 4% 240 

20 98320 98370 142.00 100 4 R54 24% 54 4% 255 
992 98322 98372 152.00 100 4 R57 24% 57 4% 270 

294 98324 98374 162.00 100 4 R60 24% 60 4% 285 
26 98326 98376 176.00 100 4 R63 24% 683 4% 305 
28 98328 98378 186.00 100 4 R66 24% 66 4% 325 

30 98330 98380 196.00 100 4 R69 24% 69 4% 345 

32° 98332 98382 «206.00 100 4 R724 24% 72 4146 360 

PANELS WITH FUSELESS MAIN KNIFE SWITCH 

4 98404 98454 $62.00 30m 4 R30 eo e300 4128 9130 

6 98406 98456 72.00 60.) dee R36 O4teme 365m 4146 ~ 160 

8 98408 98458 80.00 60 ee 4 mee ROO meee 9 4117 

10 98410 98460 90.00 60) 4een R42 med 1429 41,190 

12 98412 98462 100.00 60 4 R45 24% 45 4% 205 

14 98414 98464 120.0 100 4 R51 24% 51 4% 240 

16 98416 98466 130.00 100 4 R54 241% 54 41% 255 z 
18 98418 98468 148.00 100 4 R57 24% 57 4% 265 . 
20 98420 98470 158.00 100 4 R60 24% 60 4% 285 ‘e 
22 98422 98472 166.00 '' 100 4 R63 24% 63 4% 305 i 
24 98424 98474 176.00 100 4 R66 24% 66 4% 320 = 
26 98426 98476 184.00 100 4 R69 24% 69 4% 340 

28 98428 98478 200.00 100 4 R72 24% #72 4% 360 

30 98430 98480 210.00 100 4 ##R75 24% #75  # 41% 380 With Fuseless Main Knife 
32 98432 98482 22000 100 4 4=4R78 24% #78 4% 400 Switch. 


PANELS WITH FUSIBLE MAIN KNIFE SWITCH 


4 98504 98554 $62.00 30 4 R30 241% 30 4% 130 
6 98506 98556 72.00 60 4 R36 24% 3 4% 160 
8 98508 98558 80.00 60 4 R39 24% 39 4% 175 
10 98510 98560 90.00 60 4 R42 24% 42 4% 190 
12 98512 98562 100.00 60 4 R45 24% 45 4% 205 
14 98514 98564 120.00 100 4 R51 24% 51 4% 240 
16 98516 98566 130.00 100 4 R54 241% 54 4% 255 
18 98518 98568 148.00 100 4 R57 24% 57 4% 265 
20 98520 98570 158.00 100 4 R60 241% 60 4%, 285 
22 98522 98572 166.00 100 4 R63 241% 63 4¥, 305 
24 98524 98574 176.00 100 4 R66 24% 66 4¥, 320 
26 98526 98576 184.00 100 4 R69 24% 69 4% 340 
28 98528 98578 200.00 100 4 R72 24% 72 4% 360 
30 98530 98580 210.00 100 4 R75 24% 75 414 380 
32 98532 98582 220.00 100 4 R78 24% 78 4% 400 With abe ee ain Knife 
witc 


es BENTAMIN:STARREL) ——_——_—_» 


Galvanized Steel Boxes 
For Standard Lighting Panelboards 


Box Dimensions in Inches 
High Outside 


Shipping 
Weight, Pounds 


Catalog No. List Price Gauge No. 


Wide Outside Deep Inside 


R18 $7.60 14 244% 18 4Y 23 
R21 7.90 14 24, 21 4M 2 

R24 8.20 14 24% 24 AU 27 
R27 8.60 14 24% 27 4% 30 
R30 8.90 14 24% 30 4u, 32 
R33 9.30 14 24% 33 Ay 34 
R36 9.70 14 24% 36 4 37 
R39 10.00 14 24% 39 4Y, 3 

R42 16.80 12 24% 42 4 57 
R45 17.20 12 24% 45 4 Uy 60 
R48 17.70 12 24% 48 41, 64 
R51 18.10 12 24% 51 4% 67 
R54 18.60 i 24%, 54 4u, 70 
R57 19.00 12 24% 57 4% 73 
R60 19.70 12 24% 60 4s 76 
R63 28.50 10 24% 63 4u, 102 
R66 29.10 10 241% 66 4 106 
R69 29.60 10 24% 69 4% 110 
R72 30.10 10 24% ie AU 114 
R75 30.70 10 24% 75 4% 118 
R78 31.30 10 24% 78 4Y 122 
R81 31.80 10 QA 81 4 127 
v42 17.40 12 24% 42 by, 61 
V45 17.80 12 24% 45 BY, 65 
v48 18.30 12 24% 48 bY, 68 
V51 18.80 12 24% 51 by, 7 

v54 19.20 12 24% 54 5, 15 
V57 19.70 12 24% 57 BY, 78 
V60 20.40 12 24% 60 by, 81 
V63 29.40 10 24 63 By, 108 
V66 30.00 10 24% 66 By, 113 
v69 30.60 10 24M, 69 bY, 117 
v72 31.10 10 241% 72 bY, 121 
V75 31.70 10 24% 75 bY, 126 
V78 32.30 10 24% 78 bY, 130 
vai 32.90 10 24% 81 5 134 


Additions to Box Heights Required for Increased Mains 
and Sub-Feeds 


INCREASED MAINS | SUB-FEEDS 
INCREASE OF | | 
: ‘spaciry| MAaIn | FusisLe |Fuseiess| Fusisite | Fusrsun THROUGH | Fusrstp | Fustere 
AMPERES, CAPACITY Lues | Marns | KNIFE | KNIFE BrRuUsH eee | FEED dee Knire | BrusH 
ey To ONLY Onty | Swircn | Swirce | Swircu Se : Luas Nis Swirch | SwircH 
30 60 0 0 BEAU eres 0. | 30 0 ae 3 9” 12) 
30 100 () 6” 6” Om 3” 60 ) a ; iy" iY 
30 200 ) g” g” g” ay Hl 100 0 é g” ley ley 
60 100 0 6” a 3 Stell 200 0 iy ey | 18” 
60 200 0 Q” 6% 6” 6” || Two—3s0A 3 Pole 6” Pe boy 
100 200 0 Be Be 4 3” || One—30A_ |\ xi y 
One—60A 3 Pole 6 15 15 
Two—60A 3 Pole 6” 15" 1s" 
When 400 Ampere Mains are required, the box dimensions will | Two—30A 2 Pole 6” Le 15” 
be furnished on application. | One—30A 2 Pole GY 15 15" 
Norre—For prices on increased mains and sub-feeds, see pages One=- G0 Aaya | al 
ices | Two—60A 2Pole | 6” 15” 15” 
| One— 60A l 9 12” ua Yu 
sn De 2 S 
One—100A |f 2Fole | : _ 
ie! a 


46 


—_——_________ BENJAMIN GTARE 


RET] Da 
SECTION IV 


Increased Capacities and 
Added Equipment 


Important 
Standard bus bar capacities are based on 1924 Under- 
writers Code requirements. Special or increased capa- 
cities and additional equipment will be furnished when so 
ordered, at prices shown in this section. 


Index to Section IV 


URE OSCOMVLOUES* ATOMS UD =I. GCOS = WATG) ean ee ee ee. Page 48 
Pee OSCOMVECVIES ONE ILOKLLCCO SH O= VVatt 6) eee EEE RR cy dn a ts ws Page 49 
ee lOODSeLireciory HI AaMes I NcredsedeG ule?! iS Pace. 622... 55s.) see: Page 50 
Wi COIS ROO CMO TNS 35 | pe ke LORS One Big Oe Ge ee ee Page 51 
ve be 


47 


pa 


2Wire Increased Mains 


On Panels having one of the five different arrangements of Main Terminals shown 


= o MO oo 
(6) 


lord 


WOOOGOOOOC\ 


2 Wire Mains 
125 Volt 


)( 


VOOOOOOOOE 


©) 
@ 


Branches 


© 
eS © 
125 Volt fo) 
© 
Main Lugs Fusible Mains Fuseless Fusible Fusible 
Knife Switch Knife Switch Brush Switch 


100A | 200A | 400A | 100A | 200A,} 400A |} 100A { 200A 400A | 100A |} 200A | 400A 


No. of |Std. Cap. 
Circuits Mains 


400A | 100A | 200A 


Additions to be made to list price of Panelboard and Cabinet for increasing capacity of Mains.* 


4 GOA | $1.50 | $3.00 |$ 7.00] $3.60 | $8.60 $25.00] $8.00 [$18.00 $52.00] $9.00 $21.00|$58.00| $5.20 [$30.00]... 
Gto10/ 100A ie 3.60 | 6.00|......|_8,60| 22.00. .....| 14.00] 50.00)... 16.00} 55.00|......| 26.00|.... 
13t0 32| 200A |..... | asoulh B.O0haee eeetE1S O0la teat. c|°47.001; 20k ma 50. 00) ce 


2 Wire Sub-Feeds 


Providing Additional Extensions to Main Bus Bars in seven arrangements as shown 


5 

: 

© © 

a : © 

2 Wire Mains O 

OF T @ ,2) 

125 Volt ,0) 

Q 
Branches Through Feed with Lugs One Fusible Only, One Fusible Knife One Fusible Brush 
125 Volt Only. Must be same Sub-Feed Switch, Sub-Feed Switch, Sub-Feed 


Capacity as Mains 


60A | 100A | 200A | 3B0A | COA 100A | 200A 100A | 200A 380A 60A | 100A | 200A 


380A | 60A 


Additions to be made to list price of Panelboard and Cabinet after adding for Increased Mains.* 
$1.30 | $1.60 | $2.20 |$15.00$17.00$22.50$30.00|$19.00$23 00/834 .00'$52.00|$38.00$39.00 $44.00)$72.00 


© 


2 Wire Mains 
1255 Viole 


YOOOOOO 


Branches hig X', 
or iW Two Fusible Only, Two Fusible Knife Switch, Two Fusible Brush Switch, 
125-Volt Sub-Feeds Sub-Feeds Sub-Feeds 


| 2-304 | 1-304 N 
1-60A 1-100A 1-100A \ 1-100A 


2-60A | 1-60A | 930A | Sa 


2-60A | 1-604 | 2-30A | ey 


2-60A | 1-60A 


Additions to be made to list price of Panelboard and Cabinet after adding for Increased Mains.* 
$22.00 | $24.00 | $25.00 | $32.00 | $30.00 | $34.00 | $40.00 | $52.00 | $58.00 | $62.00 | $67.00 | $77.00 


*NOTE— See page 46 for additions to box height for Increased Mains and Sub-Feeds and add to list 
price as follows: 
When additions increase height of box to more than 57 inches, add to cover Shoot Bolts and Vault Door 
Handles 3.03 cay ke as ce re Ol ee eee ga ee a eee List Price, $ 9.00 
When additions increase height of box from 40 inches or less to not more than 60 inches, add for increasing 
thickness of steel from No. 14 Gauge to No. 12 Gauge.................... Len Eee List Price, 8.00 
When additions increase height of box between 40 inches and 60 inches to more than 60 inches, add for 
increasing thickness of steel from No. 12 Gauge to No. 10 Gauge................0..-000- List Price, 3.00 
When additions increase height of box from 40 inches or less to more than 60 inches, add for increasing 
thickness of steel from No. 44.Gatige toNo, 10 Gauge eye ee ne List Price, 9.00 


lod 


k--e 


48 


BENTAMIN-STARRETT 


Increased Mains 


On Panels having one 


3 Wire Mains 
125-250 Volt 


Branches 
125 Volt 


@ 
© 
© 
S 
©) 
© 
9 
1) 
© 


©) 


Main Lugs 


ys 
© 
2 
© 
° 
© 
© 
© 


of the five different arrangements 


Fusible Mains 


of Main 


3 Wire 


Terminals shown 


Fuseless | 
Knife Switch 


Knife Switch 


Fusible 
Brush Switch 


Fusible | 


Nae nt eee 60A | 1008 200A | 60A | 100A | 200A | 60A | 100A | 200A | 60A | 100A 2004 | 60A | 100A | 200A 
Circuits | Mains : 
Additions to be made to list price of Panelboard :nd Cabinet for increased capacity of Mains.* 
4 | 380A | $1.00) $1.60] $5.50! $2.00| $6.00/$13.00| $2.50 | $9.00 $30.00) $3.00 |$10.00$34.00| $2.00 | $7.00$36.00 
Gone OUAU ba. o 3 2.50| 5.50|......| 4.50, 12.00)......|_ 8.50) 26.00)......|_ 9.50 31.00)......| 6.50] 34.00 
14 to 30) 100A (ER eres! SENNA ea ET 


seven 


3 Wire 


arrangements as shown 


3 Wire Mains | 
125-250 Volt 


Branches 
125 Volt 


Through Feed with Lugs 
Only. Must be same 
Canacity as Mains 
60A 


100A 200A 


Only, Sub-Feed 


380A 


One Fusible 
Switch, Sub-F 


COA 


100A BOA | 6OA 


One Fusible Knife 


One Fusible Brush 
eed Switch, Sub-Feed 


100A | B30A | 60A | 100A 


$25.00 | $21.00 


$25.00 


3 Wire Mains 
125-250 Volt 


Branches 
125 Volt 


ay eae w OIA Oka 
Be 8 ee 


@ * si 


JOOOOOO 
JOOOOOO 


Two Fusible 
Only, Sub-Feeds 


Two Fusible Knife 
Switch, Sub-Feeds 


Additions to be made to list price of Paneiboard and Cabinet after adding for }ncreased Mains. * 


$1.60 | $2.20 | $3.00 | $17.00 | $20.00 


| $37.00 | $40.00 


$42.00 | $48.00 


Two Fusible Brush 
Switch, Sub-Feeds 


2-30A 1-30A 


1-60A 


2-60 \ 


2-SOA 


2-304 | 1-304 | 


Additions to be made to list price of Panelboard and Cabinet after adding for Increased Mains. 


$25.00 | $30.00 | $37.00 | $33.00 | $42.00 | $55.00 | $60.00 | $63.00 | 


$72.00 


*NOTE— See page 46 for additions to box height for Increased Mains and Sub-Feeds and add to list 


price as follows 


When additions increase height of box to more than 57 inches, add to cover Shoot Bolts and Vault Door 


ETAT GLC Spar eae ete rete nd MOR ae SE IT BO Pe Won ieAialin a, ave ies co's «1 6) whoud, sorte Peusned eat ncmnes List Price, 
additions increase height of box from 40 inches or less to not more than 60 inches, add for increasing 
thickness of steel from No. 14 Gauge to No. 12 Gauge 
additions increase height of box between 40 inches and 60 inches to more 
increasing thickness of steel from No. 12 Gauge to No. 10 : 
additions increase height of box from 40 inches or less to more than 60 inches, 
thickness of steel from No. 14 Gauge to No. 10 Gauge 


a BF 


When 
When 
When 


A 


Guuce aan comes eris 


49 


$ 9.00 

th, 2 Ni Wee. Ato List Price, 8.00 
than 60 inches, add for 

PS Re oe. List Price, 3.00 
add for increasing 

Ua ot nters List Price, 9.00 


é | BENJAMIN STARRETT 


Panels With Meter Loops 


ol aoc 
O-|> == =| 


2 =| 


Additions to be made to list prices of Panelboards and Cabinets. 


- 


FOR 2 WIRE PANELS Z| FOR 3 WIRE PANELS 
Capacity Main Connections, Additional Capacity Main Connections, Additional 
Amperes List Price Amperes List Price 
7 _ | 
48 to 60 $ 4.30 24 to 30 $4.20 
61 to 100 5.20 31 to 60 
101 to 200 7.80 61 to 100 
201 to 400 13.50 i 101 to 200 


Glass Covered Directory Frames 


The steel back of the directory frame is spot welded to the door, the glass and card are held in 
place by a flanged brass frame which is secured to the steel back by four or more brass screws, 


forming a neat, dust proof frame. 


Prices below ARE TO BE ADDED to list price of Panelboard 
and Cabinet. Price includes attaching Directory Frame to inside 
door of cabinet. 


Catalog | Size in Inches | List 
Number i} Wide Ze High | | Price 
SEED: 8 6 3.40 


Cabinets With Increased Gutter Space 


Prices below ARE TO BE ADDED to list price of Panelboard and Cabinet. 


Cabinet Height, 5-in. Gutter 6-in. Gutter 
Inches 
17 to 40 $4.00 $ 7.50 
41 to 50 5.00 8.50 
51 to 60 6.00 10.00 


61 to 85 aE 7.00 11.50 


50 


Weatherproof Cabinets 


For Inclosing Benjamin-Starrett Standard Lighting Panelboards 


an 


se) — a 4 


®= 
e®@= =@e 
= fm) (am) mc) =e? 
O= SS) ~ a@ 


6 7 


The Benjamin-Starrett Weatherproof Cabinet offers a 
practical means of protecting panels against weather conditions 
in outdoor or exposed locations. They are also needed in 
certain types of industrial interiors where dampness is pre- 
valent and atmospheric conditions are unusually severe. 

The Benjamin-Starrett Weatherproof Cabinet takes the 
place of the regular box furnished with standard lighting 
panels and while it is not water tight, when immersed in 
water, it is thoroughly weatherproof and will shed rain or snow. 
The construction also excludes dust from the inside of the 
cabinet. 

Construction. Box and outer trim are of No. 10 gauge galvanized steel. The inner trim is of 
black steel of code gauge thickness. The panel is suspended in box in the manner shown in illus- 
tration. Panelboard is fastened to back of box and brass screws fasten inner trim to steel inner 
flange inside box. Outer trim is rubber gasketed and fastened to box by means of brass screws, and 
outer door closes against rubber gasketed steel rabbet. The vault handle with shoot bolts clamps 
the outer door tightly against the rubber gasketed rabbet at three points. 


The sloping rain shed is a separate piece of galvanized steel and is attached to the two channel 
irons on the back of the box. This hood is packed separately for shipment. The channel iron 
cleats provide air space between cabinet and wall. All exposed screws are brass. 


Amount to be added to list price of Standard Lighting Panelboards and Cabinets 
when Weatherproof Cabinet is specified 


Dimensions of Dimensions of Dimensions of 
Standard Cabinet ADD FOR Standard Cabinet ADD FOR Standard Cabinet ADD FOR 
in Inches WEATHERPROOF in Inches WEATHERPROOF in Inches WEATHERPROOF 
CABINET aa La CABINET ee CABINET 
Height Depth Height Depth Height Depth 
18 4, $28.00 54 4Y/, $67.00 48 5, $58.00 
21 4V/, 30.00 57 4V/> 70.00 51 5, 64.00 
24 4 32.00 60 4 75.00 54 5, 68.00 
PY 4l4 35.00 63 4, 78.00 57 5 71.00 
30 4, 38.00 66 4, 81.00 60 54 76.00 
33 44 40.00 69 4, 84.00 63 5 79.00 
36 4\4 43.00 72 4\, 87.00 66 5 82.00 
39 4, 45.00 75 41/y 90.00 69 5, 85.00 
42 4 48.00 78 4\4 93.00 72 5 88.00 
45 4V/, 51.00 81 4V/ 96.00 75 55 91.00 
48 4l4 57.00 42 54 49.00 78 54 94.00 
51 4 63.00 45 5 52.00 81 5, 97.00 


ol 


———— 


Litiii 


RS Ee a ae et a we ee ee er ee ee ce 


Ett 


BENJAMIN ‘STARRETT <4 


SECTION V 
Meter-Control Panelboards with Cabinets 


ENJAMIN-STARRETT metering panels 
are particularly applicable to office build- 
ings, loft buildings, stores, warehouses and apart- 
ments where electricity is supplied to the tenants 
through separate meters and where changes in 
occupancy require frequent rearrangement of 
the electric service. 


The use of the Selector Type of Benjamin- 
Starrett Meter Panel makes it possible to 
re-meter floor space, quickly and economically. 
No skill is required for this operation and 
changes in metering can be made by the main- 
tenance man, without the use of tools, by simply 
re-positioning the clamp connections on the face 
of the board. 


ay 


fpriss 


Crees 


Canaan 


od 


BENJAMIN STARRETT — | : 


Metering Panels with Cabinets 


Metering Panels and Cabinets 


Benjamin-Starrett Metering Panels are furnished in 
two distinct types as shown, with a choice of three 
styles of cabinets. 


Selector Bar Type Metering Panel 


The selector bar type of panel consists of the required 
number of vertical meter bars with horizontal bus bars 
for each branch circuit. The Benjamin-Starrett clamp- 
ing contactor on each branch circuit bus bar makes it 
possible to connect one or more branch circuits to any 
vertical meter bar. These changes in meter control 
can be made by a maintenance man without discon- 
necting the service, and without the use of tools. 


Wire Connecting Type 


The Wire Connecting Type has the required number 
of meter fuses and the connection from the meter fuse 
through the meter and to the fuse receptacle are made 
on the job by means of wire. This type of panel 
requires more time to rearrange the metering than the 
“Selector Bar Type’’ and it is reeommended only where 
the initial cost of equipment must be given first con- 


sideration. . 
Cabinet Styles 


Made in three styles; (1) with side gutters only 
having no space for meters, (2) with box and trim 
extended for mounting meters on front of trim, (3) with 
box and trim extended for mounting meters in cabinets. 


Specifications 


Bases—Are of the sectional-unit moulded composition 
type, mounted on a one piece heavy gauge steel back. 


Mains—Fusible knife switch with cartridge fuse con- 
nections are furnished as standard equipment. Other 
type of main connections can be furnished if so desired. 
See page 60. 


Branches—All branches are arranged for double pole 
Edison plug fuses. In the case of the Selector Bar type 
each branch circuit 1s equipped with a positive clamping 
contactor which can be readily connected to the desired 
meter bar. In the case of the Wire Connecting type 
the rearranging of metering is done by means of wire. 


Meter Fuses—All meter fuse connections are of the 
cartridge type. Plug type meter fuse connections will 
be furnished if specified. 


Cabinets—Cabinets for Benjamin-Starrett Metering 
panels are of the same general specifications as given on 
pages 6 and 7. Center door over meter panel is 
equipped with Yale combination latch and lock to pre- 
vent unauthorized changes. Doors over meters are 
equipped with latch only. 


Finish—Boxes are galvanized—unpainted. Trims 


are finished in dead black. 


Construction Features 


A—Fusible Main Knife Switch. 


B—Meter Protection Fuse Block with 
Cartridge Fuse Clips. 


C—Screw Clamp Contactor for Con- 
necting Horizontal Branch Circuit 
Bus Bars and Vertical Meter Bars. 


D—Vertical Meter 
insulating shield. 


Bus Bars under 


al Branch Cuireuit Bus 


Bars. 
I’—Branch Circuit Fuse Blocks with 
Edison Double-Pole Fuse Recep- 


tacles. 


G—Sectional Unit Bases mounted on 
Steel Panel Back. 


H— Yale Combination Latch and Lock. 


VA 


lon 


és JAMIN: STARRETT ———_———_——~ 


Type MSB Metering Panels with Cabinets 


Selector Bar Type—without Space for Meters 


2 Fuse 
Branches 
\ 
| NUMBER OF METER BARS AND METER FUSES Box 
Capactiy | waist 
No. of rte. 6 8 10 12 14 aa 18 

Sr [Arems GHT rie UAT an PAA] ine (SRE) ce (ie (2 ae NM] iene as 
Box | Prices | Box | Prices | gox | Prices | pox | Prices | Box | Prices | Box | Prices | Box | Prices side side 
6 60? 1247415120200) een caer ee | cone e acne cea bee =e 3) uaoe sates ae ress | PNR | Se As | ce ee 416 
8 60... 124061" 140200) 26515150. OG) eres yee |e ee st ase ees tae ee EO re | ee 42 414 
10 60 2446) 160.00) -2619170. 001272415180 OO) er aerate ere tee mene eaten reenter es Ue eee UES 414 
12 60 (2444! 180.00] 26°}. 190.0012714) 200,00) 2918210500) seen leeryscee |e etl ante co} eee brmnnerne 48 416 
14 100 |2414| 200.00) 26 | 210.00/2714| 220.00} 29 | 230.00/3014/$240.00) .. |.......]....].......] 54 4% 
16 100 |2444| 220.00} 26 | 230.00)2714| 240.00} 29 | 250.00/3014} 260.00} 32 |$270.00)....].......| 57 416 
18 100 {2414} 240.00) 26 | 250.00/2714] 260.00] 29 | 270.00/3014| 280.00) 32 | 290.00)3314|$300.00) 60 414 
20 100 {241%} 260.00} 26 | 270.00/2714} 280.00] 29 | 290.00/3014] 300.00) 32 | 310.00)3314| 320.00} 63 416 
22 100 {24%} 280.00} 26 | 290.00|2714| 300.00} 29 | 310.00/3014] 320.00) 32 | 330.00)/33!4} 340.00} 66 44 
24 100 |2444| 300.00] 26 | 310.00)2714] 320.00} 29 | 330.00/3014] 340.00} 32 | 350.00/3314} 360.00) 69 414 
26 100 |2414} 320.00} 26 | 330.00/2714] 340.00) 29 | 350.00)3014] 360.00} 32 | 370.00/3314] 380.00) 72 44 
28 100 |24%4} 340.00} 26 | 350.00/2714} 360.00} 29 | 370.00/3014} 380.00} 32 | 390.00/3314] 400.00) 75 4% 
30 100 |2414/ 360.00} 26 | 370.00/2714| 380.00] 29 | 390.00)3014} 400.00} 32 | 410.00/331%]} 420.00) 78 44 
32. | 100 |2414} 380.00] 26 | 390.00|2714] 400.00] 29 | 410.00/3014} 420.00) 32 | 430.00/3314} 440.00) 81 41% 


Norge—Also made in the one fuse type Prices on request. 


54 


— BENJAMIN STARRETT — DA 


Type MWB Metering Panels with Cabinets 


Wire Connecting Type—without Space for Meters 


2 Fuse 
Branches 
om Be 
6 fe 
6a Se 
@2 Be 
68 Se 
6a toe 
68 Ba 
| ae 
| BOX DIMENSIONS IN !NCHES | 
Lem aibaceat Rosvespemmdel (un ceaiors es List Prices wide High | Deep BOX. 
Outside Outside Inside | 
6 60 6 $ 85.00 2414 39 44 R39 
8 60 8 97.00 2414 42 Ale | R42 
10 60 10 108.00 2416 45 414 R45 
12 60 12 130.00 2414 48 416 R48 
14 100 14 148.00 2416 54 414 R54 
16 100 14 158.00 2416 57 46 R57 
18 100 14 167.00 244 60 416 R60 
20 100 14 177.00 2416 63 414 R63 
22 100 18 207.00 2414 66 416 R66 
24 100 18 217.00 9416 69 4Vy R69 
26 100 18 228.00 2416 72 414 R72 
28 100 18 238.00 2414 75 414 R75 
30 100 18 250.00 2416 78 414 R78 
32 100 18 261.00 2414 81 4\4 R81 
Nore—Also made in the one fuse type. Prices on request. 
as 


Or 
Or 


AENTAMINECTARR: 
Pe BENJAMIN STARRETT ea 
Type MST Metering Panels with Cabinets 
Selector Bar Type—Meter Space on Front 
2 Fuse 
BrancheS 
68 Gay ai BS 
ea a ty i ic Be 
. _ oo an 
sot Ges wo 
| 
3  f 
SsoS (ar rs 
NUMBER OF METER FUSES, METER BARS AND METER SPACES _ Box 
Capacity Dimensions 
Ae 6 of te 6 8 10 12 14 16 18 Inches 
ir. | Mains, Width : Width ; Width ; Width : Width g Width ; Width ; High Dee 
List List List List List List Lista meee p 
Amps. ae Prices ee Prices ee Prices Ae Prices aie Prices se prices ae Prices ite A 
6 OO 5243 «160. 00a Ceara 39 44 
8] 601-43 1648000153141$210; 00s ae ees 42 4% 
10 60 | 43 | 200.00/5314} 230.00) 55 |$240.00]....]....... 45 | 44% 
ie 60 | 43 | 220.00|44%| 250.00] 55, | 260.00/5614)$270.00] .. |.......]....]....... 48 44 
14 100 | 43 | 250.00/4414| 270.00] 55 | 290.00/5614| 300.00] 58 |$310.00]....]....... 54 4\6 
16 100 | 43 | 270.00/441%4| 290.00) 55 |} 300.00/5624} 320.00) 58 | 3380.00)6814/$390.00) .. |.......| 57 4l4 
18 100 43 | 290.00/441%4} 310.00} 46 | 320.00)5614} 340.00] 58 | 350.00}6814| 410.00] 70 |$420.00) 60 44 
20 100 43 | 310.00}441%} 330.00] 46 | 340.00/5624| 3860.00] 58 | 370.00]5914| 4380.00] 70 | 440.00} 63 46 
22 100 43 | 330.00]441]} 350.00] 46 | 360.00}561%| 3870.00] 58 | 390.00]/5914} 440.00} 70 | 450.00) 66 416 
24 100 43 | 350.00/441¢} 370.00} 46 | 380.00/4714| 390.00] 58 | 410.00]5914| 460.00} 61 | 470.00} 69 44 
26 100 | 43 | 370.00)441<| 390.00} 46 | 400.00]4714} 410.00) 58 | 480.00/591%4} 480.00} 61°} 490.00) 72 44 
28 100 | 48 | 390.00/441<| 410.00] 46 | 420.00/4714} 4380.00] 58 | 440.00]5914} 500.00] 61 | 510.00) 75 414 
30 100 | 48 | 410.00/441%] 430.00} 46 | 440.00]4714] 450.00] 58 | 460.00/5914] 520.00] 61 | 530.00) 78 44 
32 100 43 | 480.00/4414| 450.001 46 | 460.00/471<] 470.00} 49 | 480.00/5914| 540.00] 61 550.00) Sl 4l4 
Norr—Also made in the one fuse type ‘Prices on request. 
7 5 ; 
lo) 


56 


ee BENJAMIN: STARRETT ak, 


Type MWT Metering Panels With Cabinets 


Wire Connecting Type—Meter Space on Front 


2 Fuse 
Branches 
ng 
| NUMBER OF METER FUSES AND METER SPACES _ Box 
| Capacity 1 = | Dimensions 
No.of | of 6 & 10 12 14 16 | 18 Inches 
Cir. ane Maeed List ae List wath List Wicd List oe List wee List bela List | Fligh Dees 
| | Box | Prices | Box | Prices Box, Prices | Box | Prices | Box | Prices | Box | Prices | Box | Prices | side aida 
CRE OU aed 04 OU Meee nies Rees aire eet ee | ANAS ea ell one) Ree sta Pac |e cannes] ae" fhe oeeee| OO 4l4 
8 | HO) |) | SOL) evs SCO oo We son aoell oot oa oc cll naiieaansell me goiter) cer (llGemo osroe 42 Als 
10 COME OM 2eOUlao 2a 202200 2atp2 004 0G aren enemies PLO Meer | ae [eaaecun lls saalema ted |) “40 44 
2) | 4a} | USS. OU) 43 | 2G ON) |) ZOO! ays ThE so ease call oo ecocas al] a2 es orl ee te) 416 
14108100 0 |43°|' 208.00). 43 | 226.00) 52 | 240.00) 52.) 244.00) 52 [$248.00] 2 }.....-.] .. |.......| 54 44 
16 LOOM 4392227 00/843" 16240700) 52 1. 254700).52) 17258,.00) 52 | 262.00) 61 1$308. 00)... |..-....) oF 416 
18 100 | 43 | 236.00] 43 | 254.00] 43 | 258.00} 52 | 272.00} 52 | 276.00} 61 | 322.00) 61 {$326.00} 60 4l4 
20 100 | 43 | 250.00] 43 | 268.00] 43 | 272.00] 52 | 286.00} 52 | 290.00} 52 | 336.00} 61 | 340.00) 63 46 
22 | 100 | 43 | 264.00] 43 | 282.00] 43 | 286.00) 52 | 290.00] 52 | 304.00) 52 | 340.00) 61 | 344.00) 66 {16 
24 100 | 43 | 278.00] 43 | 296.00] 43 | 300.00) 43 | 304.00] 52 | 318.00] 52 | 354.00) 52 | 358.00) 69 114, 
26 100 | 43 | 292.00} 43 | 310.00} 43 | 314.00} 43 | 320.00} 52 | 332.00} 52 | 368.00) 52 | 372.00) 72 114 
28 100 | 43 | 306.00} 43 | 324.00] 43 | 328.00] 43 | 334.00} 52 | 336.00} 52 | 382.00) 52 | 386.00) 75 AV, 
30 | 100 320.00} 43 | 338.00] 43 | 342.00} 43 | 348.00} 52 | 350.00} 52 | 396.00) 52 | 400.00) 78 4l4 
32 | 100 | 43 | 334.00} 43 | 352.00] 43 | 356.00] 43 | 362.00] 43 | 364.00} 52 | 410.00] 52 | 414.00) 81 Ale 
Norre—Also made in the one fuse type. Prices on request. 
oF 


Tt 


Or 


58 


gs 
es e e 
Type MSC Metering Panels with Cabinets 
Selector Bar Type—with Meter Space in Box 
2 Fuse 
Branches 
tS | i ¥ NUMBER OF METER FUSES, METER BARS AND METER SPACES _ Box 
Capacity | Dimensions 
No. of eH k 6 8 10 12 14 16 18 Inches 
ir. | Mains, (Width A Width : Width ‘ Width : Width , Width : Width} |. High Deep 
Amps. | List List List List List (ui L 
ah | on Prices ae Prices oe, Prices aes Prices oe prices a Press Price pie Li. 
6 60 AS [GS AD CO. oc alles cua ce 39 7 
8.) 360) 143° 1919000153 418220 00 eee | eee aene ae eee eee 42 fi 
10 60 AB || PAO OOS A) PAO CO) iss (EPO. OO... ooo. 5s all os ecco oealececthssss- 45 7 
12 60 | 438 | 230.00/44%) 260.00] 55 | 270.00/5614|$280.0C] .. |.......|....]....... 48 A 
14 100 | 438 | 260.00/4414| 280.00} 55 | 300.00/5614) 310.00] 58 |$320.00]....]....... 54 7 
16 | 100 | 43 | 280.00/4424) 300.00} 55 | 320.00/5614| 330.00] 58 | 340.00/6814|$400.00] .. |.......| 57 7 
18 |} 100 | 43 | 300.00/4414] 320.00} 46 | 330.00]5614| 350.00] 58 | 360.00/6814| 420.00} 70 |$430.00) 60 7 
20 | 100 | 43 | 820.00/441%4] 340.00] 46 | 350.00)5614] 370.00] 58 | 380.00/5914| 440.00] 70 | 450.00} 63 7 
22 ; 100 | 43 | 340.00/441%4| 360.00} 46 | 370.00/5614] 390.00] 58 | 400.00/5914] 460.00] 70 | 470.00) 66 7 
24 | 100 | 48 | 360.00/44%] 380.00} 46 | 390.00]4714] 410.00] 58 | 420.00}/5914] 480.00} 61 | 490.00) 69 7 
26 = 100 | 43 | 380.00/4414} 400.00} 46 | 410.00/4714] 420.00} 58 | 440.00)5914} 490.00) 61.) 500.00) 72 7 
28 | 100 | 43 | 400.00/4414] 420.00} 46 30.00/4714] 440.00} 58 | 460.00/5914] 510.00} 61 | 520.00) 75 7 
30 | 100 | 43 | 420.00/44%4} 440.00) 46 | 450.00/4714} 460.00] 58 | 480.00|5924} 530.00) 61 | 540.00) 78 7 
32 | 100 | 43 | 440.00/4414} 460.00] 46 | 470.00 4714| 480.00] 49 | 490.00/5914} 550.00] 61 | 560.00} 81 fi 
Note—Also made in the one fuse type. Prices on request. 
ine 


pa 
e e e 
Type MWC Metering Panels With Cabinets 
Wire Connecting Type—With Meter Space in Box 
2 Fuse 
Branches 
Be ot 
Ba aI 
ra = 
~ ce 
= Oe 
a! are aa 
; NUMBER OF METER FUSES AND METER SPACES ted Slues 
Capacity ic ae imensions 
Mee of of | 6 8 10 12 14 16 18 | Inches 
irs . : = = 5 ; ; A A 
piatns Width List Width fie \Widthl © ict Width eee |Width|ier. Width na Width List | High Dees 
| Box Prices Box | Prices | pox | Prices | poy | Prices | poy | Prices | Box | Prices | Box Prices side side 
6 GOs 19154) 00) ie eee “hous: Seo Sha toa Pert be es ie bean area Bann Renan abe? ae 39 i 
8 60 | 48} 168.00} 52 |$198.00) .. ]....... 2, HIS LRe Bact We Syl ae ee eg) eae | Leoariee eran fee ena sree ts Pee 49 7 
10 GO) |) 43 |) US. CO) 1, SAN OW EO PANS. CO)! se eee eae cll oe lesssceell oo [esocesal ce cue eo 45 ai 
12 RO) || 453 i) Oy) SS || SAR OO! BB. |] PROS} GR [PVBYE CO) oo lech oncoll ac |ecusos ci! ox | 4S di 
14 100 43 | 218.00) 43 | 236.00) 52 | 250.00) 52 | 254.00) 52 |$258.00| .. |....... | 54 7 
16 100 | 43 | 232.00] 43 | 250.00] 52 | 264.00] 52 | 268.00] 52 | 272.00] 61 $318.00) .. |.......] 47 | i 
18 100 43 | 246.00] 43 | 264.00] 43 | 268.00] 52 | 282.00} 52 | 286.00} 61 | 332.00] 61 |$336.00) 60 7 
20 100 43 | 260.00] 43 | 278.00] 43 | 282.00] 52 | 296.00] 52 | 300.00} 52 | 346.00] 61 | 350.00) 63 7 
22 100 43 | 274.00} 43 | 292.00] 43 | 296.00] 52 | 310.00] 52 | 314.00} 52 | 360.00} 61 | 364.00) 66 7h 
Ame LO) 43 | 288.00! 43 | 306.00] 43 | 310.00} 43 | 324.00] 52 | 328.00} 52 | 374.00) 52 | 378.00} 69 ii 
26 | 100 43 | 302.00} 43 | 320.00] 43 | 324.00! 43 | 328.00] 52 | 342.00] 52 | 378.00} 52 | 382.00) 72 7 
28 100 43 | 316.00] 43 | 334.00] 43 | 338.00] 43 | 342.00] 52 | 356.00] 52 | 392.00} 52 | 396.00} 75 7 
30 100 43 | 330.00! 43 | 348.00] 43 | 352.00! 43 | 356.00] 52 | 370.00] 52 | 406.00} 52 | 410.00} 78 7 
32 | 100 | 43 | 344.00] 43 | 362.00] 43 | 366.00] 43 | 370.00] 43 | 374.00] 52 | 420.00] 52 | 424.00) SI fl 


Note—Also made in the one fuse type. Prices on request. 


Se  _eaaeeied 
59 


Metering Panels and Cabinets 
Deductions and Additions 


Main Connections 
If lugs only, or fuse only, are desired in mains make following deductions from list price: 


Deductions from List Price 


30 Amp. 200 Amp. 100 Amp. {| 200 Amp. 


Lug Only Mains..... | $2.60 | $4.60 | $6.00 | $7.30 || Fusible Only Mains... $4.90 | $6.00 


Meter Fuse and Branch Circuit Connections 
Additions to List Price 


hi For Each | Additional Witsoe 

magemy sac" | agaiona | Aasteral | Mesias | ofe%s | Facet | owmars | sulthtrn 

TYPE Meter Bars pits ame Meter Disco eedng Eranehes Per pair oF Ones 
aren ee Dace Switches Branches Dar babe 
MWB... ..| $5.00 $6.00 i; $2.00 $20.00 $20.00 $8.00 
MSB ee oe het ace 2.00 30.00 30.00 8.00 
MWT. be ee eA : rene 2.00 20.00 20.00 8.00 
MST. % : 2.00 30.00 30.00 8.00 
MWC. .... me Loe 2.00 20.00 20.00 8.00 
MSC . The Re eee ee Bo oat : 2.00 30.00 30.00 8.00 


Diagram of Connections 


For 16-Branch Circuit, 8-Meter Fuse 
and 8-Meter Bar, Meter Control Panel 
Board Installation. Four 2-Wire and 
Two 3-Wire Meter shown. 


In wiring buildings where 
metering panels are to be 
installed, in order to avoid 
difficulties in re-metering 
space, a separate circuit 
must be provided for each 
unit of space which may 
be rented separately or 
in combination with other 
units. 


SECTION VI 


Cabinets and Boxes 


For Use As Telephone Cabinets 
Junction and Pull Boxes Only 


In this section are shown three different types of 
Benjamin-Starrett Cabinets and Boxes which are 
designed for use as Telephone Cabinets, Junction 
Boxes and Pull Boxes. 


These boxes are not carried in stock but will be built 
up according to the standard specifications shown on 
the following pages. 


Index to Section VI 


Type A Cabinets (Box and Door) for Telephone Cabinets, Junction and 


JP RP BTN CMO Ss SAPS eae ee SR Rn a ee ee re On ete Page 62 
Type B Cabinets (Box and Trim) for Telephone Cabinets, Junction and | 
Se MURL SOLE SLO TCL Sam tn ay MeCN PRP oc Aran See e201 cee UMAGA od Rete soyis Fok” Sige setog ats Page 63 
Ome OVC OMY UNCON AANOMLULLe DOXES ONLY nue el. ee Gis ae = - Page 64 


iol 


61 


BENJAMIN STARRETT 
Type A Cabinets (Box and Door) 


For Telephone Cabinets, Junction and 
Pull Boxes Only 


Construction.—Box is formed of one piece of galvanized steel. 
Corners are overlapped and riveted. Has 24-inch inward flange on 
all four edges. 

Door is formed of one piece of galvanized steel the same thickness 
as the box. Door has flange on all four edges. Door hinges are 
riveted to the side of the box. Furnished with vault handle. 


Thickness of Steel.—Boxes and doors are of Code thickness 
steel. For increased thickness see price schedule at bottom of page. 

Depth.—Type ‘“‘A”’ Cabinets are regularly furnished 41% inches 
deep. For additional depth up to and including 12 inches, see price 
schedule at bottom of page. 


Drilling.—Type “A” Cabinets are furnished without drilling 
for conduit unless template accompanies order. 


Finish.—Galvanized and not painted. 


List Prices—Type A Cabinets 


For Telephone Cabinets, Junction and Pull Boxes Only 


Saant of OUTSIDE WIDTH OF BOX, INCHES DOUBLE DOORS, INCHES 
Box, Inches 4 914 12% lé 26144 2814 3116 3414 
6 ||$ 8.20 |$ 8.50 |$ 8.80 |$ 9.10 $19.80 | $20.30) $20.901 | amy it enn nl 
1014 8.50 | 8.80] 9.20 | 9.60 20.50 | 21.10 | 21.80 | $22.60 | $23.50 | $24.50 
14, 8.80 | 9.10 | 9.60 | 10.10 21.20 | 21.90 | 22.70 | 23.60 25.60 
10° 471, 9.10 | 9.40 | 10.00 | 10.60 21.90 | 22.70 | 23.60 | 24.60 26.90 
201/, 9.70 | 10.40 12.80 | 13.60 | 22.70 | 23.50 | 24.50 | 25.60 28.10 
93 1/, 10.20 | 10.80 13.50 | 14.40 | 23.50 | 24.20 | 25.40 | 26.60 29.30 
261, || 11.20 | 12.00 | 12.65 | 13.30 | 14.20 | 15.40 | 24.30 | 25.10 | 26.30 | 27.60 33.70 
29V, || 11.60 |_12.40 | 13.15 | 13.90 | 14.90 |_ 16.20 |_25.10 | 25.90 | 27.20 | 28.60 [34.50 |_35.40 
14 | 32% || 12.00 | 12.80 | 13.65 | 14.50 | 15.60 | 17.00 | 25.90 | 26.70 | 28.10 [ 35.00 | 36.00 | 37.10 
35), || 12.40 | 13.20 | 14.15 | 15.10 | 16.30 | 17.80 | 26.70 | 27.50 [ 35.20 | 36.30 | 37.50 | 38.80 
| 38 || 12.80 | 13.60 | 14.65 | 15.70 | 17.00 | 18.60 | 27.50 [_35.10 | 36.30 | 37.60 | 39.00 | 44.80 
431/, .....| 21.70 | 23.40 | 24.70 | 25.30 | 36.00 | 36.90 | 38.50 |_ 40.20 [45.00 | 62.10 
461, "....[.......| 22.30 | 24.10 | 25.50 | 26.20 | 36.90 | 37.80 41.50 | 46.50 | 63.60 
491/, -.. | 22.90 | 24.80 | 26.30 | 27.10 | 37.80 ; 46.90 | 58.00 | 65.10 
I Saya -..| 23.50 | 25.50 | 27.10 | 28.00 | 38.70 | 39.60 | 47.00 | 48.20 | 49.50 | 66.60 
551, _.| 24.10 | 26.20 |_27.90 | 28.90 | 39.60 J 46.80 | 48.10 | 49.50 | 51.00 | 68.10 
58 1/4 _.|_ 24.70 | 26.90 |_ 28.70 |_ 29.80 | 46.80 |_47.80 | 49.20 | 50.80 | 52.50 |_69.60 
6115 31.50 | 33.30 | 34.80 | 47.80 | 48.80 | 50.30 | 52.10 | 54.00 | 71.10 
10 
79Ge lee 40.95 | 56.40 | 59.00 | 60.90 | 63.90 | 67.00 | 80.10 
| PE 42.10 | 58.20 | 61.00 | 63.00 | 66.20 | 69.50 | 81.60 
8514 68.50 | 72.00 


TO TO TO 
7 INCHES 9 INCHES 12 INCHES 


16 Gauge.... 


14 Gauge. . 
12 Gauge..... 
10 Gauge..... 


$ 3.70 $ 6.40 
br25 9.00 
9.10 15.45 

11.50 19.00 


$ 1.90 
PAS 
4.85 
6.50 


~ BENAMIN-STARRERT ———___________.. 


Type B Cabinets (Box and Trim) 


For Telephone Cabinets, Junction and 
Pull Boxes Only 


Construction.—Box is formed of one piece of galvanized steel. 
Corners are overlapped and riveted. Has 24-inch inward flange on 
all four edges which is drilled for attachment of front. 

Trim is made of one piece of sheet steel, overlapping box 1 inch 
on all four sides. The door is cut out, leaving a 3-inch mat all around. 
Door is equipped with vault handle only. 


Thickness of Steel—Boxes and trim are of Code thickness steel. 
For increased thickness see price schedule at bottom of page. 


Depth.—Type B Cabinets are 4% inches deep. For additional 
depth up to and including 12 inches see price schedule at bottom 
of page. 

Drilling.—Type B Cabinets are furnished without drilling for 
conduit unless template accompanies order. 


Finish.—Boxes are galvanized steel—unpainted. Trims are 
painted dead black. 


List Prices—Type B Cabinets 
For Telephone Cabinets, Junction and Pull Boxes Only 


U.S. Outside OUTSIDE WIDTH OF BOX, INCHES DOUBLE DOORS, INCHES 
Guage | Height of 
Steel |Box, Inches 2614 3719 3 
6 $22.90 er ew 
10% “23.70 | $24.30 | $24.80 | $53.35 | $54.60 | $56.05 
14% |... 24.50 | 25.30 | 25.90 | 55.55 | 57.00 | 58.65 
De a7 1/55 © 30 | 25.90 | 26.30 | 27.00 | 57.85 | 59.50 | 61.35 
20, 26.70 | 27.30 | 28.00 | 60.25 | 62.10 | 64.15 
231, 27.50 | 28.30 | 29.00 | 62.75 | 64.80 | 67.05 
en |a26 5 28.40 | 29.30 | 30.10 | 65.35 | 67.60 [74.40 
29), ||... 2 60 | 29.40 | 30.30 | 31.20 | 68.05 [7475 |_77.40 
[Am ESO; 30.40 | 31.30 | 32.30 [75.10 |_77.75 | 80.50 
35Y, 31.40 | 32.30 [39.30 | 78.10 | 80.85 | 83.70 
38, 32.40 [39.40 | 40.70 |_81.20 | 84.05 |_90.70_ 
CE es ee 40.70 | 42.10 | 43.50 | 87.70 100.05 | 116.65 
AG/A9 | See | Se 8S | 585: 10_|_41.60 | 43.20 [ 44.80 [91.10 | 102.92 | 120.05 
10 /5% Sana |< See | ee | 839. ; 10 | 42.50 om 46.10 | 102.35 | 105.85 | 123.50 
129 501%, 43.40 | 45.40 | 52.20 1105.30 | 108.90 | 126.90 
55Y, 44.30 [52.20 | 53.70 [108.35 | 112.05 | 130.30 
56.50 | 61.20 | 65.20 {111.60 |115.40 | 133.75 
ae 62.30 | 64.60 | 67.00 | 115.05 |118.95 | 140.50 
Sy: |) oo |e 69.10 | 71.60 |_74.80 [121.85 [125.85 | 145.35 
| . | 70.40 | 73.00 | 75.60 | 129.95 [134.05 | 150.20 
71.90 | 74.20 | 77.20 | 135.90 |140.10 | 155.10 
ity EVAR | Rn eee ee 72.95 | 75.70 | 78.70 | 141.85 |146.15 | 161.25 
74.00 | 77.20 | 80.20 | 147.80 | 152.20 


B56 eneeen (Rue tee [coset (eres | ey 30 | 78.50 | 81.70 | 84.70 | 165.65 | 170.25 


Add for Increased Depth From 414 Inches Deep Add for Increased Gauge 


TO TO TO TO nti nrasin | aan Overs, |lwe.T Ome |S) TON: 
6 INCHES | 7 INCHES | 9 INCHES | 12 INCHES 14 GAUGE | 12 GAUGE | 10 GAUGE 
16sGauge. | $1. : : 2 ee $1.00 $8.75 $9.75 


14 Gauge... 
12 Gauge. . 
1OiGaligemea. 


Box and Cover 
For Junction and Pull Boxes Only 


Construction 

Box is formed of one piece of galvanized steel. Has 34-inch 
inward flange on all four edges which is drilled for attachment 
of cover. 

Cover is made of one piece of galvanized steel, the same 
thickness as the box. Cover is fitted with machine screws for 
fastening to box. 

Thickness of Steel 


Boxes and covers are of Code thickness steel. For increased 
thickness see price schedule at bottom of page. 


Depth 
Boxes are 41% inches deep. For additional depth up to and 
including 12 inches see price schedule at bottom of page. 
Drilling 
Boxes are furnished without drilling for conduit unless 
template accompanies order. 


Finish 


Galvanized—unpainted. 


List Prices—Box and Cover 
For Junction and Pull Boxes Only 


Outside OUTSIDE WIDTH OF BOX, INCHES 


Gauge | Height of : 
Steel_|Box,Inches|| 614 914 1214 1514 2214 2414 2614 2814 3114 3414 3714 4014 
614 || $.6:30) 1 $6.70. ||$ 7.00) |S) 7.407) $ 72808) S$ e805 1 $89/90) i S110:308 | S1O!GON | cee ee |e | eee 
1014 6.60 7.10 7.40 7.90 8.30 8.70 | 10.40 | 10.90 | 11.20 | $11. $12.30 | $12. 
1414 6.90 7.50 7.80 8.40 8.80 9.30 | 10.90 | 11.50 | 11.80 } 12.40 | 13.00 | 13.70 
Loe e713 7.20} 7.90 | 8.20] 8.90) 9.30] 11.00] 11.70 | 12.10 | 12.50 | 13.20 | 13.80 | 14.10 
2014 7.50 8.30 8.60 9.40 | 11.20 | 11.70 | 12.30 | 12.70 | 13.20 | 13.90 | 14.40 |. 15.00 


23, 8.10 | 8.70 | 9.00 | 11.30 } 11.80 | 12.40 | 12.90 | 13.30 | 13.90 | 14.70 | 15.40 | 16.00 
26, 9.90 | 10.40 | 10.80 | 11.80 | 12.40 | 13.10 | 13.60 | 14.00 | 14.60 | 15.50 23.20 
291% || 10.20 | 10.80 | 11.30 | 12.30 | 13.00 | 13.80 | 14.30 | 14.70 | 15.30 | 16.30 } 23.50 | 24.30 
14 |.32\% || 10.50 | 11.20 | 11.80 | 12.80 | 13.60 | 14.50 | 15.00 23.90 | 24.70 | 25.50 
35% || 10.90 | 11.60 | 12.30 | 13.30 | 14.20 | 15.20 | 15.70 24.10 | 25.90 | 26.70 
B 14.80 | 15.90 25.80 | 26.60 } 29.50 
il ee ee 26.20 | 27.20 |~ 30.50 | 45.75 
46 //, ios ee | 27.90 | 31.20 | 46.80 
yo | 49% |e 27.60 | 30.50 | 31.90 | 47.85 
2 Wim ctr. Fe eae 29.80 | 31.20 | 32.60 | 48.90 
at) Peal | Bee eee 30.50 | 31.90 | 33.30 | 49.95 
58, 31.20 | 32.60 | 34.00 | 51.00 
Oils |e: eames 30.70 | 31.90 | 33.40 | 34.80 | 52.20 
5 DE Ae ee 26.90 | 28.70 | 29.70 | 31.40 | 32.60 | 34.00 | 35.40 | 53.10 
6710 ee a: | ine fe _.| 29.50 | 30.60 | 32.60 | 34.20 | 35.60 | 37.00 | 55.50 
70, 30.30 | 31.50 | 33.40 | 35.00 | 36.40 | 37.80 | 56.70 
Add for Increased Depth From 41% Inches Deep Add for Increased Gauge 
0 


TO TO TO TO 
6 INCHES 7 INCHES 12 GAUGE | 10 GAUGE 


16 Gauge......| $ 1.00 $ 1.90 
14 Gauge..... 1250 An On| ee 2D mee | eee OO ean | | Ga Cee | ee 8.00 9.00 
l2tGaugemaes. 20D 4.85 2.80 


Lee ef | INS BEL pe tt] |e ee ot ed fe te 


10 Gauge. . 4.00 6.50 


— BENJAMIN STARRETT oo 


SECTION VII 


Distribution Panelboards and Cabinets 
Switchboards 


Illustrated in this section are a few of the many 
types of special distribution panels and cabinets that 
have been built to meet the requirements of our 
customers. Special panels will be built for any capa- 
city or number of circuits, or for any voltage; all in 
accordance with specifications and requirements sub- 
mitted to us. 


The Benjamin-Starrett organization is also pre- 
pared to build switchboards in either Live Front or 
Dead Front Types to meet any specifications sub- 
mitted by our customers. 


Estimates will be gladly furnished on your special 
panelboard and switchboard requirements. 


ese _______— PSyauy sieekey] ——____» 


Distribution Panelboards and Cabinets 


Live Front Panel 
with 
Type ‘‘A’’ Cabinet 


Il (3119) tat 
oo @ 


fff 


Illustrated is a lighting dis- 
tribution panel having main lugs 
only and fusible knife switch 
branches. Panel is arranged for 
solid neutral connections. 


AY 


ae 


fol tsi 
pa 


Type ‘‘A’’ Cabinet 


al 
fl 


This panel is mounted in a 
Type ‘‘A” Code Gauge Steel 
Cabinet, which is designed for 
surface mounting where all wires 
are brought in directly opposite 
the circuit to which they are to 
be connected. 


Cross Section of Type ‘‘A’’ Cabinet. 


Live Front Panel 
with 
Type ‘‘B’’ Cabinet 


To the right is shown a power 
distribution panel having fusible 
main knife and fusible knife 
switch branches. 


Type ‘‘B’’ Cabinet 


This panel is mounted in a 
Type “B” Code Gauge Steel 
Cabinet, which is designed for 
flush mounting where all wires 
are brought in directly opposite 
the circuit to which they are to 
be connected. 


Cross Section of Type ‘*‘B’’ Cabinet. 


a SSSSSSSSSSSSMm9090E SS SS SSS RS 


66 


<—__—________BEWAMIN'SI 


Distribution Panelboards and Cabinets 


Live Front Panel 
with 
Type ‘‘C”’ Cabinet 


At the left is illustrated a 
lighting distribution panel 
having main lugs only and 
fusible knife switch branches. 


Type ‘‘C’’ Cabinet 


This panel is mounted in a 
Type “C” Code Gauge Steel 
Cabinet which is arranged for 
surface mounting. Cabinet 
has wiring gutters on all four 
sides, thus permitting the 
entrance of feeder and branch 
circuit wires wherever con- 


venient. 


Cross Section Type ‘‘C’”’ Cabinet 


Live Front Panel 


with 
Type ‘‘D’’ Cabinet | oe 
At the right is shown a polarity lee ven ten ty g4 FSU HEE ES HOE 138 Fed te tc 
type distribution panel with main j j 
lugs only and with fuse only con- Lh 


nections in the branches. This 
type of panel is recommended 
where amount of space in which 
panel is to be installed is limited. 


fee ee ee eee ee oF fee ee ee eee ee oF 


Type ‘‘D’’ Cabinet 


This panel is shown mounted in 
a Type ‘D” Code Gauge Steel 
Cabinet arranged for flush mount- 
ing. Cabinet has wiring gutters 
on all four sides. 


Goxe O32) G © |. 6, °e' "0 g 
BSP EPBE PEPE et 


Ost O30 P3100 0 Et i bat 


’ 
> 
+ 
° 
° 
. 
° 
° 
° 


BU BEBE 


-— 
Tal 
~ 
— 
a 
- 
—_ 
" 
— 
- 
tal 
- 


BEBE 


O31 13 
Wil 


QB 
) 1 io 


A 
{i 
ra 


Cross Section Type ‘‘D”’ Cabinet 


67 


Cross Section of Type ‘‘G”’ Cabinet. 


Live Front Panel 
with 
Type ‘‘H”’ Cabinet 
At right is illustrated a special com- 
bination distribution panel for power 
and light. 


Type “H’’ Cabinet 
This panel is mounted in a Type “‘ H”’ 
Cabinet of Code Gauge Steel which is 
arranged for flush installations. This 
type of cabinet has wiring space 
between back of panel and box. Con- 
nections are on back of panel. 


Cross Section of Type ‘‘H’’ Cabinet. 


Se, 


Live Front Panel 
with 
Type ‘‘G”’ Cabinet 


At left is shown a special 
distribution panel on which 
are mounted two types of 
branch circuit equipment. 


Type ‘“‘G”’ Cabinet 


This panel is mounted in 
Type‘ G” Cabinet of Code 
Gauge Steel which is 
arranged for surface in- 
stallation. This type of 
cabinet has wiring space 
between back of panel and 
box. Removable plates are 
provided on both sides of 
cabinet to permit easy 
access to connections on 
back of panel. 


| 


Distribution Panelboards and Cabinets 


Interlocking Safety Front Panelboard 


The Benjamin-Starrett Interlocking Safety Type Distribution Panelboard, illus- 
trated below, offers the advantage of perfect safety to the operator at all times. 
Switches are of the laminated brush contact type. Over each set of branch circuit 
fuses is an individual door equipped with an Interlocking Mechanism. This 
mechanism prevents opening of the door when switch is in ‘‘On”’ position, as well as 
operation of the switch when door is open. 


Type ‘‘C”’ Cabinet 


Panel is shown mounted in a Type “C”’ Code Gauge Steel Cabinet. This Cabinet 
has wiring gutters on all four sides. 


Front View of Interlocking Safety Front Type Panelboard, 
with Cabinet. Three Fuse Compartment doors opened. 


pS 


i 
69 


— 


i= : BENJAMIN STARRETT 


Benjamin-Starrett Switchboards 


Back View 


Front View 


This is one of the many 
switchboards built by the 
Benjamin - Starrett organi- 
zation according to speci- 
fications and requirements 
of customers. Illustration 
shows combination primary 
and secondary switchboard 
for large hospital building. 
On this particular board the 
fuses are mounted on the 
rear and are accessible only 
to the authorized mainten- 
ance man. 


BENJAMIN :STARRETT * 


Benjamin-Starrett Switchboards 


os |. if. UT : : 


uM NOM. ope 


ee py 


Bab 


“4 4 


Front View 


Another style of switch- 
board designed and built 
by the Benjamin-Starrett 
organization for a _ large 
bank and office building. 
All terminals on this board 
are brought to the bottom 
by means of bus _ bars. 
Terminal rack and pull box 
with slate cover are pro- 
vided at bottom as shown. 


Back View 


BF 


ws 
71 


p 


2 BENJAMIN STARRETT 


Benjamin-Starrett Switchboards 


Switchboard illustrated above was 

built by the Benjamin-Starrett organ- 

Back View ization to meet the needs of a large 
department store. Designed so that 
all terminal connections are made at 
the top of the board. 


i: be 


72 


SECTION VIII 


Numerical Index 


Catalog List Catalog List Catalog List Catalog List Catalog List 
Page No. Price Page No. Price Page No. Price Page No. Price Page No. Price 
46 R-18 $ 7.60 20 52140 $156.00 20 52540 $236.00 21 52940 $156.00 21 53340 $236.00 
46 R-21 7.90 20 52144 172.00 20 52544 248.00 21 52944 172.00 21 53344 248.00 
46 R-24 8.20 20 52148 182.00 | 20 52548 260.00 21 52948 182.00 21 53348 260.00 
46 R-27 8.60 20 52152 192.00 | 20 52552 272.00 21 52952 192.00 21 53352 272.00 
46 R-30 8.90 20 52156 206.00 | 20 52556 286.00 All 52956 206.00 21 53356 286.00 
46 Beso 9.30 20 52160 222.00 | 20 52560. 302.00 21 52960 222.00 21 53360 302.00 
46 R-36 9.70 20 52204 62.00 | 20 52604 76.00 21 53004 62.00 21 53404 76.00 


46 R-39 10.00 | 20 52208 74.00 | 20 52608 93.00 | 21 53008 74.00 | 21 53408 93.00 
46 R-42 16.80) 1920) 52212 86.00 | 20 52612 105.00 | 21 53012 86.00 | 21 53412 105.00 
46 R-45 70) || 20 RANG 102.00 | 20 52616 130.00 |} 21 53016 102.00 | 21 53416 130.00 


46 R-48 17.70 | 20 52220 114.00 | 20 52620 142.00} 21 53020 114.00 | 21 53420 142.00 
46 Re5il 18.10 | 20 52224 126.00 | 20 52624 154.00} 21 53024 126.00 | 21 53424 154.00 
46 R-54 18.60 | 20 52228 138.00 | 20 52628 166.00 |} 21 53028 138.00 | 21 53428 166.00 
46 R-57 19005 120 5223201505008 | 520 ee 5263259 186.00) 1 21 95303259 150.00) | 210) 53432 186.00 
46 R-60 19.70 |} 20 52236 172.00 | 20 52636 219.00 | 21 53036 172.00 | 21° 53436 219.00 
46 R-63 28.50 | 20 52240 184.00] 20 52640 233.00 | 21 53040 184.00 | 21 53440 233.00 
46 R-66 29.10 | 20 52244 204.00] 20 52644 245.00 | 21 53044 204.00 | 21 53444 245.00 
46 R-69 29.60 | 20 52248 216.00} 20 52648 257.00} 21 53048 216.00 | 21 53448 257.00 
46 R-72 30.10 | 20 52252 228.00} 20 52652 269.00] 21 53052 228.00} 21 53452 269.00 
46 R-75 30.70 | 20 52256 240.00} 20 52656 283.00] 21 53056 240.00] 21 53456 283.00 


46 R-78 31.30 | 20 52260 252.00] 20 52660 299.00} 21 53060 252.00 | 21 53460 299.00 
46 R-81 31.80 | 20 52304 62.00 |} 20 52704 76.00 | 21 53104 62.00 | 21 53504 76.00 
46 V-42 17.40 | 20 52308 74.00 | 20 52708 93.00 | 21 53108 74.00 | 21 53508 93.00 
46 V-45 17.80 | 20 52312 86:00 |} 20 52712 105:00)) 21953112 86.00 | 21 53512 105.00 
46 V-48 18.30 | 20 52316 102.00 | 20 52716 130.00 | 21 53116 102.00 | 21 53516 130.00 
46 V-51 18.80 | 20 52320 114.00 |} 20 52720 142.00 | 21 53120 114.00 | 21 53520 142.00 
46 V-54 19.20 | 20 52324 126.00 | 20 52724 154.00 | 21 53124 126.00 | 21 53524 154.00 
46 V-57 19.70 | 20 52328 188.00} 20> =52728° -166.00)] 21 53128 138.00 | 21 53528. 166.00 
46 V-60 20.40 | 20 52332 150.00 | 20 52732 186.00 | 21 53132 150.00 | 21 53532 186.00 
46 V-63 29.40 | 20 52336 172.00 | 20 52736 219.00 | 21 53136 172.00 | 21 53536 219.00 


46 V-66 30.00 } 20 52340 184.00 | 20 52740 233.00] 21 53140 184.00 | 21 53540 233.00 
46 V-69 30.60 | 20 52344 204.00 | 20 52744 245.00 | 21 53144 204.00} 21 53544 245.00 
46 V-72 31.10 | 20 52348 216.00 | 20 52748 257.00 | 21 53148 216.00 | 21 53548 257.00 
46 VETS 31.70 | 20 52352 228.00 | 20 52752 269.00 | 21 53152 228.00 | 21 53552 269.00 
46 V-78 32.30 | 20 52356 240.00 | 20 52756 283.00 | 21 53156 240.00 | 21 53556 283.00 
46 V-81 32.90 | 20) 52360 252.00 |) 20) 52760 299.00} 21 53160) 252.00 | 2 53560 299.00 
20 52004 50.00 } 20 52404 80.00 |} 21 52804 50.00 | 21 53204 80.00 } 22 53608 46.00 


20 52008 60.00 |} 20 52408 96.00 | 21 52808 60.00 | 21 53208 96.00 | 22 53616 56.00 
20 52012 70.00 |} 20 52412 108.00 | 21 52812 70.00 | 21 53212 108.00 | 22 53624 66.00 
20 52016 86.00 | 20 52416 132.00 | 21 52816 86.00 | 21 53216 132.00 | 22 53632 76.00 
20 52020 96.00 |} 20 52420 144.00 | 21 52820 96.00 | 21 53220 144.00 | 22 53640 100.00 
20 52024 106.00 | 20 52424 156.00 | 21 52824 106.00 | 21 53224 156.00 | 22 53648 115.00 
20 52028 116.00 | 20 52428 168.00 | 21 52828 116.00 | 21 53228 168.00 | 22 53656 130.00 
20 52032 126.00 | 20 52432 188.00 | 21 52832 W2GLOO |) Bal weezer 188.00 | 22 53664 150.00 
20. 52036 146.00 | 20 52436 222.00 | 21 52836 146.00 | 21 53236 222.00 | 22 53708 46.00 
20 52040 156.00 |} 20 52440 236.00 | 21 52840 156.00 | 21 53240 236.00] 22 53716 56.00 
20 52044 172.00 | 20 52444 248.00} 21 52844 172.00} 21 53244 248.00 | 22 53724 66.00 
20 52048 182.00 |} 20 52448 260.00 | 21 52848 182.00] 21 53248 260.00 | 22 53732 76.00 
20 52052 19 ZOO R20 02402 mmen (2,00) AO COD 192.00 | 21 53252 272.00 | 22 53740 # 100.00 
20 52056 206.00 | 20 52456 286.00] 21 52856 206.00 | 21 53256 286.00 | 22 53748 115.00 
20 52060 222.00} 20 52460 302.00 | 21 52860 222.00 | 21 53260 302.00 | 22 53756 130.00 
20 52104 50.00 | 20 52504 80.00 | 21 52904 50.00 | 21 53304 80.00 | 22 53764 150.00 
20 52108 60.00 | 20 52508 96.00 | 21 52908 60.00 | 21 53308 96.00 | 22 53808 60.00 
20° 52112 70.00 | 20 52512 108.00 | 21 52912 70.00 | 21 53312 108.00 | 22 53816 80.00 
205 52116 86.00 } 20 52516 132.00 |} 21 52916 86.00 | 21 53316 132.00 | 22 53824 90.00 
20 52120 96.00 | 20 52520 144.00 | 21 52920 96.00 | 21 53320 144.00 | 22 53832 105.00 
20 52124 106.00 | 20 52524 156.00 | 21 52924 106.00 |} 21 53324 156.00} 22 53840 130.00 
20 52128 116.00 | 20 52528 168.00 } 21 52928 116.00 | 21 53328 168.00 | 22 53848 145.00 
20 52132 126.00 | 20 52532 188.00 | 21 52932 126.00 | 21 53332 188.00 | 22 53856 160.00 
20 52136 146.00 | 20 52536 222.00} 21 52936 146.00 | 21 53336 222.00 | 22 53864 175.00 


73 


by 
e 
Numerical Index 

Page Snow Price Page Ppa Prick Page Nee Price Page Nee Prive Page spe Price 
22 53908 $60.00 | 23 54608 $58.00 | 23 55052 $257.00 | 24 55848 $177.00 | 25 56404 $64.00 
22 53916 80.00 | 23 54612 70.00 | 23 55056 271.00 | 24 55856 197.00 | 25 56408 81.00 
22 53924 90.00 | 23 54616 90.00 | 23 55060 287.00 | 24 55864 217.00 | 25 56412 93.00 
22 53932 105.00 | 23 54620 102.00 | 23 55104 64.00 | 24 55908 71.00 | 25 56416 118.00 
22 53940 130.00 23 54624 114.00 23 55108 81.00 24 55916 93.00 25 56420 130.00 
22 53948 145.00 | 23 54628 126.00 | 23 55112 93.00 | 24 55924 106.00 | 25 56424 142.00 
a 53956 160.00 23 54632 138.00 De 55116 118.00 24 55932 118.00 25 56428 154.00 
22 53964 175.00 23 54636 160.00 Rs 55120 130.00 24 55940 157.00 25 56432 174.00 
ae 54008 74.00 23 54640 172.00 23 55124 142.00 24 55948 177.00 25 56436 207.00 
oe 54016 95.00 23 54644 192.00 23 55128 154.00 24 55956 197.00 25 56440 221.00 
Die 54024 108.00 23 54648 204.00 23 55132 174.00 24 55964 217.00 25 56444 233.00 
2, 54032 120.00 93 54652 216.00 ie 55136 207.00 25 56004 34.00 25 56448 245.00 
2 54040 160.00 23 54656 228.00 23 55140 221.00 25 56008 40.00 25 56452 257.00 
22, 54048 180.00 23 54660 240.00 Ze 55144 233.00 25 56012 50.00 25 56456 271.00 
22 54056 200.00 23 54704 46.00 23 55148 245.00 25 56016 74.00 25 56460 287.00 
22 54064 220.00 | 23 54708 58.00 | 23 55152 257.00 | 25 56020 984.00 | 25 56504 +64.00 
22 54108 74.00 | 23 54712 70.00 | 23 55156 271.00 | 25 56024 94.00 | 25 56508 81.00 
22 54116 95.00 | 23 54716 90.00 | 23 55160 287.00 | 25 56028 104.00 | 25 56512 93.00 
22 54124 108.00 ay 54720 102.00 24 55208 46.00 25 56032 114.00 PA: 56516 118.00 
22 54132 120.00 23 54724 114.00 24 55216 56.00 25 56036 134.00 25 56520 130.00 


54140 160.00 | 23 54728 126.00 | 24 55224 66.00 | 25 56040 144.00 | 25 56524 142.00 
54148 180.00 | 23 54732 138.00 | 24 55232 76.00 | 2 56044 160.00 | 25 56528 154.00 
54156 200.00 | 23 54736 160.00 | 24 55240 100.00 | 25 56048 170.00 | 25 56532 174.00 
54164 220.00 | 23 54740 172.00 | 24 55248 115.00 | 25 56052 180.00 | 25 56536 207.00 
54208 71.00 | 23 54744 192.00 } 24 55256 130.00 | 25 56056 194.00 | 25 56540 221.00 
54216 93.00 | 23 54748 204.00 | 24 55264 150.00 | 25 56060 210.00 | 25 56544 233.00 
54224 106.00 | 23 54752 216.00 | 24 55308 46.00 | 25 56104 34.00 | 25 56548 245.00 
54232 118.00 | 23 54756 228.00 | 24 55316 56.00 | 25 56108 40.00 | 25 56552 257.00 
54240 157.00 | 23 54760 240.00 | 24 55324 66.00 | 25 56112 50.00 | 25 56556 °#271.00 
54248 177.00 | 23 54804 68.00 | 24 55332 76.00 | 25 56116 74.00 | 25 56560 287.00 


bS bo bS to DS DP te be Lo 
bo bo bo bo bo DO bo bo DO bo 


22 54256 197.00 | 23 54808 984.00 | 24 55340 100.00 | 25 56120 84.00 | 25 56604 64.00 
22 54264 217.00 | 23 54812 96.00 | 24 55348 115.00 | 25 56124 94.00 | 25 56608 81.00 
22 54308 71.00 | 23 54816 120.00 | 24 55356 130.00 | 25 56128 104.00 | 25 56612 93.00 
22 54316 93.00 | 23 54820 132.00 | 24 55364 150.00 | 25 56132 114.00 | 25 56616 118.00 
92 54324 106.00 | 23 54824 144.00 | 24 55408 60.00 | 25 56136 134.00 | 25 56620 130.00 
92 54332 118.00 | 23 54828 156.00 | 24 55416 80.00 | 25 56140 144.00 | 25 56624 142.00 
92 54340 157.00 | 23 54832 176.00 | 24 55424 90.00 | 25 56144 160.00 | 25 56628 154.00 
22 54348 177.00 | 23 54836 210.00 | 24 55432 105.00 | 25 56148 170.00 | 25 56632 174.00 
22 54356 197.00 | 23 54840 224.00 | 24 55440 130.00 | 25 56152 180.00 | 25 56636 207.00 
22 54364 217.00 | 23 54844 236.00 | 24 55448 145.00 | 25 56156 194.00 | 25 56640 2021.00 


23 54404 34.00 | 23 54848 248.00 | 24 55456 160.00 | 25 56160 210.00 | 25 56644 233.00 
23 54408 40.00 } 23 54852 260.00 | 24 55464 175.00 | 25 56204 46.00 | 25 56648 245.00 
23 ©654412 50.00 | 23 54856 274.00 | 24 55508 60.00 | 25 56208 58.00 | 25 56652 257.00 
ae 54416 74.00 | 23 54860 290.00 | 24 55516 80.00 | 25 56212 70.00 | 25 56656 271.00 
23 54420 84.00 | 23 54904 68.00 | 24 . 55524 90.00 | 25 56216 90.00 | 25 56660 287.00 
23 654424 94.00 | 23 54908 84.00 | 24 55532 105.00 | 25 56220 102.00 | 25 56704 64.00 
23 54428 104.00 | 23 54912 96.00 | 24 55540 130.00 | 25 56224 114.00 | 25 56708 81.00 
23 54432 114.00 | 23 54916 120.00 | 24 55548 145.00 | 25 56228 126.00 | 25 56712 93.00 
23 54436 134.00 | 23 54920 132.00 | 24 55556 160.00 | 25 56232 138.00 | 95 56716 118.00 
23 54440 144.00 | 23 54924 144.00 | 24 55564 175.00 } 25 56236 160.00 | 25 56720 130.00 


De 54444 160.00 } 23 54928 156.00 | 24 55608 71.00 } 25 56240 172.09 | 25 56724 142.00 
23 54448 170.00 } 23 54932 176.00 | 24 55616 93.00 | 25 56244 192.00 | 25 56728 154.00 
2 54452 180.00 | 2: 54936 210.00 | 24 55624 106.00 25 56248 204.00 25 56732 174.00 
23 54456 194.00 } 23 54940 224.00 | 24 55632 118.00 | 25 56252 216.00 | 25 56736 207.00 
23 54460 210.00 | 23 54944 236.00 | 24 55640 157.00 | 25 56256 228.00 | 25 56740 221.00 
23 54504 34.00 | 23 54948 248.00 | 24 55648 177.00 | 25 56260 240.00 | 25 56744 233.00 
23 54508 40.00 | 23 54952 260.00 | 24 55656 197.00 | 25 56304 46.00 | 25 56748 245.00 
2S 54512 50.00 | 23 54956 274.00 | 24 55664 217.00 | 25 56308 58.00 | 25 56752 257.00 
23 54516 74.00 | 23 54960 290.00 | 24 55708 71.00 } 25 56312 70.00 | 25 56756 271.00 
23 54520 84.00 |} 23 55004 64.00 | 24 55716 93.00 | 25 56316 90.00 | 25 56760 # 287.00 


23 54524 94.00 | 23 55008 81.00 | 24 55724 106.00 | 25 56320 102.00 | 26 56804 40.00 
23 54528 104.00 | 23 55012 93.00 | 24 55732 118.00 | 25 56324 114.00 | 26 56808 50.00 
23 54532 114.00 | 23 55016 118.00 | 24 55740 157.00 | 25 56328 126.00 | 26 56812 60.00 
23 54536 134.00 | 23 55020 130.00 | 24 55748 177.00 | 25 56332 138.00 |} 26 56816 72.06 
23 .54540 144.00 | 23 55024 142.00 | 24 55756 197.00 | 25 ,56336 160.00 | 26 56820 84.00 
23 54544 160.00 | 23 55028 154.00 | 24 55764 217.00 | 25 56340 172.00 | 26 56824 94.00 
23 54548 170.00 | 23 55032 174.00 | 24 55808 71.00 | 25 56344 192.00 | 26 56828 104.00 
23 54552 180.00 | 23 55036 207.00 | 24 55816 93.00 | 25 56348 204.00 | 26 56832 114.00 
23 54556 194.00 }| 23 55040 221.00 | 24 55824 106.00 | 25 56352 216.00 | 26 56836 134.00 
23 54560 210.00 | 23 55044 233.00 | 24 55832 118.00 | 25 56356 228.00 | 26 56840 148.00 
23 54604 46.00 | 23 55048 245.00 | 24 55840 157.00 | 25 .56360 240.00 | 26 56844 162.00 


74 


Numerical Index 


Page Aivebe! Prive Page ates! Prive Page SN yee Prine Page eave Phite Page ape Brite 

26 56848 $176.00 | 26 57332 $150.00 | 27 57816 $82.00 27 58260 $272.00 17 60406 $27.50 
26 56852 190.00 26 57336 188.00 |} 27 57820 94.00 27 58304 55.00 ine 60408 33.00 
26 56856 204.00 | 26 57340 202.00 27 57824 114.00 27 58308 65.00 1% 60410 38.50 
26 56860 218.00 | 26 57344 216.00 27 57828 126.00 27 58308 65.00 Gy 60412 44.00 
26 56904 40.00 | 26 57348 230.00 27 57832 138.00 oT 58316 90.00 17 60414 49.50 
26 56908 50.00 | 26 57352 244.00 27 57836 158.00 or 58320 102.00 17 60416 55.00 
26 56912 60.00 26 57356 258.00 aN 57840 172.00 Th 58324 126.00 17 60418 60.50 
26 56916 72.00 26 57360 272.00 27 57844 186.00 | 27 58328 138.00 17 60420 66.00 
26 56920 84.00 | 26 57404 55.00 PAL 57848 200.00 PALE 58332 150.00 7 60454 22.00 
26 56924 94.00 | 26 57408 65.00 | 27 57852 214.00 a7 58336 788.00 aby 60456 27.50 


26 56928 104.00 | 26 57412 162K) || 7 57856 228.00 | 97 58340 202.00 17 60458 33.00 
26 56932 114.00 | 26 57416 90.00 | 27 57860 242.00 | 2 58344 216.00 alte 60460 38.50 
26 56936 134.00 | 26 57420 102.00 | 27 57904 46.00 } 927 58348 230.00 | 17 60462 44.00 
26 56940 148.00 | 26 57424 126.00 | 27 57908 58.00 | 97 58352 24400 117 #4260464 49.50 
26 56944 162.00 | 26 57428 138.00 | 27 57912 68.00 | 97 58356 258.00 | 17 60466 55.00 
26 56948 176.00 | 26 57432 150.00 j 27 57916 82.00 | 27 58360 272.00 17 60468 60.50 
26 56952 190.00 | 26 57436 188.00 | 27 57920 94.00 aliyé 60104 SAFOOML lee 60470 66.00 
26 56956 204.00 | 26 57440 202.00 } 27 57924 114.00 17 60106 23.00 | 14 66104 6.30 
26 56960 218.00 | 26 57444 216.00 | 27 57928 126.00 17 60108 25.00 | 14 66106 9.00 
26 57004 46.00 | 26 57448 230.00 | 27 57932 138.00 | 17 60110 97.50 | 14 66108 10.80 


26 57008 58.00 | 26 57452 244.00 | 27 57936 158.00 | 17 60112 30.00 | 14 66110 12.60 
26 57012 68.00 | 26 57456 258.00 | 27 57940 172.00 117 #60114 32.50 | 14 66112 14.40 
26 57016 82.00 | 26 57460 272.00 | 27 57944 186.00 |} 17 60116 35.00 } 14 66204 9.00 
26 57020 94.00 | 26 57504 55.00 | 27 57948 200.00 | 17 #60118 37.50 | 14 66206 13.50 
26 57024 114.00 | 26 57508 65.00 | 27 57952 214.00 | 17 #260120 40.00 | 14 66208 16.20 
26 57028 126.00 | 26 57512 75.000 127 57956 228.00 |} 17 60154 21.00 | 14 66210 18.90 
26 57032 138.00 | 26 57516 90.00 | 27 57960 242.00 | 17 60156 23.00 | 14 66212 22.50 
26 57036 158.00 | 26 57520 102.00 | 27 58004 55.00 | 17 60158 25.00 | 15 66304 8.60 
26 57040 172.00 | 26 57524 126.00 | 27 58008 65.00 {| 17 60160 27.50 } 15 66306 12.50 
26 57044 186.00 | 26 57528 138.00 | 27 58012 75.00 |} 17 60162 30.00 | 15 66308 15.50 


26 57048 200.00 26 57532 150.00 Al 58016 90.00 Lye 60164 32.50 15 66310 20.00 
26 57052 214.00 26 57536 188.00 PAE 58020 102.00 ales 60166 35.00 15 66312 23.20 
26 57056 228.00 | 26 57540 202.00 | 27 58024 126.00 | 17 60168 37.50 | 15 66404 12.50 
26 57060 242.00 26 57544 216.00 07 58028 138.00 ily 60170 40.00 15 66406 18.50 
26 57104 46.00 26 57548 230.00 27 58032 150.00 Aye 60204 20.00 15 66408 23.20 
26 57108 58.00 26 57552 244.00 rat 58036 188.00 17 60206 25.00 15 66410 26.40 
26 57112 68.00 26 57556 258.00 | 27 58040 202.00 17 60208 30.00 15 66412 30.50 
26 57116 82.00 | 26 57560 272.00 | 27 58044 216.00 | 17 60210 35.00 } 50 83990 2.30 
26 57120 94.00 | 27 57604 40.00 | 27 58048 230.00 | 17 60212 40.00 | 50 83992 2.90 
26 57124 114.00 | 27 57608 50.00 |} 927 58052 244.00 | 17 60214 45.00 | 50 £83994 3.40 


26 57128 126.00 | 27 57612 60.00 | 27 58056 258.00 | 17 60216 50.00 | 3 90004 62.00 
26 57132 138.00 | 27 57616 72.00 | 97 58060 272.00 | 47 60218 55.00 | 30 90006 68.00 
26 57136 158.00 | 27 57620 84.00 | 27 58104 55.00 117 60220 60.00 | 30 90008 78.00 
26 57140 172.00 | 27 57624 94.00 | 27 58108 65.00 | 47 60254 20.00 | 30 90010 88.00 
96 57144 186.00 | 27 57628 104.00 | 27 58112 75.00 | 17 60256 25.00 130 90012 98.00 
2608707148 8) 200.00 [927 57632" 5 114.00° | 97) 58116 90.00 | 17 60258 30.00 | 30 90014 110.00 
96 57152 214.00 | 27 57636 134.00 | 27 58120 102.00 | 47 60260 35.00 | 30 90016 120.00 
296 57156 228.00 | 27 57640 148.00 | 27 58124 126.00 | 17 60262 40.00 | 30 90018 130.00 
26 57160 242.00 | 27 57644 162.00 | 27 58128 138.00 | 1417 60264 45.00 | 30 90020 140.00 
96 57204 55.00 | 27 57648 176.00 | 27 58132 150.00 | 17 60266 50.00 | 30 90022 150.00 


296 57208 65.00 | 27 57652 190.00 | 27 58136 188.00 | 17 60268 55.00 | 30 90024 160.00 
26a 87212 75.00 | 27 57656 204.00 | 27 58140 202.00 | 17 60270 60.00 | 30 90026 176.00 
26 57216 90.00 | 27 57660 218.00 | 27 58144 216.00 117 60304 23.00 | 30 90028 186.00 
26 57220 102.00 | 27 57704 40.00 | 27 58148 230.00 | 17 60306 25.50 | 30 90030 200.00 
pomenn/2e4, | 126.00 1°27. 57708 50.00 | 27 58152 244.00 | 17 60308 27.50 | 3 90032 216.00 
26 57228 138.00 | 27 57712 60.00 | 27 58156 258.00 | 17 60310 30.50 | 30 90054 62.00 
AS yee qo) |) ae PAIS 72.00 | 27 58160 272.00 | 17 60312 33.00 | 30 90056 68.00 
26 57236 188.00 | 27 57720 84.00 | 27 58204 55.00 117 60314 36.00 | 30 90058 78.00 
26 57240 202.00 | 27 57724 94.00 | 27 58208 65.00 | 17 60316 38.50 | 30 90060 88.00 
26 57244 216.00 | 27 57728 104.00 | 27 58212 75.00 | 17 60318 41.00 | 30 90062 98.00 


26 57248 230.00 | 27 57732 114.00 | 27 58216 90.00 | 17 60320 44.00 | 30 90064 #110.00 
26 57252 244.00 | 27 57736 134.00 | 27 58220 102.00 | 17 60354 23.00 | 30 90066 120.00 
26 57256 258.00 |} 27 57740 148.00 | 27 58224 126.00 | 17 60356 25.50 | 30 90068 £130.00 
26 57260 272.00 | 27 57744 162.00 | 27 58228 138.00 | 17 60358 27.50 | 30 90070 140.00 
26 57304 55.00 | 27 57748 176.00 | 27, 58232 150.00 | 17 60360 30.50 | 30 90072 °# 150.00 
26 57308 65.00 | 27 57752 190.00 | 27 58236 188.00 |} 17 60362 33.00 | 30 90074 160.00 
26 57312 75.00 | 27 57756 204.00 | 27 58240 202.00 | 17 60364 36.00 | 30 90076 176.00 
26 57316 90.00 | 27 57760 218.00 | 27 58244 216.00 | 17 60366 38.50 | 30 90078 186.00 
26 57320 102.00 |} 27 57804 46.00 | 27 58248 230.00 | 17 60368 41.00 | 30 90080 200.00 
26 57324 126.00 | 27 57808 58.00 | 27 58252 244.00 | 17 60370 44.00 | 30 90082 216.00 
26 57328 138.00 | 27 57812 68.00 | 27 58256 258.00 | 17 60404 22.00 | 30 90104 74.00 


75 


s BENJAMIN :STARRETT . 
e 
Numerical Index 
Page Weed price Pago appa Prive Page SiN Prive Page yh Prive Page ae pat 


30 90106 $86.00 | 30 90328 $257.00 | 31 90870 $158.00 | 32 91112 $98.00 32 91354 $88.00 
30 90108 96.00 | 30 90330 273.00 | 3 90872 168.00 | 32 91114 110.00 32 91356 108.00 
30 90110 106.00 | 30 90332 287.00 | 31 90874 178.00 | 32 91116 120.00 32 91358 118.00 
30 90112 126.00 | 30 90354 85.00 | 31 90876 192.00 | 32 91118 130.00 32 91360 128.00 
30 90114 136.00 | 30 90356 106.00 | 3 90878 202.00 } 32 91120 140.00 32 91362 160.00 
30 90116 146.00 | 30 90358 116.00 | 3 90880 212.00 | 32 91122 150.00 32 91364 170.00 
30 90118 156.00 | 30 90360 126.00 | 31 90882 222.00 | 32 91124 160.00 32 91366 190.00 
30 90120 166.00 | 30 90362 157.00 | 31 90904 86.00 | 32 91126 176.00 32 91368 200.00 
30 90122 186.00 | 30 90364 167.00 | 31 90906 96.00 | 32 91128 186.00 32 91370 210.00 
3 90124 196.00 | 3 90366 187.00 | 31 90908 106.00 | 32 91130 200.00 32 91372 220.00 


30 90126 206.00 | 30 90368 197.00 | 31 90910 116.00 | 32 91132 216.00 32 91374 230.00 
3 90128 216.00 | 30 90370 207.00 } 31 90912 126.00 | 32 91154 62.00 32 91376 246.00 
SO meOO1 SO mee co 00m lo 0m o0S 72m 2/2 O0M mo lame O91 4 00-00 Ino mmo OO 68.00 32 91378 260.00 
30 90132 236.00 | 3 90374 227.00 | 31 90916 160.00 | 32 91158 78.00 32 91380 276.00 
30 90154 74.00 | 30 90376 243.00 | 31 90918 180.00 | 32 91160 88.00 32 91382 290.00 
30 90156 86.00 | 30 90378 257.00 | 31 90920 190.00 | 32 91162 98.00 32 91404 85.00 
30 90158 96.00 | 30 90380 273.00 } 31 90922 200.00 | 32 91164 110.00 32 91406 106.00 
30 90160 106.00 | 3 90382 287.00 | 31 90924 210.00 | 32 91166 120.00 32 91408 116.00 
30 90162 126.00 | 3 90404 58.00 | 31 90926 220.00 | 3 91168 130.00 32 91410 126.00 
30 90164 136.00 | 31 90406 68.00 | 31 90928 230.00 | 32 91170 140.00 32 91412 #157.00 


3 90166 146.00 | 31 90408 78.00 | 31 90930 240.00 | 32 91172 150.00 32 91414 167.00 
30 90168 156.00 | 3 90410 88.00 | 31 90932 250.00 | 32 91174 #160.00 32 91416 187.00 
30 90170 166.00 | 31 90412 98.00 | 31 90954 86.00 | 32 91176 176.00 32 91418 197.00 
30 90172 186.00 | 31 90414 106.00 | 31 90956 96.00 | 32 91178 186.00 32 91420 207.00 
30 90174 196.00 | 31 90416 116.00 | 31 90958 106.00 32 91180 200.00 32 91422 217.00 
30 90176 206.00 | 31 90418 126.00 | 31 90960 116.00 | 32 91182 216.00 | 32 91424 227.00 
30 90178 216.00 | 31 90420 140.00 | 31 90962 126.00 | 32 91204 74.00 |} 32 91426 243.00 
30 90180 226.00 | 31 90422 150.00 | 31 90964 150.00 32 91206 86.00 | 32 91428 257.00 
30 90182 236.00 | 31 90424 160.00 | 31 90966 160.00 32 91208 96.00 | 32 91430 273.00 
30 90204 88.00 | 31 90426 170.00 | 31 90968 180.00 32 91210 106.00 | 32 91432 287.00 


30 90206 108.00 | 31 90428 180.00 | 31 90970 190.00 32 91212 126.00 | 32 91454 85.00 
3 90208 118.00 | 31 90430 190.00 |} 31 90972 200.00 | 32 91214 136.00 | 32 91456 106.00 
3 90210 128.00 } 3 90432 206.00 | 31 90974 210.00 32 91216 146.00 | 32 91458 116.00 
30 90212 160.00 | 31 90454 58.00 | 31 90976 220.00 | 32 91218 156.00 | 32 91460 126.00 
30 90214 170.00 } 31 90456 68.00 | 31 90978 230.00 | 32 91220 166.00 | 32 91462 157.00 
30 90216 190.00 | 31 90458 78.00 | 31 90980 240.00 | 32 91222 186.00 | 32 91464 167.00 
30 90218 200.00 | 31 90460 88.00 | 31 90982 250.00 | 32 91224 196.00 | 32 91466 187.00 
30 90220 210.00 | 31 90462 98.00 | 31 91004 82.00 | 32 91226 206.00 | 32 91468 1197.00 
30 90222 220.00 | 31 90464 106.00 | 31 91006 93.00 32 91228 216.00 | 32 91470 207.00 
30 90224 230.00 | 31 90466 116.00 | 31 91008 103.00 | 32 91230 226.00 | 32 91472 217.00 


30 90226 246.00 | 31 90468 126.00 } 31 91010 113.00 32 91232 236.00 | 32 91474 227.00 
3 90228 260.00 | 31 90470 140.00 | 31 91012 123.00 32 91254 74.00 | 32 91476 243.00 
30 90230 276.00 | 31 90472 150.00 | 31 91014 148.00 aye NaIe 86.00 | 32 91478 257.00 
30 90232 290.00 | 31 90474 160.00 | 31 91016 158.00 32 +91258 96.00 | 32 91480 273.00 
30 90254 88.00 | 31 90476 170.00 | 31 91018 178.00 32 91260 106.00 | 32 91482 287.00 
30 90256 108.00 | 31 90478 180.00 | 31 91020 188.00 32 91262 126.00 | 33 91804 58.00 
30 90258 118.00 | 31 90480 190.00 | 3 91022 198.00 32 91264 136.00 | 33 91806 68.00 
30 90260 128.00 | 31 90482 206.00 31 91024 208.00 3 91266 146.00 | 33 91808 78.00 
30 90262 160.00 | 31 90804 68.00 | 31 91026 218.00 32 91268 156.00 | 33 91810 88.00 
30 90264 £170.00 | 3 90806 78.00 | 3 91028 228.00 32 91270 166.00 | 33 91812 98.00 


30 90266 190.00 | 31 90808 88.00 3 91030 238.00 32 91272 186.00 | 33 91814 106.00 
30 90268 200.00 | 31 90810 98.00 31 91032 248.00 32 91274 196.00 | 33 91816 116.00 
30 90270 210.00 | 3 90812 108.00 31 91054 82.00 32 91276 206.00 | 33 91818 126.00 
30 90272 220.00 | 3 90814 128.00 3 91056 93.00 32 91278 216.00 | 33 91820 140.00 
30 90274 230.00 |} 3 90816 138.00 31 91058 103.00 32 91280 226.00 | 33 91822 150.00 
30 90276 246.00 | 31 90818 148.00 3 91060 113.00 32 91282 236.00 | 33 91824 160.00 
30 90278 260.00 |} 3 90820 158.00 31 91062 123.00 32 91304 88.00 | 33 91826 170.00 


30° 90280 _ 276.00 | 3 90822 168.00 3 91064 148.00 32 91306 108.00 33 91828 180.00 
30) 90282) 290.00 | 3 90824 178.00 31 91066 158.00 32 91308 118.00 | 33 91830 190.00 
30 90304 85.00 | 31 90826 192.00 31 91068 178.00 32 91310 128.00 | 383 91832 206.00 


30 90306 106.00 } 3 90828 202.00 31 91070 188.00 32 91312 160.00 | 383 91854 58.00 
30 90308 116.00 | 3 90830 212.00 3 91072 198.00 32 91314 170.00 | 3: 91856 68.00 
30 90310 126.00 | 3 90832 222.00 3 91074 208.00 32 91316 190.00 | 33 91858 78.00 
SO OS 2m / 500M Eo 90854 68.00 3l 91076 218.00 32 91318 200.00 | 33 91860 88.00 
30 90314 167.00 | 3 90856 78.00 31 91078 228.00 SAO Loc OME OLO0M IES: 91862 98.00 
30 90316 187.00 |} 3 90858 88.00 31 91080 238.00 32 91322 220.00 | 33 91864 106.00 
DUMOOS1 Om LO 7ZO0M Ta 90860 98.00 31 91082 248.00 32 91324 230.00 | 33 91866 116.00 
30 90320 207.00 | 3 90862 108.00 } 32 91104 62.00 32 91326 246.00 | 33 91868 126.00 
30 90322 217.00 | 31 90864 128.00 | 32 91106 68.00 32 91328 260.00 | 33 91870 140.00 
30 90324 227.00 | 3 90866 138.00 | 32 91108 78.00 32 91330 276.00 | 33 91872 150.00 
30 90326 243.00 | 3 90868 148.00 | 32 91110 88.00 32 91332 290.00 | 33 91874 160.00 


76 


Numerical Index 


és 
Catalog List Catalog List 
Page No. Price Page No. Price 
33 91876 $170.00 5° 92118 $178.00 
ate 91878 180.00 33 92120 188.00 
35° 91880 190.00 33 92122 198.00 
33 91882 206.00 33 92124 208.00 
33 91904 68.00 33 92126 218.00 
30 91906 78.00 33 92128 228.00 
33 91908 88.00 33 92130 238.00 
33 91910 98.00 33 92132 248.00 
33 91912 108.00 33 92154 82.00 
33 91914 128.00 33 92156 93.00 
30 91916 138.00 | 33 92158 103.00 
33 91918 148.00 333) 92160 113.00 
33 91920 158.00 33 92162 123.00 
33 91922 168.00 33 92164 148.00 
33 91924 178.00 | 33 92166 158.00 
33 91926 192.00 | 33 92168 178.00 
33 91928 202.00 } 33 92170 188.00 
33 91930 212.00 33 92172 198.00 
33 91932 222.00 33 92174 208.00 
33 91954 68.00 Be 92176 218.00 
33 91956 78.00 | 33 92178 228.00 
33 91958 88.00 33 92180 238.00 
33 91960 98.00 33 92182 248.00 
3 91962 108.00 } 34 92204 38.00 
33 91964 128.00 34 92208 45.00 
33 91966 138.00 | 34 92212 52.00 
oo 91968 148.00 | 34 92216 60.00 
33 91970 158.00 | 34 92220 70.00 
as 91972 168.00 34 92224 80.00 
33 91974 178.00 34 92228 90.00 
33 91976 192.00 | 34 92232 100.00 
33 91978 202.00 | 34 92254 38.00 
33 91980 212.00 | 34 92258 45.00 
33 91982 222.00 34 92262 52.00 
33 92004 86.00 34 92266 60.00 
33 92006 96.00 34 92270 70.00 
33 92008 106.00 | 34 92274 80.00 
33 92010 116.00 34 92278 90.00 
Be 92012 126.00 34 92282 100.00 
33 92014 150.00 | 34 92304 54.00 
3: 92016 160.00 | 34 92308 68.00 
33 92018 180.00 34 92312 85.00 
33 92020 190.00 } 34 92316 95.00 
33 92022 200.00 34 92320 105.00 
33 92024 210.00 34 92324 115.00 
33 92026 220.00 34 92328 125.00 
3 92028 230.00 | 34 92332 135.00 
33 92030 240.00 | 34 92354 54.00 
Be 92032 250.00 34 92358 68.00 
33 92054 86.00 34 92362 85.00 
33 92056 96.00 34 92366 95.00 
23 92058 106.00 34 92370 105.00 
33 92060 116.00 34 92374 115.00 
3 92062 126.00 34 92378 125.00 
33 92064 150.00 34 92382 135.00 
33 92066 160.00 34 92404 70.00 
33 92068 180.00 34 92408 80.00 
33 92070 190.00 34 92412 120.00 
33 92072 200.00 34 92416 130.00 
33 92074 210.00 34 92420 140.00 
33 92076 220.00 34 92424 150.00 
33 92078 230.00 34 92428 160.00 
33 92080 240.00 34 92432 180.00 
33 92082 250.00 | 3 92454 70.00 
3 92104 82.00 3 92458 80.00 
33 92106 93.00 34 92462 120.00 
33 92108 103.00 34 92466 130.00 
33 92110 113.00 34 92470 140.00 
ai 92112 123.00 34 92474 150.00 
33 92114 148.00 34 92478 160.00 
ae 92116 158.00 34 92482 180.00 


BENJAMIN STARRETT 


Page 


Catalog 
No. 


92504 
92508 
92512 
92516 
92520 
92524 
92528 
92532 
92554 
92558 


92562 
92566 
92570 
92574 
92578 
92582 
92604 
92608 
92612 
92616 


92620 
92624 
92628 
92632 
92636 
92640 
92644 
92648 
92652 
92656 


92660 
92704 
92708 
92712 
92716 
92720 
92724 
92728 
92732 
92736 


92740 
92744 
92748 
92752 
92756 
92760 
92804 
92808 
92812 
92016 


92820 
92824 
92828 
92832 
92836 
92840 
92844 
92848 
92852 
92856 


92860 
92904 
92908 
92912 
92916 
92920 
92924 
92928 
92932 
92936 
92940 


List 
Price 


$67.00 

78.00 
117.00 
127.00 
137.00 
147.00 
157.00 
177.00 

67.00 

78.00 


117.00 
127.00 
137.00 
147.06 
157.00 
177.00 
38.00 
45.00 
52.00 
60.00 


70.00 

80.00 

90.00 
100.00 
115.00 
125.00 
135.00 
145.00 
160.00 
170.00 


180.00 
38.00 
45.00 
52.00 
60.00 
70.00 
80.00 
90.00 

100.00 

115.00 


125.00 
135.00 
145.00 
160.00 
170.00 
180.00 
54.00 
62.00 
70.00 
85.00 


95.00 
105.00 
115.00 
125.00 
145.00 
160.00 
170.00 
180.00 
190.00 
200.00 


210.00 
54.00 
62.00 
70.00 
85.00 
95.00 

105.00 

115.00 

125.00 

145.00 

160.00 


Page 


wowwiwww www es. 
OVO OL OT OT OT OF OT OT O1 


ww ww www ie 
TOOT OU OT OV OT ONO 


(Se) 
i) 


rp 

Catalog List Catalog List 

No. Price Page No. Price 
92944 $170.00 | 36 93416 $104.00 
92948 180.00 | 36 93418 114.00 
92952 190.00 | 36 93420 124.00 
92956 200.00 | 36 93422 134.00 
92960 210.00 | 36 93424 144.00 
93004 70.00 | 36 93426 160.00 
93008 78.00 | 36 93428 170.00 
93012 86.00 | 36 93430 184.00 
93016 100.00 | 36 93432 200.00 
93020 110.00 | 36 93454 42.00 
93024 120.00 | 36 93456 52.00 
93028 136.00 | 36 93458 62.00 
93032 146.00 | 36 93460 72.06 
93036 184.00 | 36 93462 82.00 
93040 194.00 | 36 93464 94.00 
93044 204.00 | 36 93466 104.00 
93048 214.00 | 36 93468 114.00 
93052 224.00 | 36 93470 124.00 
93056 234.00 | 36 93472 134.00 
93060 244.00 | 36 93474 144.00 
93104 70.00 | 36 93476 160.00 
93108 78.00 | 36 93478 170.00 
93112 86.00 | 3 93480 184.00 
tee: Lae 36 93482 200.00 
. 3 93804 58.00 
93124 120.00 | 36 93806 70.00 
93128 136.00 | 36 93808 80.00 
93132 146.00 | 36 93810 90.00 
93136 184.00 | 36 93812 110.00 
93140 194.00 | 36 93814 120.00 
93144 204.00 | 36 93816 130.00 
93148 214.00 | 36 93818 140.00 
93152 224.00 | 36 93820 150.00 
93156 234.00 | 36 93822 170.00 
93160 244.00 | 3 93824 180.00 
93204 66.00 | 36 93826 190.00 
93208 75.00 | 36 93828 200.00 
93212 83.00 | 36 93830 210.00 
93216 98.00 | 36 93832 220.00 
93220 108.00 | 36 93854 58.00 
93224 118.00 | 36 93856 70.00 
939995134008 )13 93858 80.00 
93232 144.00 | 36 93860 90.00 
93236 181.00 | 36 93862 110.00 
93240 191.00 | 36 93864 120.00 
93244 201.00 | 36 93866 130.00 
93248 211.00 | 36 93868 140.00 
93252 221.00 | 36 93870 150.00 
93256 231.00 | 3 93872 170.00 
93260 241.00 | 3 93874 180.00 
93304 66.00 | 36 93876 190.00 
93308 75.00 | 36 93878 200.00 
93312 83.00 | 36 93880 210.00 
93316 98.00 | 36 93882 220.00 
93320 108.00 | 36 93904 72.00 
93324 118.00 | 36 93906 92.00 
93328 134.00 | 36 93908 102.00 
93332 144.00 | 36 93910 112.00 
93336 181.00 | 36 93912 144.00 
93340 191.00 | 36 93914 154.00 
93344 201.00 | 36 93916 174.00 
93348 211.00 | 36 93918 184.00 
93352 221.00 | 36 93920 194.00 
93356 231.00 | 36 93922 204.00 
93360 241.00 | 3 93924 214.00 
93404 42.00 | 36 93926 230.00 
93406 52.00 | 36 93928 244.00 
93408 62.00 {| 3 93930 260.00 
93410 72.00 | 36 93932 274.00 
93412 82.00 | 36 93954 72.00 
93414 94.00 | 36 93956 92.00 


i — 


77 


Numerical Index 


sd 


Catalog List Catalog List Catalog List Catalog List Catalog List 
No. No. No. No. No. 


Page Price Page Price Page Price Page Price Page Price 

36 93958 $102.00 3H 94180 $174.00 BHF) 94422 $182.00 38 95112 $117.00 39 95552 $190.00 
36 93960 112.00 37 94182 190.00 37 94424 192.00 38 95116 127.00 39 95556 200.00 
36 93962 144.00 37 94204 52.00 37 94426 202.00 38 95120 137.00 39 95560 210.00 
36 93964 154.00 37 94206 62.00 ol 94428 212.00 38 95124 147.00 | 39 95604 66.00 
36 93966 174.00 37 94208 72.00 ol 94430 222.00 38 95128 157.00 39 95608 75.00 
36 93968 184.00 atl 94210 82.00 37 94432 232.00 36 95132 177.00 39 95612 83.00 
36 93970 194.00 37 94212 92.00 orl 94454 66.00 38 95154 67.00 39 95616 98.00 
3 93972 204.00 37 94214 112.00 37 94456 77.00 38 95158 78.00 3 95620 108.00 
36 93974 214.00 Bil 94216 122.00 3 94458 87.00 | 38 95162 117.00 39 95624 118.00 
36 93976 230.00 37 94218 132.00 ot 94460 97.00 38 95166 127.00 39 95628 134.00 
36 93978 244.00 a7 94220 142.00 37/ 94462 107.00 | 38 95170 137.00 39 95632 144.00 
36 93980 260.00 Bytl 94222 152.00 3 94464 132.00 38 95174 147.00 39 95636 181.00 
36 93982 274.00 37 94224 162.00 37 94466 142.00 38 95178 157.00 39 95640 191.00 
36 94004 69.00 37 94226 176.00 onl 94468 162.00 | 38 95182 177.00 3$ 95644 201.00 
36 94006 90.00 Bill 94228 186.00 37 94470 172.00 | 39 95204 38.00 39 95648 211.00 
36 94008 100.00 on 94230 196.00 37 94472 182.00 39 95208 45.00 39 95652 221.00 
36 94010 110.00 37 94232 206.00 By 94474 192.00 39 95212 52.00 39 95656 231.00 
36 94012 141.00 37 94254 52.00 37 94476 202.00 39 95216 60.00 39 95660 241.00 
36 94014 151.00 OVA 94256 62.00 37 94478 212.00 39 95220 70.00 39 95804 66.00 
36 94016 171.00 37 94258 72.00 37 94480 222.00 39 95224 80.00 39 95808 75.00 
36 94018 181.00 37 94260 82.00 | 37 94482 232.00 39 95228 90.00 39 95812 83.00 
36 94020 191.00 37 94262 92.00 38 94804 38.00 39 95232 100.00 39 95816 98.00 
36 94022 201.00 37 94264 112.00 38 94808 45.00 39 95236 115.00 39 95820 108.00 
36 94024 211.00 37 94266 122.00 38 94812 52.00 | 39 95240 125.00 39 95824 118.00 
3 94026 2217.00) [037 94268 132.00 | 38 94816 60.00 | 39 95244 135.00 | 39 95828 134.00 
3 94028 241.00 | 37 94270 142.00 | 388 94820 70.00 | 39 95248 145.00 | 39 95832 144.00 
36 94030 257.00 37 94272 152.00 38 94824 80.00 29 95252 160.00 39 95836 18100 


36 94032 271.00 | 37 94274 162.00 | 38 94828 90.00 | 39 95256 170.00 | 39 95840 £191.00 
36 94054 69.00 | 37 94276 176.00 | 388 94832 100.00 | 39 95260 180.00 | 39 95844 201.00 
36 94056 90.00 | 37 94278 186.00 | 38 94854 38.00 | 39 95304 38.00 | 39 95848 211.00 


36 94058 100.00 ont 94280 196.00 38 94858 45.00 | 39 95308 45.00 39 95852 221.00 
36 94060 110.00 37 94282 206.00 38 94862 52.00 | 39 95312 52.00 39 95856 231.00 
36 94062 141.00 3 94304 70.00 38 94866 60.00 39 95316 60.00 39 95860 241.00 
36 94064 151.00 on 94306 80.00 38 94870 70.00 | 39 95320 70.00 39 95904 66.00 
3 94066 die OOm mot 94308 90.00 | 38 94874 80.00 | 39 95324 80.00 } 39 95908 75.00 
36 94068 181.00 | 37 94310 100.00 | 38 94878 90.00 } 39 95328 90.00 | 39 95912 83.00 
3 94070 191.00 | 37 94312 110.00 | 38 94882 100.00 |} 39 95332 100.00 | 39 95916 98.00 
36 94072 201.00 37 94314 134.00 | 38 94904 54.00 | 39 95336 115.00 | 39 95920 108.00 
3 94074 211.00 | 37 94316 144.00 | 38 94908 68.00 | 39 95340 125.00 | 39 95924 118.00 
36 94076 227.00 | 37 94318 164.00 | 38 94912 85.00 | 39 95344 135.00 } 39 95928 134.00 


36 94078 241.00 | 37 94320 174.00 | 38 94916 95.00 | 39 95348 145.00 | 39 95932 144.00 
26 94080 257.00 | 37 94322 184.00 | 38 94920 105.00 | 39 95352 160.00 | 39 95936 181.00 
3 94082 271.00 | 37 94324 194.00 | 38 94924 115.00 | 3 95356 170.00 | 39 95940 191.00 
37 94104 38.00 | 37 94326 204.00 | 35 94928 125.00 | 39 95360 180.00 |} 39 95944 201.00 
3 94106 48.00 | 37 94328 214.00 | 38 94932 135.00 | 39 95404 54.00 | 39 95948 211.00 
37 94108 58.00 | 37 94330 224.00 | 3 94954 54.00 | 39 95408 62.00 | 39 95952 221.00 
3 94110 68.00 | 37 94332 234.00 | 38 94958 68.00 | 39 95412 70.00 | 39 95956 231.00 

7 94112 78.00 | 37 94354 70.00 | 38 94962 85.00 | 39 95416 85.00 | 39 95960 241.00 
37 94114 90.00 | 3 94356 80.00 | 38 94966 95.00 | 39 95420 95.00 | 39 96004 66.00 
37 94116 100.00 | 37 94358 90.00 | 38 94970 105.00 | 39 95424 105.00 | 39 96008 75.00 


87 94118 110.00 | 37 94360 100.00 | 38 94974 115.00 | 39 95428 115.00 | 39 96012 83.00 
37 94120 124.00 | 37 94362 110.00 | 38 94978 125.00 | 3 95432 125.00 | 39 96016 98.00 
37 94122 134.00 | 37 94364 134.00 | 38 94982 135.00 | 39 95436 145.00 | 39 96020 108.00 
87 94124 144.00 | 37 94366 144.00 | 38 95004 67.00 | 39 95440 160.00 | 39 96024 118.00 
37 94126 154.00 | 37 94368 164.00 | 38 95008 78.00 | 39 95444 170.00 | 39 96028 134.00 
37 94128 164.00 | 37 94370 174.00 | 38 95012 117.00 | 39 95448 180.00 | 39 96032 144.00 
87 94130 174.00 | 37 94372 184.00 | 38 95016 127.00 | 35 95452 190.00 | 39 96036 181.00 
37 94132 190.00 | 37 94374 194.00 | 38 95020 137.00 | 39 95456 200.00 | 39 96040 191.00 
387 = 94.154 38.00 | 37 94376 204.00 | 38 95024 147.00 | 39 95460 210.00 | 39 96044 201.00 
37 94156 48.00 | 37 94378 214.00 | 38 95028 157.00 | 3 95504 54.00 | 3 96048 211.00 
37 94158 58.00 | 37 94380 224.00 | 38 95032 177.00 | 39 95508 62.00 | 39 96052 221.00 
3 94160 68.00 | 37 94382 234.00 | 38 95054 67.00 | 39 95512 70.00 | 39 96056 231.00 
37 94162 78.00 | 37 94404 66.00 | 38 95058 78.00 | 38 95516 85.00 | 39 96060 241.00 
37 94164 90.00 | 37 94406 77.00 | 38 95062 117.00 | 39 95520 95.00 | 40 96104 42.00 
37 94166 100.00 | 37 94408 87.00 | 3 95066 127.00 | 39 95524 105.00 | 40 96106 52.00 
37 94168 110.00 | 37 94410 97.00 | 388 95070 137.00 | 39 95528 115.00 | 40 96108 62.00 
37 94170 124.00 | 37 94412 107.00 | 3 95074 147.00 | 39 95532 125.00 | 40 96110 72.00 
37 94172 134.00 | 37 94414 132.00 | 3 95078 157.00 | 3° 95536 145.00 | 40 96112 82.00 
37 94174 144.00 | 37 94416 142.00 | 38 95082 177.00 | 39 95540 160.00 | 40 96114 94.00 
37 94176 154.00 | 37 94418 162.00 | 38 95104 67.00 | 39 95544 170.00 } 40 96116 104.00 
37 94178 164.00 | 37 94420 172.00 | 38 95108 78.00 | 39 95548 180.00 | 40 96118 114.00 


78 


<<< BENAMIN STARRETT Da 
Numerical Index 


Catalog List Catalog List Catalog List Catalog List Catalog List 
No. Price Page No. Price Page No. Price Page No. Price Page No. 

40 96120 $124.00 40 96362 $141.00 41 96604 $52.00 41 96926 $202.00 42 97168 $140.00 
40 96122 134.00 40 96364 151.00 41 96606 62.00 41 96928 212.00 42 97170 150.00 
40 96124 144.00 40 96366 171.00 41 96608 72.00 41 96930 222.00 42 97172 170.00 
4() 96126 160.00 40 96368 181.00 41 96610 82.00 41 96932 232.00 42 97174 180.00 
40) 96128 170.00 40 96370 191.00 41 96612 92.00 | 41 96954 66.00 | 42 97176 190.00 
4() 96130 184.00 40 96372 201.00 41 96614 112.00 41 96956 77.00 42 97178 200.00 
40 96132 200.00 | 40 96374 211.00 | 41 96616 122.00 | 41 96958 87.00 | 42 97180 210.00 
40) 96154 42.00 40 96376 227.00 41 96618 132.00 41 96960 97.00 | 42 97182 220.00 
40) 96156 52.00 40) 96378 241.00 41 96620 142.00 41 96962 107.00 } 42 97204 65.00 
40 96158 62.00 | 40 96380 257.00 | 41 96622 152.00 | 41 96964 132.00 | 42 97206 78.00 


40 96160 72.00 | 40 96382 271.00 | 41 96624 162.00 | 41 96966 142.00 | 42 97208 88.00 
40 96162 82.00 | 40 96404 69.00 | 41 96626 176.00 | 41 96968 162.00 | 42 97210 98.00 
40 96164 94.00 | 40 96406 90.00 | 41 96628 186.00 | 41 96970 172.00 | 42 97212 130.00 
40 96166 104.00 | 40 96408 100.00 | 41 96630 196.00 | 41 96972 182.00 | 42 97214 140.00 
40 96168 114.00 | 40 96410 110.00 | 41 96632 206.00 | 41 96974 192.00 | 42 97216 156.00 
40 96170 124.00 | 40 96412 141.00 | 41 96654 52.00 | 41 96976 202.00 | 42 97218 166.00 
40 96172 134.00 | 40 96414 151.00 | 41 96656 62.00 | 41 96978 212.00 | 42 97220 176.00 
40 96174 144.00 | 40 96416 171.00 | 41 96658 72.00 | 41 96980 222.00 | 42 97222 184.00 
40 96176 160.00 | 40 96418 181.00 | 41 96660 82.00 | 41 96982 232.00 | 42 97224 194.00 
40 96178 170.00 | 40 96420 191.00 | 41 96662 92.00 | 42 97004 44.00 | 42 97226 208.00 


40 96180 184.00 | 40 96422 201.00 | 41 96664 112.00 |} 42 97006 52,00 | 42 97228 218.00 
40 96182 200.00 | 40 96424 211.00 | 41 96666 122.00 | 42 97008 62-008 e427 97230 228.00 
40 96204 58.00 | 40 96426 227.00 | 41 96668 132.00 | 42 97010 72.00 | 42 97232) 238.00 
40 96206 70.00 | 40 96428 241.00 | 41 96670 142.00 | 42 97012 82.00 | 42 97254 65.00 
40 96208 80.00 | 40 96430 257.00 | 41 96672 152.00 | 42 97014 94.00 | 42 97256 78.00 
40 96210 90.00 | 40 96432 271.00 | 41 96674 162.00 | 42 97016 104.00 | 42 97258 82.00 
40 96212 110.00 |} 40 96454 69.00 | 41 96676 176.00 | 42 97018 114.00 | 42 97260 98.00 
40 96214 120.00 | 40 96456 90.00 |} 41 96678 186.00 | 42 97020 124.00 | 42 97262 + 1:30.00 
40 96216 130.00 | 40 96458 100.00 | 41 96680 196.00 | 42 97022 134.00 | 42 97264 140.00 
40 96218 140.00 | 40 96460 110.00 | 41 96682 206.00 {| 42 97024 144.00 | 42 97266 156.00 


40 96220 150.00 | 40 96462 141.00 | 41 96804 66.00 | 42 97026 154.00 | 42 97268 166.00 
40 96222 170.00 | 40 96464 151.00 | 41 96806 77.00 | 42 97028 164.00 | 42 97270 #8 176.00 
40 96224 180.00 | 40 96466 171.00 | 41 96808 87.00 | 42 97030 184.00 | 42 97272 184.00 
40 96226 190.00 | 40 96468 181.00 | 41 96810 97.00 | 42 97032 200.00 | 42 97274 194.00 
40 96228 200.00 | 40 96470 191.00 | 41 96812 107.00 | 42 97054 44.00 | 42 97276 208.00 
40 96230 210.00 | 40 96472 201.00 | 41 96814 132.00 | 42 97056 52.00 | 42 97278 218.08 
40 96232 220.00 | 40 96474 211.00 | 41 96816 142.00 | 42 97058 62.00 | 42 97280 228.00 
40 96254 58.00 | 40 96476 227.00 | 41 96818 162.00 | 42 97060 72.00 | 42 97282 238.00 
40 96256 70.00 | 40 96478 241.00 | 41 96820 £172.00 | 42 97062 82.00 | 42 97304 65.00 
40 96258 80.00 | 40 96480 257.00 | 41 96822 182.00 | 42 97064 94.00 | 42 97306 78.00 


40 96260 90.00 | 40 96482 271.00 | 41 96824 192.00 | 42 97066 104.00 | 42 97308 88.00 
40 96262 110.00 | 41 96504 38.00 | 41 96826 202.00 | 42 97068 114.00 | 42 97310 98.00 
40 96264 120.00 | 41 96506 48.00 | 41 96828 212.00 | 42 97070 + 124.00 |} 42 97312 130.00 
40 96266 130.00 | 41 96508 58.00 | 41 96830 222.00 | 42 97072 134.00 | 42 97314 140.00 
40 96268 140.00 | 41 96510 68.00 | 41 96832 232.00 | 42 97074 144.00 | 42 97316 156.00 
40 96270 150.00 | 41 96512 78.00 | 41 96854 66.00 | 42 97076 154.00 | 42 97318 166.00 
40 96272 170.00 | 41 96514 90.00 | 41 96856 77.00 | 42 97078 164.00 | 42 97320 176.00 
40 96274 180.00 | 41 96516 100.00 | 41 96858 87.00 | 42 97080 184.00 } 42 97322 184.00 
40 96276 190.00 | 41 96518 110.00 | 41 96860 97.00 | 42 97082 200.00 | 42 97324 194.00 
40 96278 200.00 | 41 96520 124.00 | 41 96862 107.00 | 42 97104 58.00 | 42 97326 208.00 


40 96280 210.00 | 41 96522 134.00 | 41 96864 132.00 | 42 97106 70.00 | 42 97328 218.00 
40 96282 220.00 | 41 96524 144.00 | 41 96866 142.00 | 42 97108 80.00 | 42 97330 228.00 
40 96304 69.00 | 41 96526 154.00 | 41 96868 162.00 | 42 97110 90.00 | 42 97332 238.00 
40 96306 90.00 | 41 96528 164.00 | 41 96870 172.00 | 42 Salli CaO; OOM a) 97354 65.00 
40 96308 100.00 | 41 96530 174.00 | 41 96872 182.00 | 42 97114 120.00 | 42 97356 78.00 
40 96310 110.00 | 41 96532 190.00 | 41 96874 192.00 |} 42 97116 130.00 | 42 97358 88.00 
40 96312 141.00 | 41 96554 38.00 | 41 96876 202.00 | 42 97118 140.00 | 42 97360 98.00 
40 96314 151.00 | 41 96556 48.00 | 41 96878 212.00 | 42 97/20 meee 100-00 ma, 97362 130.00 
40 96316 171.00 | 41 96558 58.00 | 41 96880 222.00 |} 42 97122 170.00 } 42 97364 140.00 
40 96318 181.00 | 41 96560 68.00 | 41 96882 232.00 | 42 97124 180.00 | 42 97366 156.00 


40 96320 191.00 | 41 96562 78.00 | 41 96904 66.00 | 42 97126 190.00 } 42 97368 166.00 
40 96322 201.00 | 41 96564 90.00 | 41 96906 77.00 | 42 97128 200.00 | 42 97370 176.00 
40 96324 211.00 | 41 96566 100.00 | 41 96908 87.00 | 42 97130 210.00 } 42 97372 184.00 
40 96326 227.00 | 41 96568 110.00 | 41 96910 97.00 | 42 97132 220.00 | 42 97374 194.00 
40 96328 241.00 | 41 96570 124.00 | 41 96912 107.00 |} 42 97154 58.00 | 42 97376 208.00 
40 96330 257.06 | 41 96572 134.00 | 41 96914 132.00 } 42 97156 70.00 | 42 97378 218.00 
40 96332 271.00 | 41 96574 144.00 | 41 96916 142.00 | 42 97158 80.00 | 42 97380 228.00 
40 96354 69.00 | 41 96576 154.00 | 41 96918 162.00 | 42 97160 90.00 | 42 97382 238.00 
40 96356 90.00 | 41 96578 164.00 | 41 96920 172.00 j 42 97162 110.00 3 97404 42.00 
40 96358 100.00 | 41 96580 174.00 | 41 96922 182.00 | 42 97164 120.00 | 43 97406 48.00 
40 96360 110.00 | 41 96582 190.00 | 41 96924 192.00 | 42 97166 130.00 3 97408 58.00 


79 


me ee oe He He aa Soom aes he 


ew vo WwW CO 


Catalog 
No. 
97410 
97412 
97414 
97416 
97418 
97420 
97422 
97424 
97426 
97428 


97430 
97432 
97454 
97456 
97458 
97460 
97462 
97464 
97466 
97468 


97470 
97472 
97474 
97476 
97478 
97480 
97482 
97504 
97506 
97508 


97510 
STAB) 7% 
97514 
97516 
97518 
97520 
97522 
97524 
97526 
97528 


97530 
97532 
97554 
97556 
97558 
97560 
97562 
97564 
97566 
97568 


97570 
Aa (2 
97574 
97576 
97578 
97580 
97582 
97604 
97606 
97608 


97610 
97612 
97614 
97616 
97618 
97620 
97622 
97624 
97626 
97628 
97630 


List 
Price 


$68.00 

78.00 

90.00 
100.00 
110.00 
124.00 
134.00 
144.00 
154.00 
164.09 


174.00 
190.00 
42.00 
48.00 
58.00 
68.00 
78.00 
90.00 
100.00 
110.00 


124.00 
134.00 
144.00 
154.00 
164.00 
174.00 
190.00 

52.00 

62.00 

72.00 


82.00 

92.00 
112.00 
122.00 
132.00 
142.00 
152.00 
162.00 
176.00 
186.00 


196.00 
206.00 
52.00 
62.00 
72.00 
82.00 
92.00 
112.00 
122.00 
132.00 


142.00 
152.00 
162.00 
176.00 
186.00 
196.00 
206.00 

62.00 

72.06 

80.00 


90.00 
100.00 
120.00 
130.00 
148.00 
158.00 
166.00 
176.00 
184.00 
200.00 
210.00 


Catalog 
No. 
97632 
97654 
97656 
97658 
97660 
97662 
97664 
97666 
97668 
97670 


97672 
97674 
97676 
97678 
97680 
97682 
97704 
97706 
97708 
97710 


97712 
97714 
97716 
97718 
97720 
Si22. 
97724 
97726 
97728 
97730 


97732 
97754 
97756 
97758 
97760 
97762 
97764 
97766 
97768 
97770 


STEZ 
97774 
97776 
97778 
97780 
97782 
97804 
97806 
97808 
97810 


97812 
97814 
97816 
97818 
97820 
97822 
97824 
97826 
97828 
97830 


97832 
97854 
97856 
97858 
97860 
97862 
97864 
972366 
97868 
97870 
97872 


JAMIN STARRETT =. 
Numerical Index 
List Catalog List Catalog List Page No. Price 
Price Page No. Price Page No. Price Catalog List 


$220.00 | 44 97874 $144.00 | 44 98116 $156.00 | 45 98358 $72.00 


62.00 | 44 97876 154.00 |} 44 98118 166.00 | 45 98360 82.00 
72.00 | 44 97878 164.00 | 44 98120 176.00 | 45 98362 92.00 
80.00 | 44 97880 184.00 | 44 98122 184.00 | 45 98364 112.00 
90.00 | 44 97882 200.00 |} 44 98124 194.00 | 45 98366 122.00 
100.00 | 44 97904 58.00 | 44 98126 208.00 | 45 98368 132.00 
120.00 | 44 97906 70.00 | 44 98128 218.00 | 45 98370 142.00 
130.00 | 44 97908 80.00 | 44 98130 228.00 | 45 98372 152.00 
148.00 | 44 97910 90.00 | 44 98132 238.00 | 45 98374 162.00 
158.00 | 44 97912 110.00 | 44 98154 65.00 | 45 98376 176.00 


166.00 | 44 97914 120.00 | 44 98156 78.00 | 45 98378 186.00 
176.00 | 44 97916 130.00 | 44 98158 88.00 | 45 98380 196.00 
184.00 | 44 97918 140.00 | 44 98160 98.00 | 45 98382 206.00 
200.00 | 44 97920 150.00 | 44 98162 130.00 | 45 98404 62.00 
210.00 | 44 97922 170.00 | 44 98164 140.00 | 45 98406 72.00 
220.00 | 44 97924 180.00 | 44 98166 156.00 | 45 98408 80.00 
62.00 | 44 97926 190.00 | 44 98168 166.00 | 45 98410 90.00 
72.00 | 44 97928 200.00 | 44 98170 176.00 | 45 98412 100.00 
80.00 | 44 97930 210.00 | 44 98172 184.00 | 45 98414 120.00 
90.00 | 44 97932 220.00 | 44 98174 194.00 | 45 98416 130.00 


100.00 | 44 97954 58.00 | 44 98176 208.00 | 42 98418 148.00 
120.00 | 44 97956 70.00 | 44 98178 218.00 | 42 98420 158.00 
130.00 | 44 97958 80.00 | 44 98180 228.00 | 42 98422 166.00 
148.00 | 44 97960 90.00 | 44 98182 238.00 | 49 98424 176.00 
158.00 | 44 97962 110.00 | 45 98204 42.00 | 42 98426 184.00 
166.00 | 44 97964 120.00 | 45 98206 48.00 | 42 98428 200.00 
176.00 | 44. 97966 130.00 | 45 98208 58.00 in: Bones 210.00 
184.00 | 44 97968 140.00 | 45 98210 68.00 | 4» gang 220.00 
200.00 | 44 97970 150.00 | 45 98212 78.00 | jr oa, 62.00 
210.00 | 44 97972 170.00 | 45 98214 90.00 5672.00 


45 98458 : 
220.00 | 44 97974 180.00 | 45 98216 100.00 | 45 99460 ocge 


62.00 44 97976 190.00 45 98218 110.00 

72.00 | 44 97978 200.00 | 45 98220 124.00 a eee Tooted 

80.00 | 44 97980 210.00 | 45 98222 134.00 | 45 98466 130.00 

90.00 44 97982 220.00 45 98224 144.00 } 45 98468 148.00 
100.00 44 98004 65.00 45 98226 154.00 45 98470 158.00 
120.00 44 98006 78.00 45 98228 164.00 | 45 98472 166.00 
130.00 44 98008 88.00 45 98230 174.00 45 98474. 176.00 
148.00 44 98010 98.00 45 98232 190.00 45 98476 184.00 
158.00 | 44 98012 130.00 | 45 98254 42.00 | y= 98478 agg 09 


166.00 | 44 98014 140.00 | 45 98256 48.00 | 45 98480 210.00 
176.00 | 44. 98016 156.00 | 45 98258 58.00 a pees 220.00 
184.00 | 44 98018 166.00 | 45 98260 68.00 | {° Secon 62.00 
200.00 | 44 98020 176.00 | 45 98262 78.00 | 4? garne 72.00 
210.00 | 44 98022 184.00 | 45 98264 90.00 | i> Ganve 80.00 
220.00 | 44 98024 194.00 | 45 98266 100.00 | {> gae,9 400.00 
44.00 | 44 98026 208.00 | 45 98268 110.00 | {> 2aeys 100.00 
52.00 | 44 98028 218.00 | 45 98270 124.00 | 1? Gan 120.00 
62.00 | 44 98030 228.00 | 45 98272 134.00 130.00 
72.00 | 44 98032 238.00 | 45 98274 144.00 | 45 98518 148.00 
45 98520 158.00 
82.00 | 44 98054 65.00 | 45 98276 154.00 145 98522 166.00 
94.00 | 44 98056 78.00 | 45 98278 164.00 | 45 98524 17600 
104.00 | 44 98058 88.00 | 45 98280 174.00 | 45 98526 184.00 
114.00 | 44 98060 98.00 | 45 98282 190.00 | 45 98528 200.00 
124.00 | 44 98062 130.00 | 45 98304 52.00 | 45 98530 210.00 
134.00 | 44 98064 140.00 | 45 98306 62.00 | 45 98532 220.00 
144.00 | 44 98066 156.00 | 45 98308 72.00] 45 98554 62.00 
154.00 4 98068 166.00 45 98310 82.00 | 45 98556 72.00 
164.00 00 145 98312 92.00 
184.00 | 44 98072 184.00 | 45 98314 112.00 a ae a eea 


200.00 | 44 98074 194.00 | 45 98316 122.00 | 42 98562 100.00 
44.00 | 44 98076 208.00 | 45 98318 132.00 | 45 98564 120.00 
52.00 | 44 98078 218.00 | 45 98320 142.00 | 45 98566 130.00 
62.00 | 44 98080 228.00 | 45 98322 152.00 | 45 98568 148.00 
72.00 | 44 98082 238.00 | 45 98324 162.00 | 45 98570 158.00 
82.00 | 44 98104 65.00 | 45 98326 176.00 | 45 98572 166.00 
94.00 | 44 98106 78.00 145 98328 186.00 | 45 98574 176.00 

104.00 | 44 98108 88.00 | 45 98330 196.00 | 45 98576 184.00 

114.00 | 44 98110 98.00 | 45 98332 206.00 | 45 98578 200.00 

124.00 | 44 98112 130.00 | 45 98354 52.00 | 45 98580 210.00 

134.00 | 44 98114 140.00 | 45 98356 62.00 | 45 98582 220.00 


80 


